Heads up: There are no amended sections in this chapter.
This appendix is informative and is not part of this code.
This section shall govern the replacement of existing building sewer piping by pipe-bursting methods.
The existing piping sections to be replaced shall be inspected internally by a recorded video camera survey. The survey shall include notations of the position of cleanouts and the depth of connections to the existing piping.
The replacement piping shall be manufactured with a standard dimension ratio (SDR) of 17 and in compliance with ASTM F714.
Pipe fittings to be connected to the replacement piping shall be of extra-high molecular weight PE3408 material and shall be manufactured with an SDR of 17 and in compliance with ASTM D2683.