Where terms are not defined through the methods authorized by this section, such terms shall have ordinarily accepted meanings such as the context implies.
Moderately abrasive particulate in high concentrations, and highly abrasive particulate in moderate and high concentrations, such as alumina, bauxite, iron silicate, sand and slag. .
A . refrigerating system in which refrigerant is pressurized by pumping a chemical solution of refrigerant in absorbent, and then separated by the addition of heat in a generator, condensed (to reject heat), expanded, evaporated (to provide refrigeration), and reabsorbed in an absorber to repeat the cycle; the system may be single or multiple effect, the latter using multiple stages or internally cascaded use of heat to improve efficiency.
That which enables a device, (TO). appliance or equipment to be reached by ready access or by a means that first requires the removal or movement of a panel, door or similar obstruction [see also “Ready access (to)”].
AIR. All air supplied to mechanical equipment and appliances for combustion, ventilation, cooling and similar purposes. Standard air is air at standard temperature and pressure, namely, 70°F (21°C) and 29.92 inches of mercury (101.3 kPa).
Any diffuser system designed to both convey air within a room, space or area and diffuse air into that space while operating under positive pressure. Systems are commonly constructed of, but not limited to, fabric or plastic film. .
A blower or fan used for the purpose of distributing . supply air to a room, space or area.
Air moved from one indoor space to another. .
[A] A change in a . mechanical system that involves an extension, addition or change to the arrangement, type or purpose of the original installation.
A device or apparatus that is manufactured and designed to utilize energy and for which this code provides specific requirements. .
Any . appliance regulated by this code which was legally installed prior to the effective date of this code, or for which a permit to install has been issued.
Any . appliance in which the products of combustion at the point of entrance to the flue under normal operating conditions have a temperature of more than 1,000°F (538°C), but not greater than 2,000°F (1093°C).
An . appliance designed and installed in such a manner that all of the products of combustion are conveyed directly from the appliance to the outdoor atmosphere through an approved chimney or vent system.
[A] Acceptable to the . code official.
[A] An established and recognized agency that is regularly engaged in conducting tests or furnishing inspection services where such agency has been approved by the . code official.
A room containing a bathtub, shower, spa or similar bathing fixture. .
A closed heating . appliance intended to supply hot water or steam for space heating, processing or power purposes. Low-pressure boilers operate at pressures less than or equal to 15 pounds per square inch (psi) (103 kPa) for steam and 160 psi (1103 kPa) for water. High-pressure boilers operate at pressures exceeding those pressures.
Any vessel used for generating hot water to be used external to the vessel, which exceeds any of the following limitations: .
- A heat input capacity of 400,000 Btuh (117.2 kW).
- A water temperature of 210°F (99°C).
- A nominal water capacity of 120 gal (454 L).
A room primarily utilized for the installation of a . boiler.
A gas-tight joint obtained by the joining of metal parts with metallic mixtures or alloys which melt at a temperature above 1,000°F (538°C), but lower than the melting temperature of the parts to be joined. .
A metal joining process wherein coalescence is produced by the use of a nonferrous filler metal having a melting point above 1,000°F (538°C), but lower than that of the base metal being joined. The filler material is distributed between the closely fitted surfaces of the joint by capillary attraction. .
The region within an occupied space between planes 3 and 72 inches (76 and 1829 mm) above the floor and more than 2 feet (610 mm) from the walls of the space or from fixed air-conditioning . equipment.
BTU. Abbreviation for British thermal unit, which is the quantity of heat required to raise the temperature of 1 pound (454 g) of water 1°F (0.56°C) (1 Btu = 1055 J).
[A] Any structure occupied or intended for supporting or sheltering any . occupancy.
[BF] A . listed device installed in a ceiling membrane of a fire-resistance-rated floor/ceiling or roof/ceiling assembly to limit automatically the radiative heat transfer through an air inlet/outlet opening.
A field-constructed . chimney composed of solid masonry units, bricks, stones or concrete.
A field-constructed . chimney of metal.
A heat-producing . appliance that employs a combustion chamber that does not have openings other than the flue collar, fuel charging door and adjustable openings provided to control the amount of combustion air that enters the combustion chamber.
An . appliance used to dry wet laundry by means of heat.
[A] These regulations, subsequent amendments thereto, or any emergency rule or regulation that the administrative authority having jurisdiction has lawfully adopted. .
[A] The officer or other designated authority charged with the administration and enforcement of this code, or a duly authorized representative. .
[BF] A . listed device installed in ducts and air transfer openings designed to close automatically upon the detection of heat and resist the passage of flame and smoke. The device is installed to operate automatically, be controlled by a smoke detection system, and where required, is capable of being positioned from a fire command center.
Wall, floor, ceiling or other assembly constructed of one or more component materials that are not defined as noncombustible. .
Class II. Liquids having a closed cup flash point at or above 100°F (38°C) and below 140°F (60°C).
Class IIIA. Liquids having a closed cup flash point at or above 140°F (60°C) and below 200°F (93°C).
Class IIIB. Liquids having a closed cup flash point at or above 200°F (93°C).
The category of combustible liquids does not include compressed gases or cryogenic fluids.
Any material not defined as noncombustible. .
In the context of this code, refers to the rapid oxidation of fuel accompanied by the production of heat or heat and light. .
. Appliances used in a commercial food service establishment for heating or cooking food and which produce grease vapors, steam, fumes, smoke or odors that are required to be removed through a local exhaust ventilation system. Such appliances include deep fat fryers; upright broilers; griddles; broilers; steam-jacketed kettles; hot-top ranges; under-fired broilers (charbroilers); ovens; barbecues; rotisseries; and similar appliances. For the purpose of this definition, a food service establishment shall include any building or a portion thereof used for the preparation and serving of food.
Self-contained system consisting of the exhaust . hood, the cooking equipment, the filters and the fire suppression system. The system is designed to capture cooking vapors and residues generated from commercial cooking equipment. The system removes contaminants from the exhaust air and recirculates the air to the space from which it was withdrawn.
A . backshelf hood is also referred to as a low-proximity hood, or as a sidewall hood where wall mounted. Its front lower lip is low over the appliance(s) and is “set back” from the front of the appliance(s). It is always closed to the rear of the appliances by a panel where free-standing, or by a panel or wall where wall mounted, and its height above the cooking surface varies. (This style of hood can be constructed with partial end panels to increase its effectiveness in capturing the effluent generated by the cooking operation).
A . double island canopy hood is placed over back-to-back appliances or appliance lines. It is open on all sides and overhangs both fronts and the sides of the appliance(s). It could have a wall panel between the backs of the appliances. (The fact that exhaust air is drawn from both sides of the double canopy to meet in the center causes each side of this hood to emulate a wall canopy hood, and thus it functions much the same with or without an actual wall panel between the backs of the appliances).
An . eyebrow hood is mounted directly to the face of an appliance, such as an oven and dishwasher, above the opening(s) or door(s) from which effluent is emitted, extending past the sides and overhanging the front of the opening to capture the effluent.
A . single island canopy hood is placed over a single appliance or appliance line. It is open on all sides and overhangs the front, rear and sides of the appliance(s). A single island canopy is more susceptible to cross drafts and requires a greater exhaust air flow than an equivalent sized wall-mounted canopy to capture and contain effluent generated by the cooking operation(s).
A wall canopy exhaust . hood is mounted against a wall above a single appliance or line of appliance(s), or it could be free-standing with a back panel from the rear of the appliances to the hood. It overhangs the front and sides of the appliance(s) on all open sides.
The wall acts as a back panel, forcing the makeup air to be drawn across the front of the cooking equipment, thus increasing the effectiveness of the hood to capture and contain effluent generated by the cooking operation(s).
. Compensating hoods are those having integral (built-in) makeup air supply. The makeup air supply for such hoods is generally supplied from: short-circuit flow from inside the hood, air curtain flow from the bottom of the front face, and front face discharge from the outside front wall of the hood. The compensating makeup airflow can also be supplied from the rear or side of the hood, or the rear, front or sides of the cooking equipment. The makeup airflow can be one or a combination of methods.
A specific machine, with or without accessories, for compressing a gas. .
A . compressor in which increase in pressure is attained by changing the internal volume of the compression chamber.
A . compressor with its prime mover and accessories.
A location that cannot be accessed without damaging permanent parts of the building structure or finish surface. Spaces above, below or behind readily removable panels or doors shall not be considered as concealed. .
The liquid that condenses from a gas (including . flue gas) caused by a reduction in temperature.
A specific refrigerating machine combination for a given . refrigerant, consisting of one or more power-driven compressors, condensers and, where required, liquid receivers, and the regularly furnished accessories.
An area, room or space that is enclosed within the building thermal envelope and that is directly heated or cooled or that is indirectly heated or cooled. Spaces are indirectly heated or cooled where they communicate through openings with . conditioned spaces, where they are separated from conditioned spaces by uninsulated walls, floors or ceilings, or where they contain uninsulated ducts, piping or other sources of heating or cooling.
[A] The written, graphic and pictorial documents prepared or assembled for describing the design, location and physical characteristics of the elements of the project necessary for obtaining a building permit. The construction drawings shall be drawn to an appropriate scale. .
A manual or automatic device designed to regulate the gas, air, water or electrical supply to, or operation of, a . mechanical system.
A burner designed to supply gaseous fuel to an . appliance originally designed to utilize another fuel.
See “ . Commercial cooking appliances.”
A device that, where installed, will restrict, retard or direct the flow of air in a . duct, or the products of combustion in a heat-producing appliance, its vent connector, vent or chimney therefrom.
[BS] The elevation of the “design flood,” including wave height, relative to the datum specified on the community’s legally designated flood hazard area map. In areas designated as . Zone AO, the design flood elevation shall be the elevation of the highest existing grade of the building’s perimeter plus the depth number, in feet, specified on the flood hazard map. In areas designated as Zone AO where a depth number is not specified on the map, the depth number shall be taken as being equal to 2 feet (610 mm).
The maximum allowable working pressure for which a specific part of a system is designed. .
Products that are noncontinuous, individual, distinct pieces such as, but not limited to, electrical, plumbing and mechanical products and . duct straps, duct fittings, duct registers and pipe hangers.
The pressure difference existing between the . appliance or any component part and the atmosphere, that causes a continuous flow of air and products of combustion through the gas passages of the appliance to the atmosphere.
Dry cleaning plants or systems are classified as follows: .
Those systems using Class I flammable liquid solvents having a . flash point below 100°F (38°C).
Those systems using Class IV nonflammable liquid solvents. .
A tube or conduit utilized for conveying air. The air passages of self-contained systems are not to be construed as air . ducts.
A warm-air . furnace normally installed in an air distribution duct to supply warm air for heating. This definition shall apply only to a warm-air heating appliance that, for air circulation, depends on a blower not furnished as part of the furnace.
A heating and cooling system that is comprised of one or multiple indoor . evaporator/air-handling units and an outdoor condensing unit that is connected by refrigerant piping and electrical wiring. A ductless mini-split system is capable of cooling or heating one or more rooms without the use of a traditional ductwork system.
[BG] A building or portion thereof that contains not more than two . dwelling units.
[BG] A single unit providing complete, independent living facilities for one or more persons, including permanent provisions for living, sleeping, eating, cooking and sanitation. .
Systems that employ air-to-air . heat exchangers to recover energy from or reject energy to exhaust air for the purpose of pre-heating, pre-cooling, humidifying or dehumidifying outdoor ventilation air prior to supplying such air to a space, either directly or as part of an HVAC system.
Air that is conveyed to or from occupied areas through . ducts which are not part of the heating or air-conditioning system, such as ventilation for human usage, domestic kitchen range exhaust, bathroom exhaust, domestic clothes dryer exhaust and parking garage exhaust.
All . piping, ducts, vents, control devices and other components of systems other than appliances which are permanently installed and integrated to provide control of environmental conditions for buildings. This definition shall also include other systems specifically regulated in this code.
Any . equipment regulated by this code which was legally installed prior to the effective date of this code, or for which a permit to install has been issued.
A device used for reducing the sensible heat of air for cooling by the process of evaporation of water into an airstream. .
The . equipment and appliances intended or installed for the purpose of environmental cooling by an evaporative cooler from which the conditioned air is distributed through ducts or plenums to the conditioned area.
That part of the system in which liquid . refrigerant is vaporized to produce refrigeration.
Uncontrolled outward air leakage from . conditioned spaces through unintentional openings in ceilings, floors and walls to unconditioned spaces or the outdoors caused by pressure differences across these openings resulting from wind, the stack effect created by temperature differences between indoors and outdoors, and imbalances between supply and exhaust airflow rates.
[BF] A . listed device installed in ducts and air transfer openings designed to close automatically upon detection of heat and to restrict the passage of flame. Fire dampers are classified for use in either static systems that will automatically shut down in the event of a fire, or in dynamic systems that continue to operate during a fire. A dynamic fire damper is tested and rated for closure under elevated temperature airflow.
A field-constructed . fireplace composed of solid masonry units, bricks, stones or concrete.
A free-standing . chimney-connected solid-fuel-burning heater, designed to be operated with the fire chamber doors in either the open or closed position.
[FG] A device that will automatically shut off the fuel supply to a main burner or group of burners when the means of ignition of such burners becomes inoperative, and when flame failure occurs on the burner or group of burners. .
[BF] The numerical value assigned to a material tested in accordance with ASTM E84 or UL 723. .
. Refrigerants shall be assigned to one of the three classes—1, 2 or 3—in accordance with ASHRAE 34. For Classes 2 and 3, the heat of combustion shall be calculated assuming that combustion products are in the gas phase and in their most stable state.
Class 1. Refrigerants that do not show flame propagation when tested in air at 14.7 psia (101 kPa) and 140°F (60°C).
Class 2. Refrigerants having a lower flammability limit (LFL) of more than 0.00625 pound per cubic foot (0.10 kg/m3) at 140°F (60°C) and 14.7 psia (101 kPa) and a heat of combustion of less than 8169 Btu/lb (19 000 kJ/kg).
Class 3. Refrigerants that are highly flammable, having a LFL of less than or equal to 0.00625 pound per cubic foot (0.10 kg/m3) at 140°F (60°C) and 14.7 psia (101 kPa) or a heat of combustion greater than or equal to 8169 Btu/lb (19 000 kJ/kg).
[F] Any liquid that has a . flash point below 100°F (38°C), and has a vapor pressure not exceeding 40 psia (276 kPa) at 100°F (38°C). Flammable liquids shall be known as Class I liquids and shall be divided into the following classifications:
Class IA. Liquids having a flash point below 73°F (23°C) and a boiling point below 100°F (38°C).
Class IB. Liquids having a flash point below 73°F (23°C) and a boiling point at or above 100°F (38°C).
Class IC. Liquids having a flash point at or above 73°F (23°C) and below 100°F (38°C).
[F] Mixtures of gases in air at concentrations equal to or greater than the LFL and less than or equal to the upper . flammability limit (UFL).
[F] The minimum temperature corrected to a pressure of 14.7 psia (101 kPa) at which the application of a test flame causes the vapors of a portion of the sample to ignite under the conditions specified by the test procedures and apparatus. The . flash point of a liquid shall be determined in accordance with ASTM D56, ASTM D93 or ASTM D3278.
A conduit for transferring air between an air . duct or plenum and an air terminal unit or between an air duct or plenum and an air inlet or air outlet. Such conduit is limited in its use, length and location.
The actual occupied area, not including unoccupied accessory areas or thicknesses of walls. .
[FG] A completely self-contained . furnace suspended from the floor of the space being heated, taking air for combustion from outside such space and with means for observing flames and lighting the appliance from such space.
A system or material used to form the inside surface of a (LINING). flue in a chimney or vent, for the purpose of protecting the surrounding structure from the effects of combustion products and conveying combustion products without leakage to the atmosphere.
[FG] A natural gas, manufactured gas, liquefied petroleum gas or a mixture of these. .
Kerosene or any hydrocarbon oil having a . flash point not less than 100°F (38°C).
A completely self-contained heating unit that is designed to supply heated air to spaces remote from or adjacent to the . appliance location.
A device arranged to relieve pressure by operation of a fusible member at a predetermined temperature. .
. Piping buried in horizontal or vertical excavations or placed in a body of water for the purpose of transporting heat transfer liquid to and from a heat pump. Included in this definition are closed loop systems in which the liquid is recirculated and open loop systems in which the liquid is drawn from a well or other source.
Any location considered to be a fire hazard for flammable vapors, dust, combustible fibers or other highly combustible substances. The location is not necessarily categorized in the Florida Building Code, Building as a high-hazard use group classification. .
A device that transfers heat from one medium to another. .
A refrigeration system that extracts heat from one substance and transfers it to another portion of the same substance or to a second substance at a higher temperature for a beneficial purpose. .
The operating or thermal storage liquid in a . mechanical system, including water or other liquid base, and additives at the concentration present under operating conditions used to move heat from one location to another. Refrigerants are not included as heat transfer liquids.
Heavy-duty cooking . appliances include electric under-fired broilers, electric chain (conveyor) broilers, gas under-fired broilers, gas chain (conveyor) broilers, gas open-burner ranges (with or without oven), electric and gas wok ranges, smokers, smoker ovens, and electric and gas over-fired (upright) broilers and salamanders.
A refrigeration system in which the basic design or the location of components is such that a leakage of . refrigerant from a failed connection, seal or component will enter an occupancy classified area, other than the machinery room.
An air intake device used to capture by entrapment, impingement, adhesion or similar means, grease, moisture, heat and similar contaminants before they enter a . duct system.
[FG] A self-contained package or factory-matched packages of integrated systems for generating gaseous hydrogen. . Hydrogen generating appliances utilize electrolysis, reformation, chemical, or other processes to generate hydrogen.
A flame, spark or hot surface capable of igniting flammable vapors or fumes. Such sources include . appliance burners, burner ignitors and electrical switching devices.
[F] The concentration of airborne contaminants that poses a threat of death, immediate or delayed permanent adverse health effects, or effects that could prevent escape from such an environment. This contaminant concentration level is established by the National Institute of Occupational Safety and Health (NIOSH) based on both (IDLH). toxicity and flammability. It is generally expressed in parts per million by volume (ppm v/v) or milligrams per cubic meter (mg/m3).
A system in which a secondary coolant cooled or heated by the . refrigerating system is circulated to the air or other substance to be cooled or heated. Indirect systems are distinguished by the following methods of application:
A system in which a secondary fluid is either cooled or heated by the . refrigerating system and then circulated within a closed circuit in indirect contact with the air or other substance to be cooled or heated.
A system in which the secondary substance for an indirect . open-spray system is heated or cooled by an intermediate coolant circulated from a second enclosure.
A system in which a secondary coolant is cooled or heated by the . refrigerating system and then circulated in direct contact with the air or other substance to be cooled or heated.
A system in which a secondary coolant is cooled or heated by the . refrigerating system and then passed through a closed circuit in the air or other substance to be cooled or heated, except that the evaporator or condenser is placed in an open or appropriately vented tank.
Uncontrolled inward air leakage to . conditioned spaces through unintentional openings in ceilings, floors and walls from unconditioned spaces or the outdoors caused by pressure differences across these openings resulting from wind, the stack effect created by temperature differences between indoors and outdoors, and imbalances between supply and exhaust airflow rates.
A device actuated by another device with which it is directly associated, to govern succeeding operations of the same or allied devices. A circuit in which a given action cannot occur until after one or more other actions have taken place. .
A joint made by bolting together a pair of flanged ends. .
A metal-to-metal compression joint in which a conical spread is made on the end of a tube that is compressed by a flare nut against a mating flare. .
A joint made in thermoset plastic . piping by the use of an adhesive substance which forms a continuous bond between the mating surfaces without dissolving either one of them.
A joint made in thermoplastic . piping by heating the parts sufficiently to permit fusion of the materials when the parts are pressed together.
A joint made in thermoplastic . piping by the use of a solvent or solvent cement which forms a continuous bond between the mating surfaces.
A gas-tight joint obtained by the joining of metal parts with metallic mixtures of alloys which melt at temperatures between 400°F (204°C) and 1,000°F (538°C). .
A gas-tight joint obtained by the joining of metal parts in molten state. .
[A] . Equipment, materials or products to which have been affixed a label, seal, symbol or other identifying mark of a nationally recognized testing laboratory, inspection agency or other organization concerned with product evaluation that maintains periodic inspection of the production of the above-labeled items and whose labeling indicates either that the equipment, material or product meets identified standards or has been tested and found suitable for a specified purpose.
Light-duty cooking . appliances include gas and electric ovens (including standard, bake, roasting, revolving, retherm, convection, combination convection/steamer, countertop conveyorized baking/finishing, deck and pastry), electric and gas steam-jacketed kettles, electric and gas pasta cookers, electric and gas compartment steamers (both pressure and atmospheric) and electric and gas cheesemelters.
[FG] A device responsive to changes in pressure, temperature or level for turning on, shutting off or throttling the gas supply to an . appliance.
[A] . Equipment, materials, products or services included in a list published by an organization acceptable to the code official and concerned with evaluation of products or services that maintains periodic inspection of production of listed equipment or materials or periodic evaluation of services and whose listing states either that the equipment, material, product or service meets identified standards or has been tested and found suitable for a specified purpose.
Space within a . dwelling unit utilized for living, sleeping, eating, cooking, bathing, washing and sanitation purposes.
See “LFL.” (LEL).
A . boiler furnishing hot water at pressures not exceeding 160 psi (1103 kPa) and at temperatures not exceeding 250°F (121°C).
A . boiler furnishing steam at pressures not exceeding 15 psi (103 kPa).
A refrigeration system in which the basic design or the location of components is such that a leakage of . refrigerant from a failed connection, seal or component will not enter an occupancy-classified area, other than the machinery room.
A room meeting prescribed safety requirements and in which refrigeration systems or components thereof are located (see Sections . 1105 and 1106).
A . venting system designed to remove flue or vent gases by mechanical means, that consists of an induced-draft portion under nonpositive static pressure or a forced-draft portion under positive static pressure.
A system for removing air from a room or space by mechanical means. .
- A connection between pipes, fittings, or pipes and fittings that is not welded, brazed, caulked, soldered, solvent cemented or heat fused.
- A general form of gas or liquid-tight connections obtained by the joining of parts through a positive holding mechanical construction such as, but not limited to, flanged, screwed, clamped or flared connections.
Medium-duty cooking . appliances include electric discrete element ranges (with or without oven), electric and gas hot-top ranges, electric and gas griddles, electric and gas double-sided griddles, electric and gas fryers (including open deep fat fryers, donut fryers, kettle fryers and pressure fryers), electric and gas conveyor pizza ovens, electric and gas tilting skillets (braising pans) and electric and gas rotisseries.
A steam or hot-water-heating assembly consisting of a group of individual . boilers called modules intended to be installed as a unit without intervening stop valves. Modules are under one jacket or are individually jacketed. The individual modules shall be limited to a maximum input rating of 400,000 Btu/h (117 228 W) gas, 3 gallons per hour (gph) (11.4 L/h) oil, or 115 kW (electric).
The movement of air into and out of a space through intentionally provided openings, such as windows and doors, or through nonpowered ventilators. .
The floor area of an . occupiable space defined by the inside surfaces of its walls but excluding shafts, column enclosures and other permanently enclosed, inaccessible and unoccupiable areas. Obstructions in the space such as furnishings, display or storage racks and other obstructions, whether temporary or permanent, shall not be deducted from the space area.
Nonabrasive particulate in high concentrations, moderately abrasive particulate in low and moderate concentrations, and highly abrasive particulate in low concentrations, such as alfalfa, asphalt, plaster, gypsum and salt. .
Materials that, when tested in accordance with ASTM E136, have at least three of four specimens tested meeting all of the following criteria: .
- The recorded temperature of the surface and interior thermocouples shall not at any time during the test rise more than 54°F (30°C) above the furnace temperature at the beginning of the test.
- There shall not be flaming from the specimen after the first 30 seconds.
- If the weight loss of the specimen during testing exceeds 50 percent, the recorded temperature of the surface and interior thermocouples shall not at any time during the test rise above the furnace air temperature at the beginning of the test, and there shall not be flaming of the specimen.
[A] The purpose for which a building, or portion thereof, is utilized or occupied. .
The timeweighted average (TWA) concentration for a normal eighthour workday and a 40-hour workweek to which nearly all workers can be repeatedly exposed without adverse effect, based on the OSHA PEL, ACGIH TLV-TWA, AIHA WEEL, or consistent value. (OEL).
An enclosed space intended for human activities, excluding those spaces intended primarily for other purposes, such as storage rooms and .equipment rooms, that are only intended to be occupied occasionally and for short periods of time.
Air taken from the outdoors, and therefore not previously circulated through the system. .
A door, window, louver or skylight openable to the outdoor atmosphere. .
A method of radiant space heating in which heat is supplied by large heated areas of room surfaces. The heating element usually consists of warm water . piping, warm air ducts, or electrical resistance elements embedded in or located behind ceiling, wall or floor surfaces.
A rigid conduit of iron, steel, copper, brass or plastic. .
Semirigid conduit of copper, aluminum, plastic or steel. .
A plastic that is capable of being repeatedly softened by increase of temperature and hardened by decrease of temperature. .
A plastic that is capable of being changed into a substantially infusible or insoluble product when cured under application of heat or chemical means. .
A fuel cell generator of electricity, which is not fixed in place. A portable fuel cell . appliance utilizes a cord and plug connection to a grid-isolated load and has an integral fuel supply.
See “ . Boiler.”
[A] A lot, plot or parcel of land, including any structure thereon. .
A permanent . mechanical joint incorporating an elastomeric seal or an elastomeric seal and corrosion-resistant grip ring. The joint is made with a pressing tool and jaw or ring approved by the fitting manufacturer.
A test performed in the field to prove system tightness. .
A pressure-responsive mechanism designed to stop automatically the operation of the pressure-imposing element at a predetermined pressure. .
A pressure-actuated valve or rupture member designed to relieve excessive pressure automatically. .
A pressure-actuated valve held closed by a spring or other means and designed to relieve pressure automatically in excess of the device’s setting. .
Closed containers, tanks or vessels that are designed to contain liquids or gases, or both, under pressure. .
Any . refrigerant-containing receptacle in a refrigerating system. This does not include evaporators where each separate section does not exceed 0.5 cubic foot (0.014 m3) of refrigerant-containing volume, regardless of the maximum inside dimensions, evaporator coils, controls, headers, pumps and piping.
CLEARANCE). Any noncombustible assembly that is (REDUCED labeled or constructed in accordance with Table 308.4.2 and is placed between combustible materials or assemblies and mechanical appliances, devices or equipment, for the purpose of reducing required airspace clearances. Protective assemblies attached directly to a combustible assembly shall not be considered as part of that combustible assembly.
To clear of air, water or other foreign substances. .
A type of . mechanical joint consisting of elastomeric seals and corrosion-resistant tube grippers. Such joints are permanent or removable depending on the design.
A valve that opens completely by fast action, either manually or automatically controlled. A valve requiring one-quarter round turn or less is considered to be quick opening. .
A heater designed to transfer heat primarily by direct radiation. .
. Refrigerants reprocessed to the same specifications as for new refrigerants by means including distillation. Such refrigerants have been chemically analyzed to verify that the specifications have been met. Reclaiming usually implies the use of processes or procedures that are available only at a reprocessing or manufacturing facility.
. Refrigerants removed from a system in any condition without necessarily testing or processing them.
. Refrigerants from which contaminants have been reduced by oil separation, removal of noncondensable gases, and single or multiple passes through devices that reduce moisture, acidity and particulate matter, such as replaceable core filter driers. These procedures usually are performed at the field job site or in a local service shop.
A substance utilized to produce refrigeration by its expansion or vaporization. .
Groupings that indicate the . toxicity and flammability classes in accordance with Section 1103.1. The classification group is made up of a letter (A or B) that indicates the toxicity class, followed by a number (1, 2 or 3) that indicates the flammability class. Refrigerant blends are similarly classified, based on the compositions at their worst cases of fractionation, as separately determined for toxicity and flammability. In some cases, the worst case of fractionation is the original formulation.
See “ . Flammability classification.”
See “ . Toxicity classification.”
A room or space in which an . evaporator or brine coil is located for the purpose of reducing or controlling the temperature within the room or space to below 68°F (20°C).
Expressed as 1 horsepower (0.75 kW), 1 ton or 12,000 Btu/h (3.5 kW), shall all mean the same quantity. .
See “ . Machinery room.”
A system in which the . evaporator is in direct contact with the material or space refrigerated, or is located in air-circulating passages communicating with such spaces.
A system in which a brine coil cooled by the . refrigerant is circulated to the material or space refrigerated, or is utilized to cool the air so circulated. Indirect systems are distinguished by the type or method of application.
Refrigeration systems are classified according to the degree of probability that leaked . refrigerant from a failed connection, seal or component will enter an occupied area. The distinction is based on the basic design or location of the components.
A combination of interconnected refrigeration-containing parts constituting one closed . refrigerant circuit in which a refrigerant is circulated for the purpose of extracting heat and in which a compressor is used for compressing the refrigerant vapor.
A complete factory-assembled and tested system that is shipped in one or more sections and that does not have . refrigerant-containing parts that are joined in the field by other than companion or block valves.
[A] An individual who is registered or licensed to practice their respective design profession as defined by the statutory requirements of the professional registration laws of the state or jurisdiction in which the project is to be constructed. .
Air removed from an . approved conditioned space or location and recirculated or exhausted.
An assembly of connected . ducts, plenums, fittings, registers and grilles through which air from the space or spaces to be heated or cooled is conducted back to the supply unit (see also “Supply air system”).
[FG] A free-standing heating unit burning solid or liquid fuel for direct heating of the space in and adjacent to that in which the unit is located. .
A valve that relieves pressure in a steam . boiler by opening fully at the rated discharge pressure. The valve is of the spring-pop type.
Complete, factory-assembled and tested, heating, air-conditioning or refrigeration . equipment installed as a single unit, and having all working parts, complete with motive power, in an enclosed unit of said machinery.
[BF] An enclosed space extending through one or more . stories of a building, connecting vertical openings in successive floors, or floors and the roof.
[BF] The walls or construction forming the boundaries of a . shaft.
[BG] A room or space in which people sleep, which can also include permanent provisions for living, eating, and either sanitation or kitchen facilities but not both. Such rooms and spaces that are also part of a . dwelling unit are not sleeping units.
[BF] A . listed device installed in ducts and air transfer openings designed to resist the passage of smoke. The device is installed to operate automatically, controlled by a smoke detection system, and where required, is capable of being positioned from a fire command center.
[BF] A numerical value assigned to a material tested in accordance with ASTM E84. .
Applicable to commercial food service operations only, (COOKING APPLICATIONS). solid fuel is any bulk material such as hardwood, mesquite, charcoal or briquettes that is combusted to produce heat for cooking operations.
A . mechanical exhaust system designed and constructed to capture air contaminants at their source and to exhaust such contaminants to the outdoor atmosphere.
[FG] A self-contained package or factory-matched packages which constitute an automatically operated assembly of integrated systems for generating useful electrical energy and recoverable thermal energy that is permanently connected and fixed in place. .
A . boiler operated at pressures not exceeding 15 psi (103 kPa) for steam.
A shutoff valve for controlling the flow of liquid or gases. .
[BG] That portion of a building included between the upper surface of a floor and the upper surface of the floor next above, except that the topmost . story shall be that portion of a building included between the upper surface of the topmost floor and the ceiling or roof above.
The highest stress level that the component will tolerate without rupture. .
That air delivered to each or any space supplied by the . air distribution system or the total air delivered to all spaces supplied by the air distribution system, which is provided for ventilating, heating, cooling, humidification, dehumidification and other similar purposes.
An assembly of connected . ducts, plenums, fittings, registers and grilles through which air, heated or cooled, is conducted from the supply unit to the space or spaces to be heated or cooled (see also “Return air system”).
The exact amount of air required to supply oxygen for complete . combustion of a given quantity of a specific fuel.
THERMAL RESISTANCE (R). A measure of the ability to retard the flow of heat. The R-value is the reciprocal of thermal conductance.
[P] Certification obtained by the manufacturer indicating that the function and performance characteristics of a product or material have been determined by testing and ongoing surveillance by an approved . third-party certification agency. Assertion of certification is in the form of identification in accordance with the requirements of the third-party certification agency.
[P] Procedure by which an approved testing laboratory provides documentation that a product, material or system conforms to specified requirements. .
The time-weighted average concentration of a . refrigerant or other chemical in air for a normal 8-hour workday and a 40-hour workweek, to which nearly all workers are repeatedly exposed, day after day, without adverse effects, as adopted by the American Conference of Government Industrial Hygienists (ACGIH).
A room containing a water closet and, frequently, a lavatory, but not a bathtub, shower, spa or similar bathing fixture. .
Class B. Refrigerants that have an OEL of less than 400 ppm.
An adapter for joining plastic . pipe to steel pipe. The purpose of this fitting is to provide a permanent, pressure-tight connection between two materials which cannot be joined directly one to another.
A . pipe or other conduit composed of factory-made components, containing a passageway for conveying combustion products and air to the atmosphere, listed and labeled for use with a specific type or class of appliance.
A device intended for installation in the . venting system, in the outlet of an individual automatically operated fuel-burning appliance that is designed to open the venting system automatically when the appliance is in operation and to close off the venting system automatically when the appliance is in a standby or shutdown condition.
The natural or mechanical process of supplying conditioned or unconditioned air to, or removing such air from, any space. .
A continuous open passageway from the . flue collar of an appliance to the outdoor atmosphere for the purpose of removing flue or vent gases. A venting system is usually composed of a vent or a chimney and vent connector, if used, assembled to form the open passageway.
One . occupiable space or several occupiable spaces with similar occupancy classification (see Table 403.3.1.1), occupant density, zone air distribution effectiveness and zone primary airflow rate per unit area.