Exception to 8.1.4
Compliance shall not be required for the relocation or reuse of existing equipment at the same site.
The following shall be automatically controlled:
This control shall function on
All controlled receptacles shall be permanently marked to visually differentiate them from uncontrolled receptacles and are to be uniformly distributed throughout the space. Plug-in devices shall not be used to comply with Section 8.4.2.
Exceptions to Section 8.4.2
Receptacles for the following shall not require an automatic control device:
Measurement devices shall be installed in new buildings to monitor the electrical energy use for each of the following separately:
Exception to 22.214.171.124
Up to 10% of the load for each of the categories (b) through (e) shall be allowed to be from other electrical loads.
The electrical energy use for all loads specified in Section 126.96.36.199 shall be recorded a minimum of every 15 minutes and reported at least hourly, daily, monthly, and annually. The data for each tenant space shall be made available to that tenant. In buildings with a digital control system installed to comply with Section 188.8.131.52, the energy use data shall be transmitted to the digital control system and graphically displayed. The system shall be capable of maintaining all data collected for a minimum of 36 months.
Exceptions to Sections 184.108.40.206 and 220.127.116.11
Low-voltage dry-type transformers shall comply with the provisions of the Energy Policy Act of 2005, where applicable, as shown in Table 8.4.4. Transformers that are not included in the scope of the Energy Policy Act of 2005 have no performance requirements in this section and are listed for ease of reference as exceptions.
Exception to 8.4.4
|Single-Phase Transformers||Three-Phase Transformers|
The terms meter, sub-meter, covered building, tenant space and covered tenant space shall have the same meanings as defined in Section 28-311.2 of the Administrative Code. Each covered tenant space in a new building shall be equipped with a separate meter or sub-meter to measure the electrical consumption of such space when let or sublet. Where the covered tenant space is a floor with multiple tenancies, each tenancy with an area less than that as defined in Section 28-311.2 of the Administrative Code of the city of New York shall (i) be equipped with a separate meter or sub-meter, (ii) share a meter or sub-meter with other tenant spaces on the floor, or (iii) share a meter or sub-meter covering the entire floor. As new covered tenant spaces are created, they shall be equipped with meters or sub-meters as provided in this section.
(Enforcement agencies should only check to ensure that the construction documents require this information to be transmitted to the owner and should not expect copies of any of the materials.)