Heads up: There are no amended sections in this chapter.
Welding, cutting, open torches and other hot work operations and equipment shall comply with this chapter.
Hot work shall only be conducted in areas designed or authorized for that purpose by the personnel responsible for a Hot Work Program. Hot work shall not be conducted in the following areas unless approval has been obtained from the fire code official:
- Areas where the sprinkler system is impaired.
- Areas where there exists the potential of an explosive atmosphere, such as locations where flammable gases, liquids or vapors are present.
- Areas with readily ignitable materials, such as storage of large quantities of bulk sulfur, baled paper, cotton, lint, dust or loose combustible materials.
- On board ships at dock or ships under construction or repair.
- At other locations as specified by the fire code official.
Temporary and fixed hot work areas shall comply with this section.
A permit for hot work operations shall not be issued unless the individuals in charge of performing such operations are capable of performing such operations safely. Demonstration of a working knowledge of the provisions of this chapter shall constitute acceptable evidence of compliance with this requirement.
Visible hazard identification signs shall be provided where required by Chapter 50. Where the hot work area is accessible to persons other than the operator of the hot work equipment, conspicuous signs shall be posted to warn others before they enter the hot work area. Such signs shall display the following warning:
HOT WORK IN PROGRESS
Hot work areas shall not contain combustibles or shall be provided with appropriate shielding to prevent sparks, slag or heat from igniting exposed combustibles.
Conveyor systems that are capable of carrying sparks to distant combustibles shall be shielded or shut down.
Partitions segregating hot work areas from other areas of the building shall be noncombustible. In fixed hot work areas, the partitions shall be securely connected to the floor such that no gap exists between the floor and the partition. Partitions shall prevent the passage of sparks, slag, and heat from the hot work area.
Hot work shall not be performed on containers or equipment that contains or has contained flammable liquids, gases or solids until the containers and equipment have been thoroughly cleaned, inerted or purged; except that "hot tapping" shall be allowed on tanks and pipe lines when such work is to be conducted by approved personnel.
Automatic sprinkler protection shall not be shut off while hot work is performed. Where hot work is performed close to automatic sprinklers, noncombustible barriers or damp cloth guards shall shield the individual sprinkler heads and shall be removed when the work is completed. If the work extends over several days, the shields shall be removed at the end of each workday. The fire code official shall approve hot work where sprinkler protection is impaired.
A fire watch shall be provided during hot work activities and shall continue for a minimum of 30 minutes after the conclusion of the work. The fire code official, or the responsible manager under a hot work program, is authorized to extend the fire watch based on the hazards or work being performed.
Exception: Where the hot work area has no fire hazards or combustible exposures.
Where hoselines are required, they shall be connected, charged and ready for operation.
Before hot work is permitted and at least once per day while the permit is in effect, the area shall be inspected by the individual responsible for authorizing hot work operations to ensure that it is a fire safe area. Information shown on the permit shall be verified prior to signing the permit in accordance with Section 105.6.
A pre-hot-work check shall be conducted prior to work to ensure that all equipment is safe and hazards are recognized and protected. A report of the check shall be kept at the work site during the work and available upon request. The pre-hot-work check shall determine all of the following:
- Hot work equipment to be used shall be in satisfactory operating condition and in good repair.
- Hot work site is clear of combustibles or combustibles are protected.
- Exposed construction is of noncombustible materials or, if combustible, then protected.
- Openings are protected.
- Floors are kept clean.
- No exposed combustibles are located on the opposite side of partitions, walls, ceilings or floors.
- Fire watches, where required, are assigned.
- Approved actions have been taken to prevent accidental activation of suppression and detection equipment in accordance with Sections 3504.1.8 and 3504.1.9.
- Fire extinguishers and fire hoses (where provided) are operable and available.
Devices or attachments mixing air or oxygen with combustible gases prior to consumption, except at the burner or in a standard torch or blow pipe, shall not be allowed unless approved.
The storage or use of a single cylinder of oxygen and a single cylinder of fuel gas located on a cart shall be allowed without requiring the cylinders to be separated in accordance with Section 5003.9.8 or 5003.10.3.6 when the cylinders are connected to regulators, ready for service, equipped with apparatus designed for cutting or welding and all of the following:
- Carts shall be kept away from the cutting or welding operation in accordance with Section 3505.5 or fire-resistant shields shall be provided.
- Cylinders shall be secured to the cart to resist movement.
- Carts shall be in accordance with Section 5003.10.3.
- Cylinder valves not having fixed hand wheels shall have keys, handles or nonadjustable wrenches on valve stems while the cylinders are in service.
- Cylinder valve outlet connections shall conform to the requirements of CGA V-1.
- Cylinder valves shall be closed when work is finished.
- Cylinder valves shall be closed before moving the cart.
Individual carts shall be separated from each other in accordance with Section 5003.9.8.
Acetylene gas shall not be piped except in approved cylinder manifolds and cylinder manifold connections, or utilized at a pressure exceeding 15 pounds per square inch gauge (psig) (103 kPa) unless dissolved in a suitable solvent in cylinders manufactured in accordance with DOTn 49 CFR Part 178. Acetylene gas shall not be brought in contact with unalloyed copper, except in a blowpipe or torch.
The torch valve shall be closed and the gas supply to the torch completely shut off when gas welding or cutting operations are discontinued for a period of 1 hour or more.
The frame or case of electric hot work machines, except internal-combustion-engine-driven machines, shall be grounded. Ground connections shall be mechanically strong and electrically adequate for the required current.
Welding current return circuits from the work to the machine shall have proper electrical contact at joints. The electrical contact shall be periodically inspected.
Electrodes shall be removed from the holders when electric arc welding or cutting is discontinued for any period of 1 hour or more. The holders shall be located to prevent accidental contact and the machines shall be disconnected from the power source.
A switch or circuit breaker shall be provided so that fixed electric welders and control equipment can be disconnected from the supply circuit. The disconnect shall be installed in accordance with NFPA 70.
Damaged cable shall be removed from service until properly repaired or replaced.
Storage and handling of calcium carbide shall comply with Chapter 50 of this code and Chapter 9 of NFPA 51.
The use of acetylene generators shall comply with this section and Chapter 6 of NFPA 51A.
The minimum volume of rooms containing portable generators shall be 35 times the total gas-generating capacity per charge of all generators in the room. The gas-generating capacity in cubic feet per charge shall be assumed to be 4.5 times the weight of carbide per charge in pounds. The minimum ceiling height of rooms containing generators shall be 10 feet (3048 mm). An acetylene generator shall not be moved by derrick, crane or hoist while charged.
Piping shall be protected against physical damage.
Signage shall be provided for piping and hose systems as follows:
- Above-ground piping systems shall be marked in accordance with ASME A13.1.
- Station outlets shall be marked to indicate their intended usage.
- Signs shall be posted, indicating clearly the location and identity of section shutoff valves.
Signs shall be posted for oxygen manifolds with service pressures not exceeding 200 psig (1379 kPa). Such signs shall include the words:
DO NOT CONNECT HIGH-PRESSURE CYLINDERS
MAXIMUM PRESSURE 250 PSIG
Hose connections shall be clamped or otherwise securely fastened.
Hoses shall be inspected frequently for leaks, burns, wear, loose connections or other defects rendering the hose unfit for service.