Heads up: There are no amended sections in this chapter.
The provisions of this appendix shall regulate the division of the city of New York into geographical territories known as fire districts and control the occupancy groups and construction classes permitted in the fire districts. Wherever reference is made to the Fire District, it shall be construed to mean the fire districts designated and referred to in this appendix.
Group H-1 occupancies shall be prohibited from location within the fire district.
The fire-resistance rating of bearing walls, floors, roofs and their supporting structural members shall comply with Table 601 of Chapter 6, but in no event shall such rating be less than 1-hour.
Exceptions: The following buildings or building elements may be constructed with fire-resistance rating in accordance with Table 601:
- Buildings of Type IV construction.
- Buildings equipped throughout with an automatic sprinkler system in accordance with Section 903.3.1.1.
- Automobile parking structures.
- Buildings surrounded on all sides by a permanently open space of not less than 30 feet (9144 mm).
- Partitions complying with Section 603.1 (8).
An existing building shall not hereafter be increased in height or area unless it is of a type of construction permitted for new buildings within the fire district or is altered to comply with the requirements for such type of construction. Nor shall any existing building be hereafter extended on any side, nor square footage or floors added within the existing building unless such modifications are of a type of construction permitted for new buildings within the fire district.
Any building located partially in the fire district, so that it is both inside and outside the district, shall be of a type of construction required for the fire district if more than 25 percent of the total floor area of the building is located inside the fire district.
The preceding provisions of this appendix shall not apply in the following instances:
- Temporary platforms, reviewing stands, and similar miscellaneous structures used for a limited period of time, subject to the approval of the com- missioner.
- Fences not over 6 feet (1829 mm) high.
- Water towers, tank structures, and trestles may be constructed of wood planking and timbers of dimensions not less than as required for Type IV construction when not over 35 feet (10 668 mm) high and having an exterior separation of at least 30 feet (9144 mm).
- Detached greenhouses accessory to a one- or two-family dwelling located on the same lot at least 6 feet (1829 mm) from any lot line or building walls and not exceeding 14 feet (4267 mm) in height.
- Porches on dwellings not over one story in height, and not over 10 feet (3048 mm) wide from the face of the building, provided such porch does not come within 5 feet (1524 mm) of any property line.
- Sheds open on a long side not over 15 feet (4572 mm) high and 500 square feet (46 m2) in area.
- Existing one- and two-family dwellings of a type of construction not permitted in the fire district can be extended 25 percent of the floor area existing at the time of inclusion in the fire district by any type of construction permitted by this code.
- Wood decks less than 600 square feet (56 m2) where constructed of 2-inch (51 mm) nominal wood, pressure treated for exterior use.
- One- or two-family detached or semi-detached dwellings of two stories or less in height and 2,500 square feet (232 m2) or less in area located within zoning Districts R-2 through R-5 may be constructed or reconstructed of construction Type VA, or if damaged for any cause only the damaged portions shall be required to be reconstructed to conform to Type VA construction. In addition, one-family dwellings located within zoning District R-1 anywhere in the city, may be constructed of Type VB construction in conformance with the area and height limits established by Table 503 of Chapter 5.
- An accessory building or structure used as an office or similar use for an open parking lot located on the same lot, may be constructed of Type VA or VB construction provided its area shall be limited to 150 square feet (14 m2) and height of 10 feet (3048 mm) maximum. Such structure shall be located not less than 6 feet (1829 mm) from any lot line or buildings on the same lot.
Within the boroughs of Richmond and Queens, the fire districts shall comprise such areas indicated on the "fire district maps" as per Figures D106.1(1) and D106.1(2).