- Resistive and inductive loads not exceeding the ampere rating of the switch at the voltage involved.
- Tungsten-filament lamp loads not exceeding the ampere rating of the switch at 120 volts.
- Motor loads not exceeding 80 percent of the ampere rating of the switch at its rated voltage.
Nonmetallic boxes for switches shall be installed with a wiring method that provides or includes an equipment grounding conductor.
3. Connection to an equipment grounding conductor shall not be required for snap switches that have an integral nonmetallic enclosure complying with Section E3905.13.
- The conductors enter the box through a raceway. The raceway shall have sufficient cross-sectional area to accommodate the extension of the grounded circuit conductor of the lighting circuit to the switch location whether or not the conductors in the raceway are required to be increased in size to comply with Section E3705.3.
- Cable assemblies enter the box through a framing cavity that is open at the top or bottom on the same floor level, or through a wall, floor, or ceiling that is unfinished on one side.
RECEPTACLE RATINGS FOR
VARIOUS SIZE MULTI-OUTLET CIRCUITS
|CIRCUIT RATING (amperes)||RECEPTACLE RATING (amperes)|
|20||15 or 20|
|40||40 or 50|
- Receptacles located more than 5.5 feet (1676 mm) above the floor.
- Receptacles that are part of a luminaire or appliance.
- A single receptacle for a single appliance or a duplex receptacle for two appliances where such receptacles are located in spaces dedicated for the appliances served and, under conditions of normal use, the appliances are not easily moved from one place to another. The appliances shall be cord-and-plug-connected to such receptacles in accordance with Section E3909.4.
- Thermal protection shall not be required in recessed luminaires listed for the purpose and installed in poured concrete.
- Thermal protection shall not be required in recessed luminaires having design, construction, and thermal performance characteristics equivalent to that of thermally protected luminaires, and such luminaires are identified as inherently protected.
The types of luminaires installed in clothes closets shall be limited to surface-mounted or recessed incandescent or LED luminaires with completely enclosed light sources, surface-mounted or recessed fluorescent luminaires, and surface-mounted fluorescent or LED luminaires identified as suitable for installation within the closet storage area. Incandescent luminaires with open or partially enclosed lamps and pendant luminaires or lamp-holders shall be prohibited. The minimum clearance between luminaires installed in clothes closets and the nearest point of a closet storage area shall be as follows:
- Surface-mounted incandescent or LED luminaires with a completely enclosed light source shall be installed on the wall above the door or on the ceiling, provided that there is a minimum clearance of 12 inches (305 mm) between the fixture and the nearest point of a storage space.
- Surface-mounted fluorescent luminaires shall be installed on the wall above the door or on the ceiling, provided that there is a minimum clearance of 6 inches (152 mm).
- Recessed incandescent luminaires or LED luminaires with a completely enclosed light source shall be installed in the wall or the ceiling provided that there is a minimum clearance of 6 inches (152 mm).
- Recessed fluorescent luminaires shall be installed in the wall or on the ceiling provided that there is a minimum clearance of 6 inches (152 mm) between the fixture and the nearest point of a storage space.
- Surface-mounted fluorescent or LED luminaires shall be permitted to be installed within the closet storage space where identified for this use.
Luminaires having exposed ballasts, transformers, LED drivers or power supplies shall be installed so that such ballasts, transformers, LED drivers or power supplies are not in contact with combustible material unless listed for such condition.
- Where likely to be subjected to physical damage.
- In wet or damp locations.
- Where subject to corrosive vapors.
- In storage battery rooms.
- In hazardous (classified) locations.
- Where concealed.
- Where extended through walls or partitions.
- Less than 5 feet (1524 mm) above the finished floor except where protected from physical damage or the track operates at less than 30 volts rms open-circuit voltage.
- Where prohibited by Section E4003.11.