Heads up: There are no suggested sections in this chapter.
Heads up: There are no amended sections in this chapter.
This code shall be known and may be cited as the "New York City Fuel Gas Code," "NYCFGC" or "FGC". All section numbers in this code shall be deemed to be preceded by the designation "FGC".
These regulations cover piping systems for natural gas with an operating pressure of 125 pounds per square inch gauge (psig) (862 kPa gauge) or less. Coverage shall extend to the outlet of the equipment shutoff valves. Piping systems requirements shall include design, materials, components, fabrication, assembly, installation, testing, inspection, operation and main- tenance.
This code shall not apply to the following:
1. Portable LP-gas equipment of all types that is not connected to a fixed fuel piping system.
2. Oxygen-fuel gas cutting and welding systems.
3. Industrial gas applications using gases such as acetylene and acetylenic compounds, hydrogen, ammonia, carbon monoxide, oxygen and nitrogen.
4. Petroleum refineries, pipeline compressor or pumping stations, loading terminals, compounding plants, refinery tank farms and natural gas processing plants.
5. Integrated chemical plants or portions of such plants where flammable or combustible liquids or gases are produced by, or used in, chemical reactions.
6. LP-gas installations at utility gas plants.
7. Liquefied natural gas (LNG) installations.
9. Components within proprietary items of equipment, apparatus or instruments such as gas-generating sets, compressors and calorimeters.
10. LP-gas equipment for vaporization, gas mixing and gas manufacturing.
11. Temporary LP-gas piping for buildings under construction or renovation that is not to become part of the permanent piping system.
12. Installation of LP-gas systems for railroad switch heating.
13. Installation of hydrogen gas, LP-gas and compressed natural gas (CNG) systems on vehicles.
14. Except as provided in Section 401.1.1 and Appendices E and F, gas piping, meters, gas pressure regulators and other appurtenances used by the serving gas supplier in the distribution of gas, other than undiluted LP-gas.
15. Building design and construction, except as specified herein.
16. Piping systems for mixtures of gas and air within the flammable range with an operating pressure greater than 10 psig (69 kPa gauge).
The purpose of this code is to provide minimum standards to safeguard life or limb, health, property, public welfare and the environment by regulating and controlling the design, construction, installation, quality of materials, location, operation and maintenance or use of fuel gas systems.
If a section, subsection, sentence, clause or phrase of this code is, for any reason, held to be unconstitutional, such decision shall not affect the validity of the remaining portions of this code.
The provisions of this code shall apply to all matters affecting or relating to structures and premises, as set forth in Section 101. Where, in a specific case, different sections of this code specify different materials, methods of construction or other requirements, the most restrictive shall govern.
Except as otherwise provided for in this chapter or elsewhere in this code, a provision in this code shall not require the removal, alteration or abandonment of, nor prevent the continued utilization and maintenance of, existing installations lawfully in existence on the effective date of this code.
Installations, both existing and new, and parts thereof shall be maintained in proper operating condition in accordance with the original design and in a safe condition. Devices or safeguards that are required by this code shall be maintained in compliance with the applicable provisions under which they were installed. The owner or the owner's designated agent shall be responsible for maintenance of installations. To determine compliance with this provision, the commissioner shall have the authority to require an existing installation to be inspected.
Additions, alterations, renovations or repairs to installations shall conform to that required for new installations without requiring the existing installation to comply with all of the requirements of this code. Additions, alterations or repairs shall not cause an existing installation to become unsafe, hazardous or overloaded. Minor additions, alterations, renovations and repairs to existing installations shall meet the provisions for new construction, unless such work is done in the same manner and arrangement as was in the existing system, is not hazardous and is approved.
The standards referenced in this code shall be those that are listed in Chapter 8 and in the rules of the department and such standards shall be considered part of the requirements of this code to the prescribed extent of each such reference. Where differences occur between provisions of this code and the referenced standards, the provisions of this code shall apply. Refer to Article 103 of chapter 1 of Title 28 of the Administrative Code for additional provisions relating to referenced standards.
Requirements necessary for the strength, stability or proper operation of an existing or proposed installation, or for the public safety, health and general welfare, not specifically covered by this code, shall be determined by the commissioner.
The commissioner shall have the authority to render interpretations and to adopt rules establishing policies, and procedures to clarify and implement the provisions of this code. Such interpretations and rules shall be in compliance with the intent and purpose of this code. See the New York City Charter and Chapter 1 of Title 28 of the Administrative Code for additional provisions relating to the authority of the Commissioner of Buildings.
Any owner or authorized agent who intends to construct, add to, alter, repair, move, demolish, or change the occupancy of a building or structure, or to erect, install, add to, alter, repair, remove, convert or replace any gas, mechanical or plumbing system, the installation of which is regulated by this code, or to cause any such work to be done, shall first make application for construction document approval in accordance with Chapter 1 of Title 28 of the Administrative Code and this chapter and obtain the required permit.
The issuance or granting of a permit shall not be construed to be a permit for, or an approval of, any violation of any of the provisions of this code or of any other law. Permits presuming to give authority to violate or cancel the provisions of this code or other law shall not be valid. The issuance of a permit based on construction documents and other data shall not prevent the commissioner from requiring the correction of errors in the construction documents and other data. The commissioner is also authorized to prevent occupancy or use of a structure where in violation of this code or of any other law.
In addition to any permits required by the provisions of this code, permits for sidewalk and street openings shall be obtained from the Department of Transportation.
The applicant shall submit all of the documents specified in Sections 106.3 through 106.8 as appropriate to the nature and extent of the work proposed. Construction documents shall indicate the heating, ventilating, refrigeration, and other mechanical work to be performed, so drawn as to conform to the architectural and structural aspects of the building and to show in detail compliance with this code.
Composite plans showing compliance of architectural, structural, and mechanical parts of a building may be submitted provided that a clear understanding of each part is not impaired.
The lot diagram shall be provided where applicable to the work proposed, including but not limited to the installation of exterior or rooftop equipment.
Where applicable to the proposed work, the statement shall identify:
1. The occupancy group or groups that apply to parts of the building in accordance with Section 302 of the New York City Building Code;
3. The construction class of the building in accordance with Section 602 of the New York City Building Code;
4. The structural occupancy category in accordance with Table 1604.5 of the New York City Building Code;
6. The applicable measurements to the highest and lowest level of fire department access; and
7. Whether the building is inside or outside of the fire districts.
Construction documents for fuel-gas-burning equipment and fuel-gas piping shall contain plans that include the following data and information.
1. Riser diagrams showing the story heights, the gas risers, and related equipment.
2. Diagrammatic floor plans showing the size, location, material for all gas distribution piping and related equipment.
3. Floor plans or partial floor plans showing the location, layout, size, and listing information for all fuel-gas burning equipment, gas vents, and chimneys, with the riser numbers coordinated with other plans and diagrams. The floor plans shall indicate locations of meters, shut-off valves, including the outside gas cut-off required by Appendix E, Section E6. The plans shall also indicate the method or means of providing air to the equipment space, including duct and opening sizes.
4. Plans indicating the location and type of any relevant smoke and heat detectors, alarm, and fire extinguishing systems.
5. Seismic protection and restraint details for piping and equipment as required by Chapter 16 of the New York City Building Code.
6. Details indicting the location, size and materials for all breechings; the thickness and type of insulation materials; and the clearances from combustible walls, partitions, and ceiling; and the fire-resistive ratings of rooms and spaces containing the equipment.
7. Details describing the type, material, listing information, height, and termination distances to adjacent properties and structures for chimneys and gas vents.
8. Details showing structural supports for fuel-gas-burning equipment where required.
Construction documents for heating systems shall include the temperature to be maintained in every room and the output capacity in BTU per hour (W) of the central heating source.
Except as otherwise specifically provided, inspections required by this code or by the department during the progress of work may be performed on behalf of the owner by approved agencies or, if applicable, by special inspectors. However, in the interest of public safety, the commissioner may direct that any of such inspections be performed by the department. All inspections shall be performed at the sole cost and expense of the owner. Refer to Article 116 of Chapter 1 of Title 28 of the Administrative Code for additional provisions relating to inspections. In addition to any inspections otherwise required by this code or applicable rules, the following inspections shall be required:
1. Progress inspections:
1.1. Underground inspection shall be made after trenches or ditches are excavated and bedded, piping is installed and before backfill is put in place. When excavated soil contains rocks, broken concrete, frozen chunks and other rubble that would damage or break the piping or cause corrosive action, clean backfill shall be on the job site.
1.2. Rough-in inspection shall be made after the roof, framing, fireblocking and bracing are in place and components to be concealed are complete, and prior to the installation of wall or ceiling membranes.
2. Special inspections. Special inspections shall be performed in accordance with this code and Chapter 17 of the New York City Building Code.
4. Issuance of Certificate of Compliance. Upon satisfactory inspection of service equipment and the project satisfied all the requirements for sign-off, the department shall issue certificate of compliance as applicable for the following service equipment:
4.1. Fuel-gas-burning equipment,
4.2. Heating systems, and
Prior to the approval of a prefabricated construction assembly having concealed work and the issuance of a permit, the department shall require the submittal of an evaluation report by an approved agency on each prefabricated construction assembly, indicating the complete details of the installation, including a description of the system and its components, the basis upon which the system is being evaluated, test results and similar information and other data as necessary for the commissioner to determine conformance to this code.
It shall be the duty of the permit holder to cause the work to remain accessible and exposed for inspection purposes. Neither the commissioner nor the city shall be liable for expense entailed in the removal or replacement of any material required to allow inspection.
New installations and parts of existing installations that have been altered, extended, renovated or repaired, shall be tested as prescribed herein to disclose leaks and defects.
Apparatus, instruments, material and labor required for testing an installation or part thereof shall be furnished by the permit holder.
Where any work or installation does not pass an initial test or inspection, the necessary corrections shall be made so as to achieve compliance with this code. The work or installation shall then be resubmitted to the department for inspection and testing.
The commissioner shall have the authority to require disconnection of utility service to the building, structure or system regulated by the technical codes in case of emergency where necessary to eliminate an immediate hazard to life or property. The commissioner shall notify the serving utility, and wherever possible, the owner and occupant of the building, structure or service system of the decision to disconnect prior to taking such action. If not notified prior to disconnection, the owner or occupant of the building, structure or service system shall be notified in writing, as soon as practicable thereafter.
A person shall not make energy source connections to installations regulated by this code that have been disconnected or ordered to be disconnected by the commissioner, or the use of which has been ordered to be discontinued by the commissioner until the commissioner authorizes the reconnection and use of such installations. When an installation is maintained in violation of this code, and in violation of a notice issued pursuant to the provisions of this section, the commissioner shall institute appropriate action to prevent, restrain, correct or abate the violation.