The following words and terms shall, for the purposes of this chapter and as used elsewhere in this code, have the meanings shown herein.
COLD DECK. A pile of unfinished cut logs.
FINES. Small pieces or splinters of wood byproducts that will pass through a 0.25-inch (6.4 mm) screen.
HOGGED MATERIALS. Wood waste materials produced from the lumber production process.
PLYWOOD and VENEER MILLS. Facilities where raw wood products are processed into finished wood products, including waferboard, oriented strandboard, fiberboard, composite wood panels and plywood.
RAW PRODUCT. A mixture of natural materials such as tree, brush trimmings, or waste logs and stumps.
STATIC PILES. Piles in which processed wood product is mounded and is not being turned or moved.
Exception: Where dryers or other sources of ignition are protected by a supervised automatic sprinkler system complying with Section 903.
Cold decks shall not exceed 500 feet (152.4 m) in length, 300 feet (91 440 mm) in width and 20 feet (6096 mm) in height. Cold decks shall be separated from adjacent cold decks or other exposures by a minimum of 100 feet (30 480 mm).
Exception: The size of cold decks shall be determined by the fire code official where the decks are protected by special fire protection including, but not limited to, additional fire flow, portable turrets and deluge sets, and hydrant hose houses equipped with approved fire-fighting equipment capable of reaching the entire storage area in accordance with Chapter 9.
Piles shall not exceed 60 feet (18 288 mm) in height, 300 feet (91 440 mm) in width and 500 feet (152 m) in length. Piles shall be separated from adjacent piles or other exposures by approved fire apparatus access roads.
Exception: The fire code official is authorized to allow the pile size to be increased when additional fire protection is provided in accordance with Chapter 9. The increase shall be based on the capabilities of the system installed.
Piles shall not exceed 25 feet (7620 mm) in height, 150 feet (45 720 mm) in width and 250 feet (76 200 mm) in length.
Exception: The fire code official is authorized to allow the pile size to be increased when additional fire protection is provided in accordance with Chapter 9. The increase shall be based upon the capabilities of the system installed.
Permanent lumber storage areas shall be surrounded with an approved fence. Fences shall be a minimum of 6 feet (1829 mm) in height.
Exception: Lumber piles inside of buildings and production mills for lumber, plywood and veneer.