In resin application areas, electrical wiring and equipment that is subject to deposits of combustible residues shall be listed for such exposure and shall be installed as required for hazardous (classified) locations. Electrical wiring and equipment not subject to deposits of combustible residues shall be installed as required for ordinary hazard locations.
Exception: Drying apparatus complying with Section 2404.6.1.2.
THE USE OF WELDING OR CUTTING
EQUIPMENT IN OR NEAR THIS AREA
IS DANGEROUS BECAUSE OF FIRE
AND EXPLOSION HAZARDS. WELDING
AND CUTTING SHALL BE DONE ONLY
UNDER THE SUPERVISION OF THE
PERSON IN CHARGE.
Exception: One individual booth not exceeding 500 square feet (46 m2).
a. An alarm shall sound; and
b. Spray operations shall automatically shut down.
Exception: Portable electrostatic paint-spraying apparatus listed for use in Class I, Division 1, locations.