Heads up: There are no amended sections in this chapter.
Ripening processes where ethylene gas is introduced into a room to promote the ripening of fruits, vegetables and other crops shall comply with this chapter.
Exception: Mixtures of ethylene and one or more inert gases in concentrations which prevent the gas from reaching greater than 25 percent of the lower explosive limit (LEL) when released to the atmosphere.
Words and terms used in this chapter and defined in Chapter 2 shall have the meanings ascribed to them as defined therein.
Ethylene gas shall be discharged only into approved rooms or enclosures designed and constructed for this purpose.
Valves controlling discharge of ethylene shall provide positive and fail-closed control of flow and shall be set to limit the concentration of gas in air below 1,000 parts per million (ppm).
Sources of ignition shall be controlled or protected in accordance with this section and Chapter 3.
Containers, piping and equipment used to dispense ethylene shall be bonded and grounded to prevent the discharge of static sparks or arcs.
This section has been amended at the state or city level.
Heating shall be by indirect means utilizing low-pressure steam, hot water or warm air.
Ethylene generators shall be listed and labeled by an approved testing laboratory, approved by the fire code official and used only in approved rooms in accordance with the ethylene generator manufacturer's instructions. The listing evaluation shall include documentation that the concentration of ethylene gas does not exceed 25 percent of the lower explosive limit (LEL).
Ethylene generators shall be used in rooms having a volume of not less than 1,000 cubic feet (28 m3). Rooms shall have air circulation to ensure even distribution of ethylene gas and shall be free from sparks, open flames or other ignition sources.