Heads up: There are no amended sections in this chapter.
Appendix U Solar-Ready Provisions—Detached One- And Two-Family Dwellings, Multiple Single-Family Dwellings (Townhouses)
(The provisions contained in this appendix are not mandatory unless specifically referenced in the adopting ordinance.)
These provisions shall be applicable for new construction where solar-ready provisions are required.
SOLAR-READY ZONE. A section or sections of the roof or building overhang designated and reserved for the future installation of a solar photovoltaic or solar thermal system.
New detached one- and two-family dwellings, and multiple single-family dwellings (townhouses) with not less than 600 square feet (55.74 m2) of roof area oriented between 110 degrees and 270 degrees of true north shall comply with sections U103.2 through U103.8.
- New residential buildings with a permanently installed on-site renewable energy system.
- A building with a solar-ready zone that is shaded for more than 70 percent of daylight hours annually.
Construction documents shall indicate the solar-ready zone.
The total solar-ready zone area shall be not less than 300 square feet (27.87 m2) exclusive of mandatory access or set back areas as required by the International Fire Code. New multiple single-family dwellings (townhouses) three stories or less in height above grade plane and with a total floor area less than or equal to 2,000 square feet (185.8 m2) per dwelling shall have a solar-ready zone area of not less than 150 square feet (13.94 m2). The solar-ready zone shall be composed of areas not less than 5 feet (1.52 m) in width and not less than 80 square feet (7.44 m2) exclusive of access or set back areas as required by the International Fire Code.
The structural design loads for roof dead load and roof live load shall be clearly indicated on the construction documents.
The main electrical service panel shall have a reserved space to allow installation of a dual pole circuit breaker for future solar electric installation and shall be labeled "For Future Solar Electric." The reserved space shall be positioned at the opposite (load) end from the input feeder location or main circuit location.