Exception: The permanent open space of 60 feet (18 288 mm) shall be permitted to be reduced to not less than 40 feet (12 192 mm), provided the following requirements are met:
Exception: The type of construction allowable building height and building area of anchor buildings greater than three stories above grade plane shall comply with Section 503, as modified by Sections 504 and 506.
Exception: An automatic sprinkler system shall not be required in spaces or areas of open parking garages separated from the covered or open mall building in accordance with Section 402.4.2.3 and constructed in accordance with Section 406.5.
|OLF = (0.00007) (GLA) + 25||(Equation 4-1)|
|OLF||=||The occupant load factor (square feet per |
|GLA||=||The gross leasable area (square feet).|
Exception: Tenant spaces attached to a covered or open mall building but with a means of egress system that is totally independent of the open mall of an open mall building or of a covered mall building shall not be considered as gross leasable area for determining the required means of egress for the mall building.
Exception: Access to exits are permitted by way of a dead-end mall which does not exceed a length equal to twice the width of the mall measured at the narrowest location within the dead-end portion of the mall.
Exception: The required fire-resistance rating of columns supporting floors shall not be permitted to be reduced.
MINIMUM BOND STRENGTH
|HEIGHT OF BUILDINGa||SFRM MINIMUM BOND STRENGTH|
|Up to 420 feet||430 psf|
|Greater than 420 feet||1,000 psf|
Exception: Two connections to the same main shall be permitted provided the main is valved such that an interruption can be isolated so that the water supply will continue without interruption through no fewer than one of the connections.
Exception: Asphalt surfaces shall be permitted at ground level in carports.
Exception: Vehicle barriers are not required in vehicle storage compartments in a mechanical access parking garage.
Exception: A single door shall be allowed provided the sources of ignition in the appliance are not less than 18 inches (457 mm) above the floor.
Exception: Openings are not required to be distributed over 40 percent of the building perimeter where the required openings are uniformly distributed over two opposing sides of the building.
OPEN PARKING GARAGES AREA AND HEIGHT
|TYPE OF CONSTRUCTION||AREA PER TIER |
|HEIGHT (in tiers)|
|Ramp access||Mechanical access|
|Automatic sprinkler system|
|IB||Unlimited||12 tiers||12 tiers||18 tiers|
|IIA||50,000||10 tiers||10 tiers||15 tiers|
|IIB||50,000||8 tiers||8 tiers||12 tiers|
|IV||50,000||4 tiers||4 tiers||4 tiers|
Exception: The grade-level tier is permitted to contain an office, waiting and toilet rooms having a total combined area of not more than 1,000 square feet (93 m2). Such area need not be separated from the open parking garage.
In open parking garages having a spiral or sloping floor, the horizontal projection of the structure at any cross section shall not exceed the allowable area per parking tier. In the case of an open parking garage having a continuous spiral floor, each 9 feet 6 inches (2896 mm) of height, or portion thereof, shall be considered a tier.
The clear height of a parking tier shall be not less than 7 feet (2134 mm), except that a lower clear height is permitted in mechanical-access open parking garages where approved by the building official.
Means of egress from detention and correctional occupancies that traverse other use areas shall, as a minimum, conform to requirements for detention and correctional occupancies.
Exception: Provisions for remote locking and unlocking of occupied rooms in Occupancy Condition 4 are not required provided that not more than 10 locks are necessary to be unlocked in order to move occupants from one smoke compartment to a refuge area within 3 minutes. The opening of necessary locks shall be accomplished with not more than two separate keys.
The room shall have a floor area of not less than 80 square feet (7.44 m2) for a single machine and not less than 40 square feet (3.7 m2) for each additional machine. Each motion picture projector, floodlight, spotlight or similar piece of equipment shall have a clear working space of not less than 30 inches by 30 inches (762 mm by 762 mm) on each side and at the rear thereof, but only one such space shall be required between two adjacent projectors. The projection room and the rooms appurtenant thereto shall have a ceiling height of not less than 7 feet 6 inches (2286 mm). The aggregate of openings for projection equipment shall not exceed 25 percent of the area of the wall between the projection room and the auditorium. Openings shall be provided with glass or other approved material, so as to close completely the opening.
Exception: Stages need not be constructed of the same materials as required for the type of construction provided the construction complies with one of the following:
Exception: Floors of fly galleries and catwalks shall be constructed of any approved material.
For flammable decorative materials, see the International Fire Code.
HEIGHT AND AREA LIMITATIONS FOR AIRPORT TRAFFIC
|TYPE OF CONSTRUCTION||HEIGHTa |
|MAXIMUM AREA |
Exception: Aircraft hangars with individual lease spaces not exceeding 2,000 square feet (186 m2) each in which servicing, repairing or washing is not conducted and fuel is not dispensed shall have floors that are graded toward the door, but shall not require a separator.
Exception: Where a fixed base operator has separate repair facilities on site, Group II hangars operated by a fixed base operator used for storage of transient aircraft only shall have a fire suppression system, but the system is exempt from foam requirements.
[F] TABLE 412.4.6
HANGAR FIRE SUPPRESSION REQUIREMENTSa,b,c
|MAXIMUM SINGLE |
|TYPE OF CONSTRUCTION|
|≥ 40,001||Group I||Group I||Group I||Group I||Group I||Group I||Group I||Group I||Group I|
|40,000||Group II||Group II||Group II||Group II||Group II||Group II||Group II||Group II||Group II|
|30,000||Group III||Group II||Group II||Group II||Group II||Group II||Group II||Group II||Group II|
|20,000||Group III||Group III||Group II||Group II||Group II||Group II||Group II||Group II||Group II|
|15,000||Group III||Group III||Group III||Group II||Group III||Group II||Group III||Group II||Group II|
|12,000||Group III||Group III||Group III||Group III||Group III||Group III||Group III||Group II||Group II|
|8,000||Group III||Group III||Group III||Group III||Group III||Group III||Group III||Group III||Group II|
|5,000||Group III||Group III||Group III||Group III||Group III||Group III||Group III||Group III||Group III|