Plumbing fixtures, faucets and fixture fittings shall have smooth impervious surfaces, shall be free from defects, shall not have concealed fouling surfaces, and shall conform to the standards indicated in Table P2701.1 and elsewhere in this code.
|Air gap fittings for use with plumbing fixtures, appliances and appurtenances||ASME A112.1.3|
|Bathtub/whirlpool pressure-sealed doors||ASME A112.19.15|
|Diverters for faucets with hose spray, anti-syphon type, residential application||ASTM A112.18.1/CSA B125.1|
|Enameled cast-iron plumbing fixtures||ASME A112.19.1M/CSA B45.2|
|Floor drains||ASME A112.6.3|
|Floor-affixed supports for off-the-floor plumbing fixtures for public use||ASME A112.6.1M|
|Framing-affixed supports for off-the-floor water closets with concealed tanks||ASME A112.6.2|
|Hose connection vacuum breaker||ASSE 1052|
|Hot water dispensers, household storage type, electrical||ASSE 1023|
|Household disposers||ASSE 1008|
|Hydraulic performance for water closets and urinals||ASME A 112.19.2/CSA B45.1|
|Individual automatic compensating valves for individual fixture fittings||ASME A 112.18.1/CSA B125.1|
|Individual shower control valves anti-scald||ASSE 1016/ASMEA 112.1016/CSAB125.16|
|Macerating toilet systems and related components||ASME A 112.3.4/CSA B45.9|
|Nonvitreous ceramic plumbing fixtures||ASME A 112.19.2/CSA B45.1|
|Plastic bathtub units||CSAB45.5/IAPMO Z124, ASME A112.19.2/CSA B45.1|
|Plastic lavatories||CSA B45.5/IAPMO Z124|
|Plastic shower receptors and shower stall||CSA B45.5/IAPMO Z124|
|Plastic sinks||CSA B45.5/IAPMO Z124|
|Plastic water closet bowls and tanks||CSA B45.5/IAPMO Zl24|
|Plumbing fixture fittings||ASME A 112.18.1/CSA B125.1|
|Plumbing fixture waste fittings||ASME A 112.18.2/CSA B125.2, ASTM F409|
|Porcelain-enameled formed steel plumbing fixtures||ASME A 112.19.1/CSA B45.2|
|Pressurized flushing devices for plumbing fixtures||ASSE 1037, CSA B125.3|
|Specification for copper sheet and strip for building construction||ASTMB370|
|Stainless steel plumbing fixtures||ASME A 112.19.3/CSA B45.4|
|Suction fittings for use in whirlpool bathtub appliances||ASME A 112.19.7 /CSA B45.10|
|Temperature-actuated, flow reduction valves to individual fixture fittings||ASSE 1062|
|Thermoplastic accessible and replaceable plastic tube and tubular fittings||ASTM F409|
|Trench drains||ASME A 112.6.3|
|Trim for water closet bowls, tanks and urinals||ASME A 112.19.5/CSA B45.15|
|Vacuum breaker wall hydrant-frost-resistant, automatic-draining type||ASSE 1019|
|Vitreous china plumbing fixtures||ASME A 112.19.2/CSA B45.1|
|Wall-mounted and pedestal-mounted, adjustable and pivoting lavatory and sink
|ASME A 112.19.12|
|Water closet flush tank fill valves||ASSE 1002, CSA B125.3|
|Whirlpool bathtub appliances||ASME A 112.19.7 /CSA B45.10|
Plastic tubular fittings shall conform to ASTM F409 as indicated in Table P2701.1.
Carriers for wall-hung water closets shall conform to ASME A112.6.1 or ASME A112.6.2
Slip joints shall be made with an approved elastomeric gasket and shall be installed only on the trap outlet, trap inlet and within the trap seal. Fixtures with concealed slip-joint connections shall be provided with an access panel or utility space not less than 12 inches (305 mm) in its smallest dimension or other approved arrangement so as to provide access to the slip connections for inspection and repair.
The installation of fixtures shall conform to the following:
- Floor-outlet or floor-mounted fixtures shall be secured to the drainage connection and to the floor, where so designed, by screws, bolts, washers, nuts and similar fasteners of copper, copper alloy or other corrosion-resistant material.
- Wall-hung fixtures shall be rigidly supported so that strain is not transmitted to the plumbing system.
- Where fixtures come in contact with walls and floors, the contact area shall be water tight.
- Plumbing fixtures shall be usable.
- Water closets, lavatories and bidets. A water closet, lavatory or bidet shall not be set closer than 15 inches (381 mm) from its center to any side wall, partition or vanity or closer than 30 inches (762 mm) center-to-center between adjacent fixtures. There shall be a clearance of not less than 21 inches (533 mm) in front of a water closet, lavatory or bidet to any wall, fixture or door.
- The location of piping, fixtures or equipment shall not interfere with the operation of windows or doors.
- In flood hazard areas as established by Table R301.2(1), plumbing fixtures shall be located or installed in accordance with Section R322.1.7.
- Integral fixture-fitting mounting surfaces on manufactured plumbing fixtures or plumbing fixtures constructed on site, shall meet the design requirements of ASME A112.19.2/CSA B45.1 or ASME Al 12.19.3/CSA B45.4.
For other than hub drains that receive only clear-water waste and standpipes, a removable strainer or basket shall cover the waste outlet of waste receptors. Waste receptors shall not be installed in concealed spaces. Waste receptors shall not be installed in plenums, attics, crawl spaces or interstitial spaces above ceilings and below floors. Waste receptors shall be readily accessible.
Standpipes shall extend not less than 18 inches (457 mm) and not greater than 42 inches (1067 mm) above the trap weir.
Where a laundry tray waste line connects into a standpipe for an automatic clothes washer drain, the standpipe shall extend not less than 30 inches (762 mm) above the standpipe trap weir and shall extend above the flood level rim of the laundry tray. The outlet of the laundry tray shall not be greater than 30 inches (762 mm) horizontally from the standpipe trap.
Shower compartments shall have not less than 900 square inches (0.6 m2) of interior cross-sectional area. Shower compartments shall be not less than 30 inches (762 mm) in minimum dimension measured from the finished interior dimension of the shower compartment, exclusive of fixture valves, shower heads, soap dishes, and safety grab bars or rails. The minimum required area and dimension shall be measured from the finished interior dimension at a height equal to the top of the threshold and at a point tangent to its centerline and shall be continued to a height of not less than 70 inches (1778 mm) above the shower drain outlet. Hinged shower doors shall open outward. The wall area above builtin tubs having installed shower heads and in shower compartments shall be constructed in accordance with Section R702.4. Such walls shall form a water-tight joint with each other and with either the tub, receptor or shower floor.
- Fold-down seats shall be permitted in the shower, provided the required 900-square-inch (0.6 m2) dimension is maintained when the seat is in the folded-up position.
- Shower compartments having not less than 25 inches (635 mm) in minimum dimension measured from the finished interior dimension of the compartment provided that the shower compartment has a cross-sectional area of not less than 1,300 square inches (0.838 m2).
The shower compartment access and egress opening shall have a clear and unobstructed finished width of not less than 22 inches (559 mm).
Individual shower and tub/ shower combination valves shall be equipped with control valves of the pressure-balance, thermostatic-mixing or combination pressure-balance/thermostatic-mixing valve types with a high limit stop in accordance with ASSE 1016/ASME A112.1016/CSA B125.16. The high limit stop shall be set to limit the water temperature to not greater than 120°F (49°C). In-line thermostatic valves shall not be used for compliance with this section.
Hand-held showers shall conform to ASME A112.18.1/CSA B125.1. Hand-held showers shall provide backflow protection in accordance with ASME A112.18.1/CSA B125.1 or shall be protected against backflow by a device complying with ASME A112.18.3.
Where a shower receptor has a finished curb threshold, it shall be not less than 1 inch (25 mm) below the sides and back of the receptor. The curb shall be not less than 2 inches (51 mm) and not more than 9 inches (229 mm) deep when measured from the top of the curb to the top of the drain. The finished floor shall slope uniformly toward the drain not less than 1⁄4 unit vertical in 12 units horizontal (2-percent slope) nor more than 1⁄2 unit vertical per 12 units horizontal (4-percent slope) and floor drains shall be flanged to provide a water-tight joint in the floor.
The adjoining walls and floor framing enclosing on-site built-up shower receptors shall be lined with 1 of the following:
- Sheet lead.
- Sheet copper.
- Plastic liner material that complies with ASTM D4068 or ASTM D4551.
- Sheet-applied load-bearing, bonded waterproof membranes that comply with ANSI A118.10.
Plasticized polyvinyl chloride (PVC) sheet shall meet the requirements of ASTM D4551. Sheets shall be joined by solvent welding in accordance with the manufacturer's instructions.
Nonplasticized chlorinated polyethylene sheet shall meet the requirements of ASTM D4068. The liner shall be joined in accordance with the manufacturer's instructions.
Liquid-type, trowel-applied, load-bearing, bonded waterproof materials shall meet the requirements of ANSI A118.10 and shall be applied in accordance with the manufacturer's instructions.
Lining materials shall be sloped one-fourth unit vertical in 12 units horizontal (2-percent slope) to weep holes in the subdrain by means of a smooth, solidly formed subbase, shall be properly recessed and fastened to approved backing so as not to occupy the space required for the wall covering, and shall not be nailed or perforated at any point less than 1 inch (25.4 mm) above the finished threshold.
Lead and copper linings shall be insulated from conducting substances other than the connecting drain by 15-pound (6.80 kg) asphalt felt or its equivalent. Sheet lead liners shall weigh not less than 4 pounds per square foot (19.5 kg/m2). Sheet copper liners shall weigh not less than 12 ounces per square foot (3.7 kg/m2). Joints in lead and copper pans or liners shall be burned or silver brazed, respectively. Joints in plastic liner materials shall be joined in accordance with the manufacturer's instructions.
Walls in shower compartments and walls above bathtubs that have a wall-mounted showerhead shall be finished in accordance with Section R307.2.
Lavatories shall conform to ASME A112.19.1/CSA B45.2, ASME A112.19.2/CSA B45.1, ASME A112.19.3/CSA B45.4 or CSA B45.5/IAPMO Z124.
Cultured marble vanity tops with an integral lavatory shall conform to CSA B45.5/IAPMO Z124.
Movable lavatory systems shall comply with ASME A112.19.12.
Water closets shall conform to the water consumption requirements of Section P2903.2 and shall conform to ASME A112.19.2/CSA B45.1, ASME A112.19.3/ CSA B45.4 or CSA B45.5/IAPMO Z124. Water closets shall conform to the hydraulic performance requirements of ASME A112.19.2/CSA B45.1. Water closet tanks shall conform to ASME A112.19.2/CSA B45.1, ASME A112.19.3/CSA B45.4 or CSA B45.5/IAPMO Z124. Water closets that have an invisible seal and unventilated space or walls that are not thoroughly washed at each discharge shall be prohibited. Water closets that allow backflow of the contents of the bow 1 into the flush tank shall be prohibited. Water closets equipped with a dual flushing device shall comply with ASME A112.19.14.
An adequate quantity of water shall be provided to flush and clean the fixture served. The water supply to flushing devices equipped for manual flushing shall be controlled by a float valve or other automatic device designed to refill the tank after each discharge and to completely shut off the water flow to the tank when the tank is filled to operational capacity. Provision shall be made to automatically supply water to the fixture so as to refill the trap after each flushing.
Flush valve seats in tanks for flushing water closets shall be not less than 1 inch (25 mm) above the flood-level rim of the bowl connected thereto, except an approved water closet and flush tank combination designed so that when the tank is flushed and the fixture is clogged or partially clogged, the flush valve will close tightly so that water will not spill continuously over the rim of the bowl or backflow from the bowl to the tank.
Flush tanks shall be provided with overflows discharging to the water closet connected thereto and such overflow shall be of sufficient size to prevent flooding the tank at the maximum rate at which the tanks are supplied with water according to the manufacturer's design conditions.
Parts in a flush tank shall be accessible for repair and replacement.
Water closets shall be equipped with seats of smooth, nonabsorbent material and shall be properly sized for the water closet bowl type.
Sheet copper used for flush tank linings shall have a weight of not less than 10 ounces per square foot (3 kg/m2).
Electro-hydraulic water closets shall conform to ASME A112.19.2/CSA B45.1.
Doors within a bathtub enclosure shall conform to ASME A112.19.15.
Hot water supplied to bathtubs and whirlpool bathtubs shall be limited to a temperature of not greater than 120°F (49°C) by a water-temperature limiting device that conforms to ASSE 1070 or CSA B125.3, except where such protection is otherwise provided by a combination tub/shower valve in accordance with Section P2708.4.
Movable sink systems shall comply with ASME A112.19.12.
A sink equipped with a food-waste disposer shall be provided with a faucet.
The combined discharge from a dishwasher and a one- or two-compartment sink, with or without a food-waste disposer, shall be served by a trap of not less than 11⁄2 inches (38 mm) in outside diameter. The dishwasher discharge pipe or tubing shall rise to the underside of the counter and be fastened or otherwise held in that position before connecting to the head of the food-waste disposer or to a wye fitting in the sink tailpiece.
The discharge from a clothes washing machine shall be through an air break.
Floor drains shall have waste outlets not less than 2 inches (51 mm) in diameter and a removable strainer. Floor drains shall be constructed so that the drain can be cleaned. Access shall be provided to the drain inlet. Floor drains shall not be located under or have their access restricted by permanently installed appliances.
Access shall be provided to circulation pumps in accordance with the fixture or pump manufacturer's installation instructions. Where the manufacturer's instructions do not specify the location and minimum size of field-fabricated access openings, an opening of not less than 12-inches by 12-inches (305 mm by 305 mm) shall be installed for access to the circulation pump. Where pumps are located more than 2 feet (610 mm) from the access opening, an opening of not less than 18 inches by 18 inches (457 mm by 457 mm) shall be installed. A door or panel shall be permitted to close the opening. The access opening shall be unobstructed and be of the size necessary to permit the removal and replacement of the circulation pump.
Leak testing and pump operation shall be performed in accordance with the manufacturer's instructions.
The product shall be installed in accordance with the manufacturer's instructions.
The bidet shall be equipped with either an air-gap-type or vacuum-breaker-type fixture supply fitting.
The discharge water temperature from a bidet fitting shall be limited to not greater than 110°F (43°C) by a water-temperature-limiting device conforming to ASSE 1070 or CSA B125.3.
Fixture supply valves and faucets shall comply with ASME A112.18.1/CSA Bl25.1 as indicated in Table P2701.1. Faucets and fixture fittings that supply drinking water for human ingestion shall conform to the requirements of NSF 61, Section 9. Flexible water connectors shall conform to the requirements of Section P2905.7.
Fixture fittings supplied with both hot and cold water shall be installed and adjusted so that the left-hand side of the water temperature control represents the flow of hot water when facing the outlet.
Personal hygiene devices integral to water closets or water closet seats shall conform to ASME A112.4.2.
Macerating toilet systems shall be installed in accordance with manufacturer's instructions.
The size of the drain from the macerating toilet system shall be not less than 3⁄4 inch (19 mm) in diameter
Materials, design, construction and performance of nonliquid saturated treatment systems shall comply with NSF 41.