Heads up: There are no amended sections in this chapter.
Materials used in the construction of outdoor installations shall be weather resistant. Where wood is used, it shall be naturally durable or preservative-treated wood as defined in the building code or other approved material. Where ferrous metal is used, it shall be protected from corrosion. Fasteners shall consist of aluminum or other approved corrosion-resistant materials or shall be provided with approved corrosion-resistant coatings such as copper or zinc.
Installations located in interior corrosive environments, such as those located in conjunction with indoor pools, shall be corrosion resistant.
The structural design shall be in accordance with the building code.
Bleachers, folding and telescopic seating, and grandstands shall be designed for a uniform live load of 100 pounds per square foot (psf) (4788 Pa). Press boxes shall be designed for a uniform live load of 50 psf (2394 Pa). The components of the installation shall be designed to support the loads listed in Table 303.2.
|TIERED SEATING ELEMENT||LOAD TYPE||LOAD|
|Seats (vertical)||L||120 pounds per linear foot.|
|Treads||L||Stair treads and aisle stair treads shall be designed to resist a minimum concentrated load of 300|
pounds on an area of 4 square inches.
|Handrails and guards, |
|Rr||Handrail assemblies and guards shall be designed to resist a load of 50 pounds per linear foot |
(pound per foot) applied in any direction at the top. The supporting elements shall transfer this
load to the structure.
|Handrails and guards, |
|Rr||Handrail assemblies and guards shall be able to resist a single concentrated load of 200 pounds, |
applied in any direction at any direction along the top. Attachment devices and supporting elements
shall transfer this load to the structure.
|Guards, infill components||Rr||Intermediate rails (all those except the handrail), balusters, and panel fillers (including flexible |
infill components) shall be designed to withstand a horizontally applied normal load of 50 pounds
on an area equal to 1 square foot, including openings and space between rails. Application of the
loads shall not allow guard openings greater than that permitted by Sections 408.2.and 503.2.
|For SI: 1 square inch = 645.46 mm2, 1 square foot = 0.0929 m2, 1 pound = 4.448 N, 1 pound per linear foot = 14.594 N/m.|
A horizontal load of 24 pounds per linear foot shall be applied parallel to seating at the footboard level of each row of seating.
A horizontal load of 10 pounds per linear foot shall be applied perpendicular to seating at the footboard level of each row of seating.
In addition to the load combinations required to be considered for design in accordance with the building code, the additional load combinations in Section 303.5.1.or in Section 303.5.2.shall be considered. Parallel and perpendicular sway loads need not be considered simultaneously. Also uniform, concentrated and infill loads need not be considered simultaneously.
When using allowable stress design the following additional load combination must be considered.
|D + 0.75L + 0.75Z||(Equation 3-3)|
|D + 0.75Rr||(Equation 3-4)|
The following notations shall, for the purpose of this chapter, have the meanings shown herein.
|D||=||dead load as defined by the building code|
|L||=||live load as defined by Section 303.2|
|Z||=||horizontal sway loads as defined by Section 303.4.2.and Section 303.4.3|
|Rr||=||guard or handrail loads as defined in Table 303.2|
A smoke-protected assembly seating area with a roof shall have the lowest portion of the roof deck not less than 15 feet (4572 mm) above the highest aisle or aisle accessway.
The electrical system shall comply with the electrical code.
Fire protection systems shall be provided where required by the building code.
- An emergency voice/alarm system is not required for outdoor bleacher-type seating provided all of the following are met:
- The bleacher-type seating has an occupant load of less than 15,000;
- A public address system with standby power is provided;
- Enclosed spaces attached or immediately adjacent to the bleacher-type seating comprise, in the aggregate, 10% or less of the overall area of the bleacher-type seating or 1,000 square feet (92.9 square meters), whichever is less.
- Spaces under the bleacher-type seating shall be separated from the bleacher-type seating in accordance with Section 1028.1.1.1 of the International Building Code.
- All means of egress from the bleacher-type seating are open to the outside.
- An emergency voice/alarm system is not required for outdoor bleacher-type seating with an occupant load of 300 or less.
- An emergency voice/alarm system is not required for temporary outdoor bleacher-type seating providing all of the following are met:
- There are no enclosed spaces under or attached to the bleacher-type seating;
- The bleacher-type seating is erected for a period of less than 180 days;
- Evacuation of the bleacher-type seating is included in an approved fire safety plan.
Tiered seating shall be accessible as required by the building code.
Where an opening between the seatboard and footboard is located more than 30 inches (762 mm) above the floor or ground below, the opening shall be closed with construction such that a 4-inch-diameter (102 mm) sphere cannot pass through.