The maximum amount of fuel oil stored above ground or inside of a building shall be 660 gallons (2498 L). The supply tank shall be supported on rigid noncombustible supports to prevent settling or shifting.
Exception: The storage of fuel oil, used for space or water heating, above ground or inside buildings in quantities exceeding 660 gallons (2498 L) shall comply with NFPA 31.
Exterior abovegrade fill piping shall be removed when tanks are abandoned or removed. Tank abandonment and removal shall be in accordance with the Florida Fire Prevention Code.