The air removed by every mechanical exhaust system shall be discharged to the outdoors in accordance with Section M1506.2. Air shall not be exhausted into an attic, soffit, ridge vent or crawl space.
Clothes dryers shall be exhausted in accordance with the manufacturer's instructions.
Exhaust duct termination s shall be in accordance with the dryer manufacturer's installation instructions. If the manufacturer's instructions do not specify a termination location, the exhaust duct shall terminate no less than 3 feet (914 mm) in any direction from openings into buildings or ventilated section in a soffit. Exhaust duct terminations shall be equipped with a backdraft damper. Screens shall not be installed at the duct termination.
Dryer exhaust ducts shall conform to the requirements of Sections M1502.4.1 through M1502.4.7.
Dryer exhaust ducts shall be supported at 4 foot (1219 mm) intervals and secured in place. The insert end of the duct shall extend into the adjoining duct or fitting in the direction of airflow. Ducts shall not be joined with screws or similar fasteners that protrude into the inside of the duct.
Transition ducts used to connect the dryer to the exhaust duct system shall be a single length that is listed and labeled in accordance with UL 2158A. Transition ducts shall be not greater than 8 feet (2438 mm) in length. Transition ducts shall not be concealed within construction.
The maximum length of the exhaust duct shall be 35 feet (10668 mm) from the connection to the transition duct from the dryer to the outlet terminal. Where fittings are used, the maximum length of the exhaust duct shall be reduced in accordance with Table M1502.4.5.1. The maximum length of the exhaust duct does not include the transition duct.
For SI: 1 inch = 25.4 mm, l foot= 304.8 mm, 1 degree = 0.0175 rad.
|DRYER EXHAUST DUCT FITTING TYPE||EQUIVALENT LENGTH|
|4 inch radius mitered 45 degree elbow||2 feet 6 inches|
|4 inch radius mitered 90 degree elbow||5 feet|
|6 inch radius smooth 45 degree elbow||1 foot|
|6 inch radius smooth 90 degree elbow||1 foot 9 inches|
|8 inch radius smooth 45 degree elbow||1 foot|
|8 inch radius smooth 90 degree elbow||1 foot 7 inches|
|10 inch radius smooth 45 degree elbow||9 inches|
|10 inch radius smooth 90 degree elbow||1 foot 6 inches|
The size and maximum length of the exhaust duct shall be determined by the dryer manufacturer's installation instructions. The code official shall be provided with a copy of the installation instructions for the make and model of the dryer at the concealment inspection. In the absence of fitting equivalent length calculations from the clothes dryer manufacturer, Table M1502.4.4.1 shall be used.
The maximum length of the exhaust duct shall be determined in accordance with the manufacturer's instructions for the dryer exhaust duct power ventilator.
Where space for a clothes dryer is provided, an exhaust duct system shall be installed. Where the clothes dryer is not installed at the time of occupancy the exhaust duct shall be capped or plugged in the space in which it originates and identified and marked "future use."
Exception: Where a listed condensing clothes dryer is installed prior to occupancy of the structure.
Protective shield plates shall be placed where nails or screws from finish or other work are likely to penetrate the clothes dryer exhaust duct. Shield plates shall be placed on the finished face of framing members where there is less than 11⁄4 inches (32 mm) between the duct and the finished face of the framing member. Protective shield plates shall be constructed of steel, shall have a minimum thickness of 0.062-inch (1.6 mm) and shall extend not less than 2 inches (51 mm) above sole plates and below top plates.
Range hoods shall discharge to the outdoors through a duct. The duct serving the hood shall have a smooth interior surface, shall be air tight, shall be equipped with a back-draft damper and shall be independent of all other exhaust systems. Ducts serving range hoods shall not terminate in an attic or crawl space or areas inside the building.
Ducts serving range hoods shall be constructed of galvanized steel, stainless steel or copper.
Exception: Ducts for domestic kitchen cooking appliances equipped with down-draft exhaust systems shall be permitted to be constructed of schedule 40 PVC pipe and fittings provided that the installation complies with all of the following:
- The duct is installed under a concrete slab poured on grade.
- The underfloor trench in which the duct is installed is completely backfilled with sand or gravel.
- The PVC duct extends not more than 1 inch (25 mm) above the indoor concrete floor surface.
- The PVC duct extends not more than 1 inch (25 mm) above grade outside of the building.
- The PVC ducts are solvent cemented.
Exhaust hood systems capable of exhausting in excess of 400 cubic feet per minute (0.19 m3⁄s) shall be mechanically or naturally provided with makeup air at a rate approximately equal to the exhaust air rate. Such makeup air systems shall be equipped with not less than one damper. Each damper shall be a gravity damper or an electrically operated damper that automatically opens when the exhaust system operates. Dampers shall be accessible for inspection, service, repair and replacement without removing permanent construction or any other ducts not connected to the damper being inspected, serviced, repaired or replaced.
Kitchen exhaust makeup air shall be discharged into the same room in which the exhaust system is located or into rooms or duct systems that communicate through one or more permanent openings with the room in which such exhaust system is located. Such permanent openings shall have a net cross-sectional area not less than the required area of the makeup air supply openings.
Domestic open-top broiler units shall have a metal exhaust hood, having a minimum thickness of 0.0157-inch (0.3950 mm) (No. 28 gage) with 1⁄4 inch (6.4 mm) clearance between the hood and the underside of combustible material or cabinets. A clearance of not less than 24 inches (610 mm) shall be maintained between the cooking surface and the combustible material or cabinet. The hood shall be not less than the width of the broiler unit, extend over the entire unit, discharge to the outdoors and be equipped with a backdraft damper or other means to control infiltration/exfiltration when not in operation. Broiler units incorporating an integral exhaust system, and listed and labeled for use without an exhaust hood, need not have an exhaust hood.
Where exhaust duct construction is not specified in this chapter, construction shall comply with Chapter 16.
The length of exhaust and supply ducts used with ventilating equipment shall not exceed the lengths determined in accordance with Table M1506.2.
Exception: Duct length shall not be limited where the duct system complies with the manufacturer's design criteria or where the flow rate of the installed ventilating equipment is verified by the installer or approved third party using a flow hood, flow grid or other airflow measuring device.
For SI: 1 foot = 304.8 mm.
|DUCT TYPE||FLEX DUCT||SMOOTH-WALL DUCT|
|Fan airflow rating
(CFM @ 0.25 inch wca)
|8 and above||NL||NL||NL||NL||NL||189||111||69||NL||NL||NL||NL||NL||NL||198||133|
- Fan airflow rating shall be in acordance with ANSVAMCA 210-ANSI/AS HRAE 51.
- For noncircular ducts, calculate the diameter as four times the cross-sectional area divided by the perimeter.
- This table assumes that elbows are not used. Fifteen feet of allowable duct length shall be deducted for each elbow installed in the duct run.
- NL = no limit on duct length of this size.
- X = not allowed. Any length of duct of this size with assumed turns and fittings will exceed the rated pressure drop.
Air exhaust openings shall terminate not less than 3 feet (914 mm) from property lines; 3 feet (914 mm) from operable and nonoperable openings into the building and 10 feet (3048 mm) from mechanical air intakes except where the opening is located 3 feet (914 mm) above the air intake. Openings shall comply with Sections R303.5.2 and R303.6.
The whole-house ventilation system shall consist of one or more supply or exhaust fans, or a combination of such, and associated ducts and controls. Local exhaust or supply fans are permitted to serve as such a system. Outdoor air ducts connected to the return side of an air handler shall be considered as providing supply ventilation.
The whole-house mechanical ventilation system shall provide outdoor air at a continuous rate of not less than that determined in accordance with Table M1507.3.3(1).
Exception: The whole-house mechanical ventilation system is permitted to operate intermittently where the system has controls that enable operation for not less than 25-percent of each 4-hour segment and the ventilation rate prescribed in Table M1507.3.3(1) is multiplied by the factor determined in accordance with Table M1507.3.3(2).
For SI: 1 square foot = 0.0929 m2, 1 cubic foot per minute = 0.0004719 m3/s.
|NUMBER OF BEDROOMS|
|Airflow in CFM|
|1,501 - 3,000||45||60||75||90||105|
|3,001 - 4,500||60||75||90||105||120|
|4,501 - 6,000||75||90||105||120||135|
|6,001 - 7,500||90||105||120||135||150|
|RUN-TIME PERCENTAGE IN EACH 4-HOUR
- For ventilation system run time values between those given, the factors are permitted to be determined by interpolation.
- Extrapolation beyond the table is prohibited.
Local exhaust systems shall be designed to have the capacity to exhaust the minimum air flow rate determined in accordance with Table M1507.4.
For SI: 1 cubic foot per minute = 0.0004719 m3/s.
|AREA TO BE EXHAUSTED||EXHAUST RATES|
|Kitchens||100 cfm intermittent or 25 cfm continuous|
|Bathrooms-Toilet Rooms||Mechanical exhaust capacity of 50 cfm intermittent or 20 cfm continuous|