Branch-circuit and feeder conductors shall have ampacities not less than the maximum load to be served. Where a branch circuit or a feeder supplies continuous loads or any combination of continuous and noncontinuous loads, the minimum branch-circuit or feeder conductor size, before the application of any adjustment or correction factors, shall have an allowable ampacity equal to or greater than the noncontinuous load plus 125 percent of the continuous load.
The ungrounded and grounded circuit conductors of each multiwire branch circuit shall be grouped by cable ties or similar means in at least one location within the panelboard or other point of origination.
The voltage ratings of branch circuits that supply luminaires or receptacles for cord-and-plug-connected loads of up to 1,400 voltamperes or of less than 1/4 horsepower (0.186 kW) shall be limited to a maximum rating of 120 volts, nominal, between conductors.
Branch circuits that supply cord-and-plug-connected or permanently connected utilization equipment and appliances rated at over 1,440 volt-amperes or 1/4 horsepower (0.186 kW) and greater shall be rated at 120 volts or 240 volts, nominal.
1. It is cord- and attachment plug-connected.
2. The rating is not more than 40 amperes and 250 volts; single phase.
3. Total rated-load current is shown on the room air-conditioner nameplate rather than individual motor currents.
4. The rating of the branch-circuit short-circuit and ground-fault protective device does not exceed the ampacity of the branch-circuit conductors, or the rating of the branch-circuit conductors, or the rating of the receptacle, whichever is less.
The requirements for circuits having two or more outlets, or receptacles, other than the receptacle circuits of Sections E3703.2, E3703.3 and E3703.4, are summarized in Table E3702.13. Branch circuits in dwelling units shall supply only loads within that dwelling unit or loads associated only with that dwelling unit. Branch circuits installed for the purpose of lighting, central alarm, signal, communications or other purposes for public or common areas of a two-family dwelling shall not be supplied from equipment that supplies an individual dwelling unit.
BRANCH-CIRCUIT REQUIREMENTS-SUMMARYa, b
|15 amp||20 amp||30 amp|
Minimum size (AWG)
protection device rating
Receptacle rating (amperes)
|Any type 15 |
|Any type |
15 or 20
|Maximum load (amperes)||15||20||30|
A minimum of two 20-ampere-rated branch circuits shall be provided to serve all wall and floor receptacle outlets located in the kitchen, pantry, breakfast area, dining area or similar area of a dwelling. The kitchen countertop receptacles shall be served by a minimum of two 20-ampere-rated branch circuits, either or both of which shall also be permitted to supply other receptacle outlets in the same kitchen, pantry, breakfast and dining area including receptacle outlets for refrigeration appliances.
The minimum load in volt-amperes shall be calculated in accordance with the load calculation procedure prescribed in Table E3704.2(1). The associated table demand factors shall be applied to the actual load to determine the minimum load for feeders.
FEEDER LOAD CALCULATION
|LOAD CALCULATION PROCEDURE||APPLIED DEMAND FACTOR|
|Lighting and receptacles: A unit load of not less than 3 VA per square |
foot of total floor area shall constitute the lighting and 120-volt, 15-
and 20-ampere general use receptacle load. 1,500 VA shall be added
for each 20-ampere branch circuit serving receptacles in the kitchen,
dining room, pantry, breakfast area and laundry area.
|100 percent of first 3,000 VA or less and 35 percent of that in excess |
of 3,000 VA.
|Appliances and motors: The nameplate rating load of all fastened-in-|
place appliances other than dryers, ranges, air-conditioning and space-
|100 percent of load for three or less appliances.|
75 percent of load for four or more appliances.
|Fixed motors: Full-load current of motors plus 25 percent of the full load current of the largest motor.|
|Electric clothes dryer: The dryer load shall be 5,000 VA for each dryer circuit or the nameplate rating load of each dryer, whichever is greater.|
|Cooking appliances: The nameplate rating of ranges, wall-mounted |
ovens, counter-mounted cooking units and other cooking appliances
rated in excess of 1.75 kVA shall be summed.
|Demand factors shall be as allowed by Table E3704.2(2).|
|Plus the largest of either the heating or cooling load|
|Largest of the following two selections:|
1.100 percent of the nameplate rating(s) of the air conditioning and cooling, including heat pump compressors.
2.100 percent of the fixed electric space heating.
DEMAND LOADS FOR ELECTRIC RANGES, WALL-MOUNTED OVENS, COUNTER-MOUNTED
COOKING UNITS AND OTHER COOKING APPLIANCES OVER 13/4 kVA RATINGa, b
|NUMBER OF APPLIANCES||MAXIMUM DEMANDb, c||DEMAND FACTORS (percent)d|
|Column A |
maximum 12 kVA rating
|Column B |
less than 31/2 kVA rating
|Column C |
31/2 to 83/4 kVA rating
|CONDUCTOR TEMPERATURE RATING||CONDUCTOR |
|Copper||Aluminum or copper-clad aluminum|
For ambient temperatures other than 30°C (86°F), multiply the allowable ampacities specified in Table E3705.1 by the appropriate correction factor shown in Table E3705.2.
AMBIENT TEMPERATURE CORRECTION FACTORS
|For ambient temperatures other than 30°C (86°F), multiply the |
allowable ampacities specified in the ampacity tables
by the appropriate correction factor shown below.
|Temperature Rating of Conductor||Ambient |
|10 or less||1.29||1.20||1.15||50 or less|
Where the number of current-carrying conductors in a raceway or cable exceeds three, or where single conductors or multiconductor cables are stacked or bundled for distances greater than 24 inches (610 mm) without maintaining spacing and are not installed in raceways, the allowable ampacity of each conductor shall be reduced as shown in Table E3705.3.
1. Adjustment factors shall not apply to conductors in nipples having a length not exceeding 24 inches (610 mm).
2. Adjustment factors shall not apply to underground conductors entering or leaving an outdoor trench if those conductors have physical protection in the form of rigid metal conduit, intermediate metal conduit, or rigid nonmetallic conduit having a length not exceeding 10 feet (3048 mm) and the number of conductors does not exceed four.
3. Adjustment factors shall not apply to type AC cable or to type MC cable without an overall outer jacket meeting all of the following conditions:
4. An adjustment factor of 60 percent shall be applied to Type AC cable and Type MC cable where all of the following conditions apply:
CONDUCTOR PROXIMITY ADJUSTMENT FACTORS
|NUMBER OF CURRENT-CARRYING |
CONDUCTORS IN CABLE OR RACEWAY
|PERCENT OF VALUES IN |
|41 and above||35|
Except where the equipment is marked otherwise, termination provisions of equipment for circuits rated 100 amperes or less, or marked for 14 AWG through 1 AWG conductors, shall be used only for one of the following:
1. Conductors rated 60°C (140°F);
2. Conductors with higher temperature ratings, provided that the ampacity of such conductors is determined based on the 60°C (140°F) ampacity of the conductor size used;
3. Conductors with higher temperature ratings where the equipment is listed and identified for use with such conductors; or
4. For motors marked with design letters B, C, or D conductors having an insulation rating of 75°C (167°F) or higher shall be permitted to be used provided that the ampacity of such conductors does not exceed the 75°C (167°F) ampacity.
1. Conductors rated 75°C (167°F).
2. Conductors with higher temperature ratings provided that the ampacity of such conductors does not exceed the 75°C (167°F) ampacity of the conductor size used, or provided that the equipment is listed and identified for use with such conductors.
All ungrounded branch-circuit and feeder conductors shall be protected against overcurrent by an overcurrent device installed at the point where the conductors receive their supply. Overcurrent devices shall not be connected in series with a grounded conductor. Overcurrent protection and allowable loads for branch circuits and feeders that do not serve as the main power feeder to the dwelling unit load shall be in accordance with this chapter.
Branch-circuit conductors and equipment shall be protected by overcurrent protective devices having a rating or setting not exceeding the allowable ampacity specified in Table E3705.1 and Sections E3705.2, E3705.3 and E3705.4 except where otherwise permitted or required in Sections E3705.5.1 through E3705.5.3.
The next higher standard overcurrent device rating, above the ampacity of the conductors being protected, shall be permitted to be used, provided that all of the following conditions are met:
1. The conductors being protected are not part of a branch circuit supplying more than one receptacle for cord- and plug-connected portable loads.
2. The ampacity of conductors does not correspond with the standard ampere rating of a fuse or a circuit breaker without overload trip adjustments above its rating (but that shall be permitted to have other trip or rating adjustments).
3. The next higher standard device rating does not exceed 400 amperes.
|COPPER||ALUMINUM OR COPPER-CLAD |
|Maximum overcurrentprotection-device ratinga |
|Maximum overcurrentprotection-device ratinga |
Overcurrent devices shall:
1. Be readily accessible.
2. Not be located where they will be exposed to physical damage.
3. Not be located where they will be in the vicinity of easily ignitible material such as in clothes closets.
4. Not be located in bathrooms.
5. Not be located over steps of a stairway.
6. Be installed so that the center of the grip of the operating handle of the switch or circuit breaker, when in its highest position, is not more than 6 feet 7 inches (2007 mm) above the floor or working platform.