Heads up: There are no amended sections in this chapter.
The storage and use of corrosive materials shall be in accordance with this chapter. Compressed gases shall also comply with Chapter 53.
This section has been amended at the state or city level.
Outdoor storage of corrosive materials shall not be within 20 feet (6096 mm) of buildings not associated with the manufacturing or distribution of such materials, lot lines, public streets, public alleys, public ways or means of egress. A 2-hour fire barrier without openings or penetrations, and extending not less than 30 inches (762 mm) above and to the sides of the storage area, is allowed in lieu of such distance. The wall shall either be an independent structure, or the exterior wall of the building adjacent to the storage area.