|1.2D + 1.0L + 1.6Z||(Equation 3-1)|
|1.2D + 1.2Rr||(Equation 3-2)|
|D + 0.75L + 0.75Z||(Equation 3-3)|
|D + 0.75Rr||(Equation 3-4)|
|D||=||dead load as defined by the building code|
|L||=||live load as defined by Section 303.2|
|Z||=||horizontal sway loads as defined by Section 303.4.2 and Section 303.4.3|
|Rr||=||guard or handrail loads as defined in Table 303.2|
- Dumpsters or containers in areas protected by an approved automatic sprinkler system installed throughout in accordance with Section 903.3.1.1, 903.3.1.2 or 903.3.1.3.
- Storage in a structure shall not be prohibited where the structure is of Type I or IIA construction, located not less than 10 feet (3048 mm) from other buildings and used exclusively for dumpster or container storage.
- LP-gas-fueled devices used for sweating pipe joints or removing paint in accordance with Chapter 61.
- Cutting and welding operations in accordance with Chapter 35.
- Torches or flame-producing devices in accordance with Section 308.4.
- Candles and open-flame decorative devices in accordance with Section 308.3.
- Open-flame devices are allowed to be used in the following situations, provided approved precautions are taken to prevent ignition of a combustible material or injury to occupants:
- Where necessary for ceremonial or religious purposes in accordance with Section 308.1.7.
- On stages and platforms as a necessary part of a performance in accordance with Section 308.3.2.
- Where candles on tables are securely supported on substantial noncombustible bases and the candle flames are protected.
- Heat-producing equipment complying with Chapter 6 and the International Mechanical Code.
- Gas lights are allowed to be used provided adequate precautions satisfactory to the fire code official are taken to prevent ignition of combustible materials.
- Class I and Class II liquids and LP-gas shall not be used.
- Liquid- or solid-fueled lighting devices containing more than 8 ounces (237 ml) of fuel must self-extinguish and not leak fuel at a rate of more than 0.25 teaspoon per minute (1.26 ml per minute) if tipped over.
- The device or holder shall be constructed to prevent the spillage of liquid fuel or wax at the rate of more than 0.25 teaspoon per minute (1.26 ml per minute) when the device or holder is not in an upright position.
- The device or holder shall be designed so that it will return to the upright position after being tilted to an angle of 45 degrees from vertical.
5. The flame shall be enclosed except where openings on the side are not more than 0.375-inch (9.5 mm) diameter or where openings are on the top and the distance to the top is such that a piece of tissue paper placed on the top will not ignite in 10 seconds.
6. Chimneys shall be made of noncombustible materials and securely attached to the open-flame device.
7. Fuel canisters shall be safely sealed for storage.
10. Candelabras with flame-lighted candles shall be securely fastened in place to prevent overturning, and shall be located away from occupants using the area and away from possible contact with drapes, curtains or other combustibles.
- When the premises have been cleared of all combustible materials and debris and, in the opinion of the fire code official, the type of construction, fire separation distance and security of the premises do not create a fire hazard.
- Where approved by the fire chief, buildings that will not be heated and where fire protection systems will be exposed to freezing temperatures, fire alarm and sprinkler systems are permitted to be placed out of service and standpipes are permitted to be maintained as dry systems (without an automatic water supply), provided the building has no contents or storage, and windows, doors and other openings are secured to prohibit entry by unauthorized persons.
- This symbol shall mean that the structure had normal structural conditions at the time of marking.
- This symbol shall mean that structural or interior hazards exist and interior fire-fighting or rescue operations should be conducted with extreme caution.
- This symbol shall mean that structural or interior hazards exist to a degree that consideration should be given to limit fire fighting to exterior operations only, with entry only occurring for known life hazards.
- Vacant marker hazard identification symbols: The following symbols shall be used to designate known hazards on the vacant building marker. They shall be placed directly above the symbol.
- R/O—Roof open
- S/M—Stairs, steps and landing missing
- F/E—Avoid fire escapes
- H/F—Holes in floor
- Constructed of steel not less than 4 inches (102 mm) in diameter and concrete filled.
- Spaced not more than 4 feet (1219 mm) between posts on center.
- Set not less than 3 feet (914 mm) deep in a concrete footing of not less than a 15-inch (381 mm) diameter.
- Set with the top of the posts not less than 3 feet (914 mm) above ground.
- Located not less than 3 feet (914 mm) from the protected object.
- Buildings or rooms constructed for such use in accordance with the International Building Code.
- Where allowed by Section 314.
- Storage of equipment utilized for maintenance purposes is allowed in approved locations when the aggregate fuel capacity of the stored equipment does not exceed 10 gallons (38 L) and the building is equipped throughout with an automatic sprinkler system installed in accordance with Section 903.3.1.1.
|These sections on equipment rooms are rewritten from the previous code to clarify where storage is allowed, and they remove the requirement for the rooms to be protected with a fire-extinguishing system, fire sprinklers. The electrical section specifies where storage is not allowed. It was not the intent of the code to prohibit storage in rooms that only had electrical circuit breaker panels. Storage around circuit breaker panels is addressed in Section 605.3.|
- The separation distance is allowed to be reduced to 3 feet (914 mm) for storage not exceeding 6 feet (1829 mm) in height.
- The separation distance is allowed to be reduced when the fire code official determines that no hazard to the adjoining property exists.
- Such obstruction shall be permitted where the wire, cable, rope, antenna or suspended obstruction is encased in a white, 2-inch (51 mm) minimum diameter plastic pipe or an approved equivalent.
- Such obstruction shall be permitted where there is a solid obstruction below such that accidentally walking into the wire, cable, rope, antenna or suspended obstruction is not possible.
- Maintain an effective fire break by removing and clearing away flammable vegetation and combustible growth from areas within 30 feet (9144 mm) of such buildings or structures.
Exception: Single specimens of trees, ornamental shrubbery or similar plants used as ground covers, provided they do not form a means of rapidly transmitting fire from the native growth to any structure.
- Maintain additional fire protection or firebreak by removing brush, flammable vegetation and combustible growth located from 30 feet to 100 feet (9144 mm to 30 480 mm) from such buidlings or structures, when required by the fire chief because of extra hazardous conditions causing a firebreak of only 30 feet (9144 mm) to be insufficient to provide reasonable fire safety.
Exception: Grass and other vegetation located more than 30 feet (9144 mm) from buildings or structures and less than 18 inches (457 mm) in height above the ground need not be removed where necessary to stabilize the soil and prevent erosion.
- Remove portions of trees that extend within 10 feet (3048 mm) of the outlet of a chimney.
- Maintain trees adjacent to or overhanging a building free of deadwood.
- Maintain the roof of a structure free of leaves, needles or other dead vegetative growth.