The requirements of NFPA 652 apply to all new and existing facilities and operations with combustible dust hazard. Existing facilities shall have a dust hazard analysis (DHA) completed in accordance with Section 7.1.2 of NFPA 652.
The fire code official shall be authorized to order a dust hazard analysis to occur sooner if a combustible dust hazard has been identified in a facility that has not previously performed an analysis.
The industry- or commodity-specific codes and standards listed in Table 2204.1 shall be complied with based on the identification and evaluation of the specific fire and deflagration hazards that exist at a facility.
SPECIFIC HAZARDS STANDARDS
|NFPA 61||Standard for the Prevention of Fires and Dust Explosions in Agricultural and Food Processing Facilities|
|NFPA 69||Standard on Explosion Prevention Systems|
|NFPA 70||National Electrical Code|
|NFPA 85||Boiler and Combustion System Hazards Code|
|NFPA 120||Standard for Fire Prevention and Control in Coal Mines|
|NFPA 484||Standard for Combustible Metals|
|NFPA 654||Standard for Prevention of Fire and Dust Explosions from the Manufacturing, Processing and Handling of Combustible Particulate Solids|
|NFPA 655||Standard for the Prevention of Sulfur Fires and Explosions|
|NFPA 664||Standard for the Prevention of Fires and Explosions in Wood Processing and Woodworking Facilities|