|Adopt Entire Chapter|
|Adopt Entire Chapter as amended (amended sections listed below)||X|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19,Division 1]||X|
|Chapter / Section|
|[T-19 §3.05 (a)]||X|
|[T-19 §3.05 (b)]||X|
Approved fire apparatus access roads shall be provided for every facility, building or portion of a building hereafter constructed or moved into or within the jurisdiction. The fire apparatus access road shall comply with the requirements of this section and shall extend to within 150 feet (45 720 mm) of all portions of the facility and all portions of the exterior walls of the first story of the building as measured by an approved route around the exterior of the building or facility.
- 1.1. The building is equipped throughout with an approved automatic sprinkler system installed in accordance with Section 903.3.1.1, 903.3.1.2 or 903.3.1.3.
- 1.2. Fire apparatus access roads cannot be installed because of location on property, topography, waterways, nonnegotiable grades or other similar conditions, and an approved alternative means of fire protection is provided.
- 1.3. There are not more than two Group R-3 or Group U occupancies.
- Where approved by the fire code official, fire apparatus access roads shall be permitted to be exempted or modified for solar photovoltaic power generation facilities.
- Fire lanes shall have a minimum clear roadway width of 20 feet (6096 mm) when no parking is allowed on either side.
- Those portions of a fire lane which must accommodate the operation of Fire Department aerial ladder apparatus shall have a minimum clear roadway width of 28 feet (8534 mm) when no parking is allowed on either side.
- Those portions of a fire lane 30 feet (9144 mm) on either side of a private fire hydrant shall have a minimum clear roadway width of 28 feet (8534 mm). No parking shall be permitted within those portions of the roadway which are within 30 feet (9144 mm) of and on the same side of the roadway as a private fire hydrant.
- Where parking is allowed on only one side of a required fire lane, parking shall be on the same side of the roadway as the hydrants.
- Where parallel parking is allowed on either side of a fire lane, the roadway width shall be increased 8 feet (238 mm) for each parking lane.
- Where access requires accommodation of Fire Department apparatus, overhead clearance shall not be less than 14 feet (4267 mm).
- Deadend fire lanes shall terminate in cul-de-sacs or other approved turning areas consistent with the Department of Public Works Standard Street Dimension Plan D-22549.
- Fire lanes shall be paved to the city engineer's standards for public alleys.
Where required, gates and barricades shall be secured in an approved manner. Roads, trails and other accessways that have been closed and obstructed in the manner prescribed by Section 503.5 shall not be trespassed on or used unless authorized by the owner and the fire code official.
Exception: The restriction on use shall not apply to public officers acting within the scope of duty.
School grounds may be fenced and gates therein may be equipped with locks, provided that safe dispersal areas based on 3 square feet (0.28 m2) per occupant are located between the school and the fence. Such required safe dispersal areas shall not be located less than 50 feet (15 240 mm) from school buildings.
Every public and private school shall conform with Section 32020 of the Education Code which states:
The governing board of every public school district, and the governing authority of every private school, which maintains any building used for the instruction or housing of school pupils on land entirely enclosed (except for building walls) by fences of walls, shall, through cooperation with the local law enforcement and fire-protection agencies having jurisdiction of the area, make provision for the erection of gates in such fences or walls. The gates shall be of sufficient size to permit the entrance of the ambulances, police equipment and fire-fighting apparatus used by the law enforcement and fire-protection agencies. There shall be no less than one such access gate and there shall be as many such gates as needed to assure access to all major buildings and ground areas. If such gates are to be equipped with locks, the locking devices shall be designed to permit ready entrance by the use of the chain or bolt-cutting devices with which the local law enforcement and fire-protection agencies may be equipped.
Exterior doors and openings required by this code or the California Building Code shall be maintained readily accessible for emergency access by the fire department. An approved access walkway leading from fire apparatus access roads to exterior openings shall be provided when required by the fire code official.
[California Code of Regulations, Title 19, Division 1, §3.05(b)] Fire Department Access and Egress. (Roofs)
(b) Roofs. No person shall install or maintain any security barrier such as barbed wire fencing, razor wire fencing, chain link fencing, or any other fencing material, cable, aerial, antenna, or other obstruction on the roof of any commercial establishment in such a manner as to obstruct or render egress or access hazardous in the event of fire or other emergency.
Exception: Guy wire, rods and aerial antenna masts may be attached to a roof structure having a slope of less than 30 degrees provided there is full clearance of seven feet or more between the roof and said obstruction. Guy wire or rods required to support aerial or antenna masts may be attached to a roof structure a lateral distance from the mast not in excess of one-sixth the height of the mast.
No person shall install or maintain any security barrier such as barbed wire fencing, razor wire fencing, chain link fencing, or any other fencing material, cable, aerial, antenna, or other obstruction on the roof of any commercial establishment in such a manner as to obstruct or render egress or access hazardous in the event of fire or other emergency.
Exception: Guy wire, rods and aerial antenna masts may be attached to a roof structure having a slope of less than 30 degrees provided there is full clearance of 7 feet or more between the roof and said obstruction. Guy wire or rods required to support aerial or antenna masts may be attached to a roof structure a lateral distance from the mast not in excess of one-sixth the height of the mast.
- The height in inches of any number or letter therein shall be the sum of one-tenth (1/10) of the distance in feet of the number from the boundary of the property (upon which the building, structure, or parking lot is situated) abutting the street, plus two (2), providing that every number shall not be less than 4 inches (100 mm) in height.
- The overall width of any figure in or comprising the number or letter shall be one-half (1/2) of its height. The width of any portion of a figure in or comprising the number or letter shall be one-tenth (1/10) of its height.
- The key box shall be compatible with an existing rapid entry key box system in use in the jurisdiction and approved by the fire code official.
- The front cover shall be permanently labeled with the words "Fire Department Use Only—Elevator Keys."
- The key box shall be mounted at each elevator bank at the lobby nearest to the lowest level of fire department access.
- The key box shall be mounted 5 feet 6 inches (1676 mm) above the finished floor to the right side of the elevator bank.
- Contents of the key box are limited to fire service elevator keys. Additional elevator access tools, keys and information pertinent to emergency planning or elevator access shall be permitted where authorized by the fire code official.
- In buildings with two or more elevator banks, a single key box shall be permitted to be used where such elevator banks are separated by not more than 30 feet (9144 mm). Additional key boxes shall be provided for each individual elevator or elevator bank separated by more than 30 feet (9144 mm).
Exception: A single key box shall be permitted to be located adjacent to a fire command center or the nonstandard fire service elevator key shall be permitted to be secured in a key box used for other purposes and located in accordance with Section 506.1.
- Where street alignments mandate the installation of dead-end mains, the fire-flow in gallons per minute may be adjusted downward, depending on the type of land development.
- A minimum residual water pressure of 20 pounds per square inch (137.9 kPa) is to remain in the system with the required gallons per minute flowing.
|TYPE OF LAND DEVELOPMENT||FIRE-FLOW IN GALLONS PER MINUTE|
|Low density Residential||2,000 gpm from three adjacent fire
hydrants flowing simultaneously.
|High density Residential and
|4,000 gpm from four adjacent fire
hydrants flowing simultaneously.
|Industrial and Commercial||6,000 to 9,000 gpm from four to six
fire hydrants flowing simultaneously.
|High density Industrial and
Commercial (Principal business
districts or Centers)
|12,000 gpm available to any block
(where local conditions indicate
that consideration must be given to
simultaneous fires, and additional
2,000 to 8,000 gpm will be
- Every first story dwelling unit, first story guest room, and all first story portions of any commercial or industrial building must be within 300 feet (91 440 mm) of an approved fire hydrant.
- All fire hydrants shall have 2 1/2 inch by 4-inch (64 mm by100 mm) outlets or 4-inch by 4-inch (100 mm by 100 mm) outlets and conform to the minimum standards of the American Water Works Association for wet barrel hydrants. A minimum of one fire hydrant is to be provided at each intersection. "Built-up" type single 2 1/2-inch (64 mm) outlet hydrants [6-inch (1524 mm) pipe surmounted by an angle valve] shall be used in areas having a static water pressure of 210 psi or more.
- Streets with raised median center dividers, excessive traffic loads, or more than 80 feet (24 m) in dedicated width require the installation of hydrants on both sides of the street. Additional intermediate hydrants are required in areas where restricted access, depth of lots, or blocks exceeding the maximum hydrant spacing intervals exist.
|TYPE OF LAND
|150,000||600||2 1/2" × 4" Double
|100,000||300—450||2 1/2" × 4" Double
|80,000a||300||2 1/2" × 4" Double
Fire Hydrant or
4" x 4" Double
|40,000||300||4" × 4" Double
- This figure will be systematically reduced where greater fire-flow is required due to restricted access, depth of lots, length of blocks or additional hazards.
|LAND USEa||REQUIRED FIRE FLOW
|ENGINE CO.||TRUCK CO.|
|2,000 gpm from three
adjacent fire hydrants
|1 1/2 miles||2 mile|
|4,000 gpm from four
adjacent fire hydrants
|1 1/2 miles||2 mile|
|6,000 to 9,000 from
four to six fire hydrants
|1 mile||1 1/2 miles|
|12,000 available to any
block (where local conditions
consideration must be
given to simultaneous
fires, additional 2,000 to
8,000 will be required).
|3/4 mile||1 mile|
- Land use designations are contained in the community plan elements of the General Plan for the City of Los Angeles.
- The maximum response distances for both LAFD fire suppression companies (engine and truck) must be satisfied.
Where a portion of the facility or building hereafter constructed or moved into or within the jurisdiction is more than 400 feet (122 m) from a hydrant on a fire apparatus access road, as measured by an approved route around the exterior of the facility or building, on-site fire hydrants and mains shall be provided where required by the fire code official.
Exception: For Group R-3 and Group U occupancies, equiped throughout with an approved automatic sprinkler system installed in accordance with Section 903.3.1.1, 903.3.1.2 or 903.3.1.3, the distance requirement shall be not more than 600 feet (183 m).
Private fire service mains and water tanks shall be periodically inspected, tested and maintained in accordance with California Code of Regulations, Title 19, Division 1, Chapter 5.
Records of inspections, testing and maintenance shall be maintained.
- The emergency voice/alarm communication system control unit.
- The fire department communications system.
- Fire alarm system zoning annunciator panel required by Section 907.6.4.3.
- Annunciator unit visually indicating the location of the elevators and whether they are operational.
- Status indicators and controls for air distribution systems.
- The fire fighter's control panel required by Section 909.16 for smoke control systems installed in the building.
- Controls for unlocking stairway doors simultaneously.
- Sprinkler valve and water-flow detector display panels.
- Emergency and standby power status indicators.
- A telephone for fire department use with controlled access to the public telephone system.
- Fire pump status indicators.
- Schematic building plans indicating the typical floor plan and detailing the building core, means of egress, fire protection systems, fire-fighter air-replenishment systems, fire-fighting equipment and fire department access, and the location of fire walls, fire barriers, fire partitions, smoke barriers and smoke partitions.
- 13.1. General building information that includes: property name, address, the number of floors in the building above and below grade, use and occupancy classification (for mixed uses, identify the different types of occupancies on each floor) and the estimated building population during the day, night and weekend;
- 13.2. Building emergency contact information that includes: a list of the building's emergency contacts including but not limited to building manager, building engineer and their respective work phone number, cell phone number and e-mail address;
- 13.3. Building construction information that includes: the type of building construction including but not limited to floors, walls, columns and roof assembly;
- 13.4. Exit access stairway and exit stairway information that includes: number of exit access stairways and exit stairways in building; each exit access stairway and exit stairway designation and floors served; location where each exit access stairway and exit stairway discharges, interior exit stairways that are pressurized; exit stairways provided with emergency lighting; each exit stairway that allows reentry; exit stairways providing roof access; elevator information that includes: number of elevator banks, elevator bank designation, elevator car numbers and respective floors that they serve; location of elevator machine rooms, control rooms and control spaces; location of sky lobby; and location of freight elevator banks;
- 13.5. Building services and system information that includes: location of mechanical rooms, location of building management system, location and capacity of all fuel oil tanks, location of emergency generator and location of natural gas service;
- 13.6. Fire protection system information that includes: location of standpipes, location of fire pump room, location of fire department connections, floors protected by automatic sprinklers and location of different types of automatic sprinkler systems installed including but not limited to dry, wet and pre-action;
- 13.7. Hazardous material information that includes: location and quantity of hazardous material.
- Work table.
- Generator supervision devices, manual start and transfer features.
- Public address system, where specifically required by other sections of this code.
- Elevator fire recall switch in accordance with California Code of Regulations, Title 8, Division 1, Chapter 4, Subchapter 6, Elevator Safety Orders.
- Elevator emergency or standby power selector switch(es), where emergency or standby power is provided.
- A master switch for unlocking elevator lobby doors permitted by Section 1010.1.9.10.
Fire command centers shall not be used for the housing of any boiler, heating unit, generator, combustible storage, or similar hazardous equipment or storage.
509.3 Fire Protection Equipment Access for Sprinkler Valves, Standpipes, and Other Fire Protection Equipment
All new buildings shall have approved radio coverage for emergency responders within the building based upon the existing coverage levels of the public safety communication systems of the jurisdiction at the exterior of the building. This section shall not require improvement of the existing public safety communication systems.
- Where approved by the building official and the fire code official, a wired communication system in accordance with Section 907.2.13.2 shall be permitted to be installed or maintained instead of an approved radio coverage system.
- Where it is determined by the fire code official that the radio coverage system is not needed.
- In facilities where emergency responder radio coverage is required and such systems, components or equipment required could have a negative impact on the normal operations of that facility, the fire code official shall have the authority to accept an automatically activated emergency responder radio coverage system.
If used, signal boosters shall meet the following requirements:
- All signal booster components shall be contained in a National Electrical Manufacturer's Association (NEMA) 4-type waterproof cabinet.
- Battery systems used for the emergency power source shall be contained in a NEMA 4-type waterproof cabinet.
- The signal booster system and battery system shall be electrically supervised and monitored by a supervisory service, or when approved by the fire code official, shall sound an audible signal at a constantly attended location
- Equipment shall have FCC certification prior to installation.
The minimum qualifications of the system designer and lead installation personnel shall include both of the following:
- A valid FCC-issued general radio operators license.
- Certification of in-building system training issued by a nationally recognized organization, school or a certificate issued by the manufacturer of the equipment being installed.
These qualifications shall not be required where demonstration of adequate skills and experience satisfactory to the fire code official is provided.
Where an emergency responder radio coverage system is required, and upon completion of installation, the building owner shall have the radio system tested to verify that two-way coverage on each floor of the building is not less than 90 percent. The test procedure shall be conducted as follows:
- Each floor of the building shall be divided into a grid of 20 approximately equal test areas.
- The test shall be conducted using a calibrated portable radio of the latest brand and model used by the agency talking through the agency's radio communications system.
- Failure of not more than two nonadjacent test areas shall not result in failure of the test.
- In the event that three of the test areas fail the test, in order to be more statistically accurate, the floor shall be permitted to be divided into 40 equal test areas. Failure of not more than four nonadjacent test areas shall not result in failure of the test. If the system fails the 40-area test, the system shall be altered to meet the 90-percent coverage requirement.
- A test location approximately in the center of each test area shall be selected for the test, with the radio enabled to verify two-way communications to and from the outside of the building through the public agency's radio communications system. Once the test location has been selected, that location shall represent the entire test area. Failure in the selected test location shall be considered failure of that test area. Additional test locations shall not be permitted.
- The gain values of all amplifiers shall be measured and the test measurement results shall be kept on file with the building owner so that the measurements can be verified during annual tests. In the event that the measurement results become lost, the building owner shall be required to rerun the acceptance test to reestablish the gain values.
- As part of the installation a spectrum analyzer or other suitable test equipment shall be utilized to ensure spurious oscillations are not being generated by the subject signal booster. This test shall be conducted at the time of installation and subsequent annual inspections.
The emergency responder radio coverage system shall be inspected and tested annually or where structural changes occur including additions or remodels that could materially change the original field performance tests. Testing shall consist of the following:
- In-building coverage test as described in Section 510.5.3.
- Signal boosters shall be tested to verify that the gain is the same as it was upon initial installation and acceptance.
- Backup batteries and power supplies shall be tested under load of a period of 1 hour to verify that they will properly operate during an actual power outage. If within the 1-hour test period the battery exhibits symptoms of failure, the test shall be extended for additional 1-hour periods until the integrity of the battery can be determined.
- Other active components shall be checked to verify operation within the manufacturer's specifications.
- At the conclusion of the testing, a report, which shall verify compliance with Section 510.5.3, shall be submitted to the fire code official.
- By at least one publication in a newspaper of general circulation in the City, designated for the purpose of the City Clerk, not less than 10 days prior to the date of the hearing.
- By mailing written notice not less than 10 days prior to the date of such hearing, to the owners of all property within 300 feet (91 440 mm) of the boundaries of the proposed fire roads, firebreaks and fuelbreaks, or in those instances where existing fire roads, firebreaks and fuelbreaks are proposed to be widened within 300 feet (91 440 mm) of the new boundaries. Where all property within the 300-foot (91 440 mm) radius is under the same ownership as the property upon which the construction is proposed to be performed, the owners of all property adjoining that property in the same ownership as that involved in the proposed construction, or separated only by a street, alley, public right-of-way or other easement, shall also be notified in the same manner.
Section 512 Response Distances That if Exceeded Require the Installation of an Automatic Fire Sprinkler System
- Fire protective signaling systems which shall be installed in accordance with Chapter 9 of this article.
- Fire hydrants which shall be installed in accordance with Section 507.3.1 of this chapter, or as required by the Chief.
- Automatic fire extinguishing systems which shall be installed in accordance with, but not limited to, Chapter 9 of this article.
- Smoke removal systems which shall be designed for the hazard to be protected and shall be approved by the Chief.
- Standpipe systems which shall be installed in accordance with Chapter 9 of the LAMC (Plumbing Code).
- Systems or equipment not specified. The installation, arrangement of, or alteration thereto, of other fire protection equipment or systems which are deemed necessary to provide minimum fire protection as may be required by the Chief.