|Adopt Entire Chapter||X|
|Adopt Entire Chapter as amended (amended sections listed below)|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19, Division 1]|
|Chapter / Section|
In Group A, E, I or U occupancies, any amount of Class 3 and 4 unstable (reactive) materials shall be stored in accordance with the following:
In classrooms in Group B, F or M occupancies, any amount of Class 3 and 4 unstable (reactive) materials shall be stored in accordance with the following:
Indoor storage of unstable (reactive) materials in amounts exceeding the maximum allowable quantity per control area indicated in Table 5003.1.1(1) shall be in accordance with Sections 5001, 5003, 5004 and this chapter.
Unstable (reactive) materials stored in quantities greater than 500 cubic feet (14 m3) shall be separated into piles, each not larger than 500 cubic feet (14 m3). Aisle width shall not be less than the height of the piles or 4 feet (1219 mm), whichever is greater.
Exception: Materials stored in tanks.