Heads up: There are no amended sections in this chapter.
Fuel cell power plants with a power output of less than 50 kW shall be listed and installed in accordance with the manufacturer's instructions. Fuel cell power plants with a power output of greater than 50 kW shall be installed in accordance with NFPA 853. [NFPA 54:10.30] Stationary fuel cell power plants shall be tested in accordance with CSA FC-1.
The installation of gas engines shall conform to NFPA 37. [NFPA 54:10.23]
Stationary gas engines shall not be rigidly connected to the gas supply piping. [NFPA 54:10.23.1]