The provisions contained in this appendix are not mandatory unless specifically referenced in the adopting ordinance.The provisions contained in this appendix are adopted as part of this code.
Walls, floors, roofs and their supporting structural members shall be a minimum of 1-hour fire-resistance-rated construction.
1. Buildings of Type IV construction.
3. Automobile parking structures.
4. Buildings surrounded on all sides by a permanently open space of not less than 30 feet (9144 mm).
5. Partitions complying with Section 603.1, Item 10.
Exterior load-bearing walls of Type II buildings shall have a fire-resistance rating of 2 hours or more where such walls are located within 30 feet (9144 mm) of a common property line or an assumed property line. Exterior nonload-bearing walls of Type II buildings located within 30 feet (9144 mm) of a common property line or an assumed property line shall have fireresistance ratings as required by Table 601, but not less than 1 hour. Exterior walls located more than 30 feet (9144 mm) from a common property line or an assumed property line shall comply with Table 601.
Exception: In the case of one-story buildings that are 2,000 square feet (186 m2) or less in area, exterior walls located more than 15 feet (4572 mm) from a common property line or an assumed property line need only comply with Table 601.
Permanent canopies are permitted to extend over adjacent open spaces provided all of the following are met:
Exception: Any textile covering for the canopy shall be flame resistant as determined by tests conducted in accordance with NFPA 701 after both accelerated water leaching and accelerated weathering.
3. The canopy shall have at least one long side open.
4. The maximum horizontal width of the canopy shall not exceed 15 feet (4572 mm).
The preceding provisions of this appendix shall not apply in the following instances:
1. Temporary buildings used in connection with duly authorized construction.
3. Fences not over 8 feet (2438 mm) high.
4. Coal tipples, material bins and trestles of Type IV construction.
6. Greenhouses less than 15 feet (4572 mm) high.
7. Porches on dwellings not over one story in height, and not over 10 feet (3048 mm) wide from the face of the building, provided such porch does not come within 5 feet (1524 mm) of any property line.
8. Sheds open on a long side not over 15 feet (4572 mm) high and 500 square feet (46 m2) in area.
9. One- and two-family dwellings where of a type of construction not permitted in the fire district can be extended 25 percent of the floor area existing at the time of inclusion in the fire district by any type of construction permitted by this code.
10. Wood decks less than 600 square feet (56 m2) where constructed of 2-inch (51 mm) nominal wood, pressure treated for exterior use.
12. Exterior plastic veneer complying with Section 2605.2 where installed on exterior walls required to have a fire-resistance rating not less than 1 hour, provided the exterior plastic veneer does not exhibit sustained flaming as defined in NFPA 268.
|ASTM E 84-04||Test Method for Surface Burning Characteristics of Building Materials||D102.2.8|
|NFPA 268-01||Test Method for Determining Ignitability of Exterior Wall Assemblies Using a Radiant Heat Energy Source||D105.1|
|NFPA 701-99||Methods of Fire Tests for Flame-Propagation of Textiles and Films||D102.2.8|
|UL 723-03||Standard for Test for Surface Burning Characteristics of Building Materials, with Revisions through May 2005||D102.2.8|