Heads up: There are no amended sections in this chapter.
Words and terms used in this chapter and defined in Chapter 2 shall have the meanings ascribed to them as defined therein.
Tire rebuilding plants shall maintain the requirements of the applicable building code, as to construction, separation from other buildings or other portions of the same building, and protection.
The buffing area shall be cleaned at frequent intervals to prevent the accumulation of rubber particles.
Cutting, welding or heating devices shall not be operated in tire storage yards.
Tire storage piles shall not be located beneath electrical power lines having a voltage in excess of 750 volts or that supply power to fire emergency systems.
The owner or individual in charge of the tire storage yard shall be required to prepare and submit to the fire code official a fire safety plan for review and approval. The fire safety plan shall include provisions for fire department vehicle access. Not less than one copy of the fire safety plan shall be prominently posted and maintained at the storage yard.
The telephone number of the fire department and location of the nearest telephone shall be posted conspicuously in attended locations.
Tire storage shall be restricted to individual piles not exceeding 5,000 square feet (464.5 m2) of continuous area. Piles shall not exceed 50,000 cubic feet (1416 m3) in volume or 10 feet (3048 mm) in height.
Individual tire storage piles shall be separated from other piles by a clear space of not less than 40 feet (12 192 mm).
Tire storage piles shall be separated by a clear space of not less than 40 feet (12 192 mm) from piles of other stored product.
Tire storage piles shall be located not less than 50 feet (15 240 mm) from lot lines and buildings.
Where the bulk volume of stored product is more than 150,000 cubic feet (4248 m3), storage arrangement shall be in accordance with the following:
Separation between groups shall be not less than 75 feet (22 860 mm) wide.
Outdoor waste tire storage shall not be located under bridges, elevated trestles, elevated roadways or elevated railroads.
Fire apparatus access roads shall be located within all pile clearances identified in Section 3405.4 and within all fire breaks required in Section 3405.5. Access roadways shall be within 150 feet (45 720 mm) of any point in the storage yard where storage piles are located, not less than 20 feet (6096 mm) from any storage pile.
The fence shall be constructed of approved materials and shall be not less than 6 feet (1829 mm) high and provided with gates not less than 20 feet (6096 mm) wide.
Gateways shall be kept clear of obstructions and be fully openable at all times.
Where tires are stored on-tread, the dimension of the pile in the direction of the wheel hole shall be not more than 50 feet (15 240 mm). Tires stored adjacent to or along one wall shall not extend more than 25 feet (7620 mm) from that wall. Other piles shall be not more than 50 feet (15 240 mm) in width.