In addition to the provisions of this chapter, work shall comply with all of the requirements of Chapters 7 and 8. The requirements of Sections 803, 804 and 805 shall apply within all work areas whether or not they include exits and corridors shared by more than one tenant and regardless of the occupant load.
Exception: Buildings in which the reconfiguration of space affecting exits or shared egress access is exclusively the result of compliance with the accessibility requirements of Section 705.2 shall not be required to comply with this chapter.
Boiler and furnace equipment rooms adjacent to or within the following facilities shall be enclosed by 1-hour fire-resistance-rated construction: day nurseries, children’s shelter facilities, residential childcare facilities, and similar facilities with children below the age of 21/2 years or that are classified as Group I-2 occupancies, shelter facilities, residences for the developmentally disabled, group homes, teaching family homes, transitional living homes, rooming and boarding houses, hotels, and multiple dwellings.
- Furnace and boiler equipment of low-pressure type, operating at pressures of 15 pounds per square inch gauge (psig) (103.4 KPa) or less for steam equipment or 170 psig (1171 KPa) or less for hot water equipment, when installed in accordance with manufacturer recommendations.
- Furnace and boiler equipment of residential R-3 type with 200,000 British thermal units (Btu) (2.11 × 108 J) per hour input rating or less is not required to be enclosed.
- Furnace rooms protected with automatic sprinkler protection.
Emergency controls for boilers and furnace equipment shall be provided in accordance with the International Mechanical Code in all buildings classified as day nurseries, children’s shelter facilities, residential childcare facilities, and similar facilities with children below the age of 21/2 years or that are classified as Group I-2 occupancies, and in group homes, teaching family homes, and supervised transitional living homes in accordance with the following:
- Emergency shutoff switches for furnaces and boilers in basements shall be located at the top of the stairs leading to the basement; and
- Emergency shutoff switches for furnaces and boilers in other enclosed rooms shall be located outside of such room.
Where the work area is in any attached dwelling unit in Group R-3 or any multiple single-family dwelling (townhouse), walls separating the dwelling units that are not continuous from the foundation to the underside of the roof sheathing shall be constructed to provide a continuous fire separation using construction materials consistent with the existing wall or complying with the requirements for new structures. All work shall be performed on the side of the dwelling unit wall that is part of the work area.
Where required by the International Building Code, a manual fire alarm system shall be provided throughout the work area. Alarm notification appliances shall be provided on such floors and shall be automatically activated as required by the International Building Code.
- Alarm-initiating and notification appliances shall not be required to be installed in tenant spaces outside of the work area.
- Visual alarm notification appliances are not required, except where an existing alarm system is upgraded or replaced or where a new fire alarm system is installed.
All existing elements of the lateral force-resisting system shall comply with this section.
- Buildings of Group R occupancy with no more than five dwelling or sleeping units used solely for residential purposes that are altered based on the conventional light-frame construction methods of the International Building Code or in compliance with the provisions of the International Residential Code.
- Where such alterations involve only the lowest story of a building and the change of occupancy provisions of Chapter 10 do not apply, only the lateral force-resisting components in and below that story need comply with this section.