(The content of this Appendix is based on Annex F of NFPA 54)

This appendix provides general
guidelines for sizing venting systems serving appliances
equipped with draft hoods, Category I appliances, and
appliances listed for use with Type B vents.

See Figure G 101.2(1) through Figure G 101.2(14).

Table 510.1.2(1) is used where sizing a Type B double-wall gas vent connected directly to the appliance.

Table 510.1.2(2) is used where sizing a single-wall metal vent connector attached to a Type B double-wall gas vent.

Table 510.1.2(3) is used where sizing a Type B double-wall gas vent connector attached to a tile-lined masonry chimney.

1.

2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 510.1.2(4) is used where sizing a single-wall vent connector attached to a tile-lined masonry chimney.

1.

2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal vent serving a single draft hood-equipped appliance. [See Table 510.1.2(5)]

Table 510.2(1) is used where sizing Type B double-wall gas vent connectors attached to a Type B double-wall common vent.

Table 510.2(2) is used where sizing single-wall vent connectors attached to a Type B double-wall common vent.

Table 510.2(3) is used where sizing Type B double-wall vent connectors attached to a tile-lined masonry chimney.

1.

2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 510.2(4) is used where sizing single-wall metal vent connectors attached to a tile-lined masonry chimney.

1.

2. Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal pipe vent serving two or more draft hood-equipped appliances. [See Table 510.2(5)]

Example: Manifolded common vent connector

Example: Offset common vent

Table 510.1.2(1) is used where sizing a Type B double-wall gas vent connected directly to the appliance.

**Note:**The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 510.1.2(2) is used where sizing a single-wall metal vent connector attached to a Type B double-wall gas vent.

**Note:**The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 510.1.2(3) is used where sizing a Type B double-wall gas vent connector attached to a tile-lined masonry chimney.

**Notes:**1.

*A*is the equivalent cross-sectional area of the tile liner.2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 510.1.2(4) is used where sizing a single-wall vent connector attached to a tile-lined masonry chimney.

**Notes:**1.

*A*is the equivalent cross-sectional area of the tile liner.2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal vent serving a single draft hood-equipped appliance. [See Table 510.1.2(5)]

Table 510.2(1) is used where sizing Type B double-wall gas vent connectors attached to a Type B double-wall common vent.

**Note:**Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 510.2(2) is used where sizing single-wall vent connectors attached to a Type B double-wall common vent.

**Note:**Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 510.2(3) is used where sizing Type B double-wall vent connectors attached to a tile-lined masonry chimney.

**Notes:**1.

*A*is the equivalent cross-sectional area of the tile liner.2. The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 510.2(4) is used where sizing single-wall metal vent connectors attached to a tile-lined masonry chimney.

**Notes:**1.

*A*is the equivalent cross-sectional area of the tile liner.2. Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal pipe vent serving two or more draft hood-equipped appliances. [See Table 510.2(5)]

Example: Manifolded common vent connector

*L*shall not exceed 18 times the common vent connector manifold inside diameter; that is, a 4 inch (102 mm) inside diameter common vent connector manifold shall not exceed 72 inches (1829 mm) in length._{M}**Note:**This is an illustration of a typical manifolded vent connector. Different appliance, vent connector, or common vent types are possible.Example: Offset common vent

**Note:**This is an illustration of a typical offset vent. Different appliance, vent connector, or vent types are possible.An installer has a 120000 British thermal units
per hour (Btu/h) (35 kW) input appliance with a 5 inch (127
mm) diameter draft hood outlet that needs to be vented into a
10 foot (3048 mm) high Type B vent system. What size vent
shall be used assuming: (1) a 5 foot (1524 mm) lateral single-wall
metal vent connector is used with two 90 degree (1.57
rad) elbows or (2) a 5 foot (1524 mm) lateral single-wall
metal vent connector is used with three 90 degree (1.57 rad)
elbows in the vent system? (See Figure G 101.3)

Solution:

Table 510.1.2(2) shall be used to solve this problem because single-wall metal vent connectors are being used with a Type B vent, as follows:

Solution:

Table 510.1.2(2) shall be used to solve this problem because single-wall metal vent connectors are being used with a Type B vent, as follows:

- Read down the first column in Table 510.1.2(2) until the row associated with a 10 foot (3048 mm) height and 5 foot (1524 mm) lateral is found. Read across this row until a vent capacity exceeding 120000 Btu/h (35 kW) is located in the shaded columns labeled NAT Max for draft hood-equipped appliances. In this case, a 5 inch (127 mm) diameter vent has a capacity of 122000 Btu/h (35.7 kW) and shall be permitted to be used for this application.
- Where three 90 degree (1.57 rad) elbows are used in
the vent system, the maximum vent capacity listed in
the tables shall be reduced by 10 percent. This implies
that the 5 inch (127 mm) diameter vent has an adjusted
capacity of 110000 Btu/h (32 kW). In this case, the
vent system shall be increased to 6 inches (152 mm) in
diameter. See the following calculations:

122000 Btu/h (35.7 kW) x 0.90 = 110000 Btu/h (32 kW) for 5 inch (127 mm) vent From Table 510.1.2(2), select 6 inch (152 mm) vent. 186000 Btu/h (54.5 kW) x 0.90 = 167000 Btu/h (49 kW)

This figure is exceeding the required 120000 Btu/h (35 kW). Therefore, use a 6 inch (152 mm) vent and connector where three elbows are used.

An installer has an 80000 Btu/h (23.4 kW)
input fan-assisted appliance that shall be installed using 10
feet (3048 mm) of lateral connector attached to a 30 foot
high (9144 mm) Type B vent. Two 90 degree (1.57 rad)
elbows are needed for the installation. Is a single-wall metal
vent connector permitted to be used for this application?
(See Figure G 101.4)

Solution:

Table 510.1.2(2) refers to the use of single-wall metal vent connectors with Type B vent. In the first column find the row associated with a 30 foot (9144 mm) height and a 10 foot (3048 mm) lateral. Read across this row, looking at the FAN Min and FAN Max columns, to find that a 3 inch (76 mm) diameter single-wall metal vent connector is not recommended. Moving to the next larger size single-wall connector [4 inch (102 mm)] we find that a 4 inch (102 mm) diameter single-wall metal connector has a recommended maximum vent capacity of 144000 Btu/h (42 kW). The 80000 Btu/h (23.4 kW) fan-assisted appliance is outside this range, so the conclusion is that a single-wall metal connector shall not be used to vent the appliance using a 10 foot (3048 mm) of lateral for the connector. However, if the 80,000 Btu/hr (23.4 kW) input appliance is moved within 5 feet (1524 mm) of the vertical vent, a 4 inch (102 mm) single-wall metal connector shall be used to vent the appliance. Table 510.1.2(2) shows the acceptable range of vent capacities for a 4 inch (102 mm) vent with 5 feet (1524 mm) of lateral to be between 72000 Btu/h (21.1 kW) and 157000 Btu/h (46 kW).

Where the appliance cannot be moved closer to the vertical vent, then a Type B vent shall be used as the connector material. In this case, Table 510.1.2(1) shows that, for a 30 foot (9144 mm) high vent with 10 feet (3048 mm) of lateral, the acceptable range of vent capacities for a 4 inch (102 mm) diameter vent attached to a fan-assisted appliance is between 37000 Btu/h (10.8 kW) and 150000 Btu/h (44 kW).

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293kW

Solution:

Table 510.1.2(2) refers to the use of single-wall metal vent connectors with Type B vent. In the first column find the row associated with a 30 foot (9144 mm) height and a 10 foot (3048 mm) lateral. Read across this row, looking at the FAN Min and FAN Max columns, to find that a 3 inch (76 mm) diameter single-wall metal vent connector is not recommended. Moving to the next larger size single-wall connector [4 inch (102 mm)] we find that a 4 inch (102 mm) diameter single-wall metal connector has a recommended maximum vent capacity of 144000 Btu/h (42 kW). The 80000 Btu/h (23.4 kW) fan-assisted appliance is outside this range, so the conclusion is that a single-wall metal connector shall not be used to vent the appliance using a 10 foot (3048 mm) of lateral for the connector. However, if the 80,000 Btu/hr (23.4 kW) input appliance is moved within 5 feet (1524 mm) of the vertical vent, a 4 inch (102 mm) single-wall metal connector shall be used to vent the appliance. Table 510.1.2(2) shows the acceptable range of vent capacities for a 4 inch (102 mm) vent with 5 feet (1524 mm) of lateral to be between 72000 Btu/h (21.1 kW) and 157000 Btu/h (46 kW).

Where the appliance cannot be moved closer to the vertical vent, then a Type B vent shall be used as the connector material. In this case, Table 510.1.2(1) shows that, for a 30 foot (9144 mm) high vent with 10 feet (3048 mm) of lateral, the acceptable range of vent capacities for a 4 inch (102 mm) diameter vent attached to a fan-assisted appliance is between 37000 Btu/h (10.8 kW) and 150000 Btu/h (44 kW).

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293kW

An installer has an 80 000 Btu/h (23.4 kW) input
appliance with a 4 inch (102 mm) diameter draft hood outlet
that needs to be vented into a 12 foot (3658 mm) high Type
B vent. The vent connector has a 5 foot (1524 mm) lateral
length and is also Type B vent. Is this appliance permitted to
be vented using a 4 inch (102 mm) diameter vent?

Solution:

Table 510.1.2(1) is used in the case of an all Type B Vent system. However, since there is no entry in Table 510.1.2(1) for a height of 12 feet (3658 mm), interpolation shall be used. Read down the 4 inch (102 mm) diameter NAT Max column to the row associated with a 10 foot (3048 mm) height and 5 foot (1524 mm) lateral to find the capacity value of 77000 Btu/h (22.6 kW). Read further down to the 15 foot (4572 mm) height, 5 foot (1524 mm) lateral row to find the capacity value of 87000 Btu/h (25.5 kW). The difference between the 15 foot (4572 mm) height capacity value and the 10 foot (3048 mm) height capacity value is 10000 Btu/h (3 kW). The capacity for a vent system with a 12 foot (3658 mm) height is equal to the capacity for a 10 foot (3048 mm) height plus two-fifths of the difference between the 10 foot (3048 mm) and 15 foot (4572 mm) height values, or 77000 Btu/h (22.6 kW) +

Solution:

Table 510.1.2(1) is used in the case of an all Type B Vent system. However, since there is no entry in Table 510.1.2(1) for a height of 12 feet (3658 mm), interpolation shall be used. Read down the 4 inch (102 mm) diameter NAT Max column to the row associated with a 10 foot (3048 mm) height and 5 foot (1524 mm) lateral to find the capacity value of 77000 Btu/h (22.6 kW). Read further down to the 15 foot (4572 mm) height, 5 foot (1524 mm) lateral row to find the capacity value of 87000 Btu/h (25.5 kW). The difference between the 15 foot (4572 mm) height capacity value and the 10 foot (3048 mm) height capacity value is 10000 Btu/h (3 kW). The capacity for a vent system with a 12 foot (3658 mm) height is equal to the capacity for a 10 foot (3048 mm) height plus two-fifths of the difference between the 10 foot (3048 mm) and 15 foot (4572 mm) height values, or 77000 Btu/h (22.6 kW) +

^{2}/_{5}x 10000 Btu/h (3 kW) = 81000 Btu/h (23.7 kW). Therefore, a 4 inch (102 mm) diameter vent shall be used in the installation.A 35000 Btu/h (10.3 kW)
water heater is to be common vented with a 150000 Btu/h
(44 kW) furnace, using a common vent with a total height of
30 feet (9144 mm). The connector rise is 2 feet (610 mm) for
the water heater with a horizontal length of 4 feet (1219
mm). The connector rise for the furnace is 3 feet (914 mm)
with a horizontal length of 8 feet (2438 mm). Assume single-wall
metal connectors will be used with Type B vent. What
size connectors and combined vent should be used in this
installation? (See Figure G 101.6)

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

Solution:

Table 510.2(2) shall be used to size single-wall metal vent connectors attached to Type B vertical vents. In the vent connector capacity portion of Table 510.2(2), find the row associated with a 30 foot (9144 mm) vent height. For a 2 foot (610 mm) rise on the vent connector for the water heater, read the shaded columns for draft hood-equipped appliances to find that a 3 inch (76 mm) diameter vent connector has a capacity of 37000 Btu/h (10.8 kW). Therefore, a 3 inch (76 mm) single-wall metal vent connector shall be used with the water heater. For a draft hood-equipped furnace with a 3 foot (914 mm) rise, read across the row to find that a 5 inch (127 mm) diameter vent connector has a maximum capacity of 120000 Btu/h (35 kW) (which is too small for the furnace), and a 6 inch (152 mm) diameter vent connector has a maximum vent capacity of 172000 Btu/h (50 kW). Therefore, a 6 inch (152 mm) diameter vent connector shall be used with the 150000 Btu/h (44 kW) furnace. Since both vent connector horizontal lengths are less than the maximum lengths listed in Section 510.2.1, the table values shall be used without adjustments.

In the common vent capacity portion of Table 510.2(2), find the row associated with a 30 foot (9144 mm) vent height and read over to the NAT + NAT portion of the 6 inch (152 mm) diameter column to find a maximum combined capacity of 257000 Btu/h (75 kW). Since the two appliances total 185000 Btu/h (54 kW), a 6 inch (152 mm) common vent shall be used.

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

Solution:

Table 510.2(2) shall be used to size single-wall metal vent connectors attached to Type B vertical vents. In the vent connector capacity portion of Table 510.2(2), find the row associated with a 30 foot (9144 mm) vent height. For a 2 foot (610 mm) rise on the vent connector for the water heater, read the shaded columns for draft hood-equipped appliances to find that a 3 inch (76 mm) diameter vent connector has a capacity of 37000 Btu/h (10.8 kW). Therefore, a 3 inch (76 mm) single-wall metal vent connector shall be used with the water heater. For a draft hood-equipped furnace with a 3 foot (914 mm) rise, read across the row to find that a 5 inch (127 mm) diameter vent connector has a maximum capacity of 120000 Btu/h (35 kW) (which is too small for the furnace), and a 6 inch (152 mm) diameter vent connector has a maximum vent capacity of 172000 Btu/h (50 kW). Therefore, a 6 inch (152 mm) diameter vent connector shall be used with the 150000 Btu/h (44 kW) furnace. Since both vent connector horizontal lengths are less than the maximum lengths listed in Section 510.2.1, the table values shall be used without adjustments.

In the common vent capacity portion of Table 510.2(2), find the row associated with a 30 foot (9144 mm) vent height and read over to the NAT + NAT portion of the 6 inch (152 mm) diameter column to find a maximum combined capacity of 257000 Btu/h (75 kW). Since the two appliances total 185000 Btu/h (54 kW), a 6 inch (152 mm) common vent shall be used.

In this case, a 35000 Btu/h (10.3 kW) input draft hood-equipped water heater with a 4 inch (102 mm) diameter draft hood outlet, 2 feet (610 mm)
of connector rise, and 4 feet (1219 mm) of horizontal length is to be common vented with a 100000 Btu/h (29 kW) fan assisted furnace with a 4 inch (102 mm) diameter flue collar, 3 feet (914 mm) of connector rise, and 6 feet (1829 mm) of horizontal length. The common vent consists of a 30 foot
(9144 mm) height of Type B vent. What are the recommended vent diameters for each connector and the common vent? The installer would like to use a single-wall metal vent connector. (See Figure G 101.7)

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

Solution:

Water Heater Vent Connector Diameter. Since the water heater vent connector horizontal length of 4 feet (1219 mm) is less than the maximum value listed in Table 510.2(2), the venting table values shall be used without adjustment. Using the Vent Connector Capacity portion of Table 510.2(2), read down the Total Vent Height (H) column to 30 feet (9144 mm) and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input rating of 37000 Btu/h (l0.8 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 510.2.17. A 4 inch (102 mm) vent connector has a maximum input rating of 67000 Btu/h (19.6 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected. Since the water heater is equipped with a draft hood, there are no minimum input rating restrictions.

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 510.2(2), read down the Total Vent Height (H) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (R) row. Since the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 119000 Btu/h (34.9 kW) and a minimum input rating of 85 000 Btu/h (24.9 kW).

The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector is used. Since the furnace vent connector horizontal length of 6 feet (1829 mm) is less than the maximum value listed in Section 510.2.1, the venting table values shall be used without adjustment. Where the furnace had an input rating of 80000 Btu/h (23.4 kW), a Type B vent connector is needed in order to meet the minimum capacity limit.

Common Vent Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 510.2(2), read down the Vent Height (H) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating equal to or exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 132000 Btu/h (39 kW) and the 5 inch (127 mm) common vent has a capacity of 202000 Btu/h (59 kW). Therefore, the 5 inch (127 mm) common vent shall be used in this example.

Summary: In this example, the installer shall use a 4 inch (102 mm) diameter, single-wall metal vent connector for the water heater and a 4 inch (102 mm) diameter, single wall metal vent connector for the furnace. The common vent shall be a 5 inch (127 mm) diameter Type B vent.

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

Solution:

Water Heater Vent Connector Diameter. Since the water heater vent connector horizontal length of 4 feet (1219 mm) is less than the maximum value listed in Table 510.2(2), the venting table values shall be used without adjustment. Using the Vent Connector Capacity portion of Table 510.2(2), read down the Total Vent Height (H) column to 30 feet (9144 mm) and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input rating of 37000 Btu/h (l0.8 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 510.2.17. A 4 inch (102 mm) vent connector has a maximum input rating of 67000 Btu/h (19.6 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected. Since the water heater is equipped with a draft hood, there are no minimum input rating restrictions.

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 510.2(2), read down the Total Vent Height (H) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (R) row. Since the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 119000 Btu/h (34.9 kW) and a minimum input rating of 85 000 Btu/h (24.9 kW).

The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector is used. Since the furnace vent connector horizontal length of 6 feet (1829 mm) is less than the maximum value listed in Section 510.2.1, the venting table values shall be used without adjustment. Where the furnace had an input rating of 80000 Btu/h (23.4 kW), a Type B vent connector is needed in order to meet the minimum capacity limit.

Common Vent Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 510.2(2), read down the Vent Height (H) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating equal to or exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 132000 Btu/h (39 kW) and the 5 inch (127 mm) common vent has a capacity of 202000 Btu/h (59 kW). Therefore, the 5 inch (127 mm) common vent shall be used in this example.

Summary: In this example, the installer shall use a 4 inch (102 mm) diameter, single-wall metal vent connector for the water heater and a 4 inch (102 mm) diameter, single wall metal vent connector for the furnace. The common vent shall be a 5 inch (127 mm) diameter Type B vent.

In this case, the water heater and fan-assisted furnace of Example 5(a) are to be common-vented into a clay-tile-lined masonry chimney with a 30 foot (9144 mm) height. The chimney is not exposed to the outdoors below the roof line. The internal dimensions of the clay tile liner are nominally 8 inches (203 mm) by 12 inches (305 mm). Assuming the same vent connector heights, laterals, and materials found in Example 5(a), what are the recommended vent connector diameters, and is this an acceptable installation?

Solution:

Table 510.2(4) is used to size common venting installations involving single-wall connectors into masonry chimneys.

Water Heater Vent Connector Diameter. Using Table 510.2(4), Vent Connector Capacity, read down the Vent Height (H) column to 30 feet (9144 mm), and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input of 31000 Btu/h (9 kW), while a 4 inch (102 mm) vent connector has a maximum input of 57000 Btu/h (16.7 kW). A 4 inch (102 mm) vent connector is be used.

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 510.2(4), read down the total Vent Height (H) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (R) row. Because the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 127000 Btu/h (37 kW) and a minimum input rating of 95000 Btu/h (27.8 kW). The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector is used.

Masonry Chimney. From Table G101.8, the equivalent area for a nominal liner size of 8 inches (203 mm) by 12 inches (305 mm) is 63.6 square inches (0.041 m

Section 510.2.16 requires the common vent area to not exceed seven times the smallest listed appliance categorized vent area, flue collar area, or draft hood outlet area. Both appliances in this installation have 4 inch (102 mm) diameter outlets. From Table G 101.8, the equivalent area for an inside diameter of 4 inches (102 mm) is 12.2 square inches (0.008 m

For SI units: 1 inch = 25.4 mm, 1 square inch = 0.000645 m

Solution:

Table 510.2(4) is used to size common venting installations involving single-wall connectors into masonry chimneys.

Water Heater Vent Connector Diameter. Using Table 510.2(4), Vent Connector Capacity, read down the Vent Height (H) column to 30 feet (9144 mm), and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input of 31000 Btu/h (9 kW), while a 4 inch (102 mm) vent connector has a maximum input of 57000 Btu/h (16.7 kW). A 4 inch (102 mm) vent connector is be used.

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 510.2(4), read down the total Vent Height (H) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (R) row. Because the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 127000 Btu/h (37 kW) and a minimum input rating of 95000 Btu/h (27.8 kW). The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector is used.

Masonry Chimney. From Table G101.8, the equivalent area for a nominal liner size of 8 inches (203 mm) by 12 inches (305 mm) is 63.6 square inches (0.041 m

^{2}). Using Table 510.2(4), Common Vent Capacity, read down the FAN + NAT column under the Minimum Internal Area of Chimney value of 63 to the row for 30 foot (9144 mm) height to find a capacity value of 739000 Btu/h (217 kW). The combined input rating of the furnace and water heater, 135000 Btu/h (40 kW), is less than the table value so this is an acceptable installation.Section 510.2.16 requires the common vent area to not exceed seven times the smallest listed appliance categorized vent area, flue collar area, or draft hood outlet area. Both appliances in this installation have 4 inch (102 mm) diameter outlets. From Table G 101.8, the equivalent area for an inside diameter of 4 inches (102 mm) is 12.2 square inches (0.008 m

^{2}). Seven times 12.2 equals 85.4, which is exceeding 63.6, so this configuration is acceptable.NOMINAL LINER SIZE (inches) |
INSIDE DIMENSIONS OF LINER (inches) |
INSIDE DIAMETER OR EQUIVALENT DIAMETER (inches) |
EQUIVALENT AREA (square inches) |
---|---|---|---|

4 x 8 | 2^{1}/_{2} x 6^{1}/_{2} |
4.0 | 12.2 |

5.0 | 19.6 | ||

6.0 | 28.3 | ||

7.0 | 38.3 | ||

8 x 8 | 6^{3}/_{4} x 6^{3}/_{4} |
7.4 | 42.7 |

8.0 | 50.3 | ||

8 x 12 | 6^{1}/_{2} x 10^{1}/_{2} |
9.0 | 63.6 |

10.0 | 78.5 | ||

12 x 12 | 9^{3}/_{4} x 9^{3}/_{4} |
10.4 | 83.3 |

11.0 | 95.0 | ||

12 x 16 | 9^{1}/_{2} x 13^{1}/_{2} |
11.8 | 107.5 |

12.0 | 113.0 | ||

14.0 | 153.9 | ||

16 x 16 | 13^{1}/_{4} x 13^{1}/_{4} |
14.5 | 162.9 |

15.0 | 176.7 | ||

16 x 20 | 13 x 17 | 16.2 | 206.1 |

18.0 | 254.4 | ||

20 x 20 | 16^{3}/_{4} x 16^{3}/_{4} |
18.2 | 260.2 |

20.0 | 314.1 | ||

20 x 24 | 16^{1}/_{2} x 20^{1}/_{2} |
20.1 | 314.2 |

22.0 | 380.1 | ||

24 x 24 | 20^{1}/_{4} x 20^{1}/_{4} |
22.1 | 380.1 |

24.0 | 452.3 | ||

24 x 28 | 20^{1}/_{4} x 24^{1}/_{4} |
24.1 | 456.2 |

28 x 28 | 24^{1}/_{4} x 24^{1}/_{4} |
26.4 | 543.3 |

27.0 | 572.5 | ||

30 x 30 | 25^{1}/_{2} x 25^{1}/_{2} |
27.9 | 607.0 |

30.0 | 706.8 | ||

30 x 36 | 25^{1}/_{2} x 31^{1}/_{2} |
30.9 | 749.9 |

33.0 | 855.3 | ||

36 x 36 | 31^{1}/_{2} x 31^{1}/_{2} |
34.4 | 929.4 |

36.0 | 1017.9 |

For SI units: 1 inch = 25.4 mm, 1 square inch = 0.000645 m

^{2}* Where liner sizes differ dimensionally from those shown in this table, equivalent diameters shall be permitted to be determined from published tables for square and rectangular ducts of equivalent carrying capacity or by other engineering methods.

In this case, the water heater and fan-assisted furnace of Examples 5(a) and 5(b) are to be common-vented into an exterior masonry chimney. The chimney height, clay-tile-liner dimensions, and vent connector heights and laterals are the same as in Example 5(b). This system is being installed in Charlotte, North Carolina. Does this exterior masonry chimney need to be relined? Where so, what corrugated metallic liner size is recommended? What vent connector diameters are recommended? [See Table G 101.8 and Figure 510.1.2(6)]

Solution:

According to Section 510.2.19, Type B vent connectors are required to be used with exterior masonry chimneys. Use Table 510.2(8) and Table 510.2(9) to size FAN+NAT common venting installations involving Type-B double wall connectors into exterior masonry chimneys.

The local 99 percent winter design temperature needed to use Table 510.2(8) and Table 510.2(9) shall be found in the ASHRAE Handbook - Fundamentals. For Charlotte, North Carolina, this design temperature is 19°F (-7.2°C).

Chimney Liner Requirement. As in Example 5(b), use the 63 square inches (0.04 m

According to Section 510.2.18, Table 510.2(1) or Table 510.2(2) are used for sizing corrugated metallic liners in masonry chimneys, with the maximum common vent capacities reduced by 20 percent. This example will be continued assuming Type B vent connectors.

Water Heater Vent Connector Diameter. Using Table 510.2(1) Connector Capacity, read down the total Vent Height (H) column to 30 feet (9144 mm), and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/hour rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum capacity of 39000 Btu/h (11.4 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 510.2.19. A 4 inch (102 mm) vent connector has a maximum input rating of 70000 Btu/h (20.5 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected.

Furnace Vent Connector Diameter. Using Table 510.2(1), Vent Connector Capacity, read down the total Vent Height (H) column to 30 feet (9144 mm), and read across the 3 feet (914 mm) Connector Rise (R) row to the first Btu/h rating in the FAN MAX column that is equal to or exceeding the furnace input rating. The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted.

Chimney Liner Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 510.2(1), read down the total Vent Height (H) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 138000 Btu/h (40.4 kW). Reducing the maximum capacity by 20 percent results in a maximum capacity for a 4 inch (102 mm) corrugated liner of 110000 Btu/h (32 kW), less than the total input of 135000 Btu/h (40 kW). So a larger liner is needed. The 5 inch (127 mm) common vent capacity listed in Table 510.2(1) is 210000 Btu/h (62 kW), and after reducing by 20 percent is 168000 Btu/h (49.2 kW). Therefore, a 5 inch (127 mm) corrugated metal liner shall be used in this example.

Single Wall Connectors. Once it has been established that relining the chimney is necessary, Type B double-wall vent connectors are not specifically required. This example shall be permitted to be redone using Table 510.2(2) for single-wall vent connectors. For this case, the vent connector and liner diameters would be the same as found for Type B double-wall connectors.

Solution:

According to Section 510.2.19, Type B vent connectors are required to be used with exterior masonry chimneys. Use Table 510.2(8) and Table 510.2(9) to size FAN+NAT common venting installations involving Type-B double wall connectors into exterior masonry chimneys.

The local 99 percent winter design temperature needed to use Table 510.2(8) and Table 510.2(9) shall be found in the ASHRAE Handbook - Fundamentals. For Charlotte, North Carolina, this design temperature is 19°F (-7.2°C).

Chimney Liner Requirement. As in Example 5(b), use the 63 square inches (0.04 m

^{2}) internal area column for this size clay tile liner. Read down the 63 square inches (0.04 m^{2}) column of Table 510.2(8) to the 30 foot (9144 mm) height row to find that the combined appliance maximum input is 747000 Btu/h (218.9 kW). The combined input rating of the appliance in this installation, 135000 Btu/h (40 kW), is less than the maximum value, so this criterion is satisfied. Table 510.2(9), at a 19°F (-7.2°C) design temperature, and at the same vent height and internal area used earlier, shows that the minimum allowable input rating of a space-heating appliance is 470000 Btu/h (137.7 kW). The furnace input rating of 100000 Btu/h (29 kW) is less than this minimum value. So this criterion is not satisfied, and an alternative venting design shall be used, such as a Type B vent shown in Example 5(a) or a listed chimney liner system shown in the rest of the example.According to Section 510.2.18, Table 510.2(1) or Table 510.2(2) are used for sizing corrugated metallic liners in masonry chimneys, with the maximum common vent capacities reduced by 20 percent. This example will be continued assuming Type B vent connectors.

Water Heater Vent Connector Diameter. Using Table 510.2(1) Connector Capacity, read down the total Vent Height (H) column to 30 feet (9144 mm), and read across the 2 feet (610 mm) Connector Rise (R) row to the first Btu/hour rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum capacity of 39000 Btu/h (11.4 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 510.2.19. A 4 inch (102 mm) vent connector has a maximum input rating of 70000 Btu/h (20.5 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected.

Furnace Vent Connector Diameter. Using Table 510.2(1), Vent Connector Capacity, read down the total Vent Height (H) column to 30 feet (9144 mm), and read across the 3 feet (914 mm) Connector Rise (R) row to the first Btu/h rating in the FAN MAX column that is equal to or exceeding the furnace input rating. The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted.

Chimney Liner Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 510.2(1), read down the total Vent Height (H) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 138000 Btu/h (40.4 kW). Reducing the maximum capacity by 20 percent results in a maximum capacity for a 4 inch (102 mm) corrugated liner of 110000 Btu/h (32 kW), less than the total input of 135000 Btu/h (40 kW). So a larger liner is needed. The 5 inch (127 mm) common vent capacity listed in Table 510.2(1) is 210000 Btu/h (62 kW), and after reducing by 20 percent is 168000 Btu/h (49.2 kW). Therefore, a 5 inch (127 mm) corrugated metal liner shall be used in this example.

Single Wall Connectors. Once it has been established that relining the chimney is necessary, Type B double-wall vent connectors are not specifically required. This example shall be permitted to be redone using Table 510.2(2) for single-wall vent connectors. For this case, the vent connector and liner diameters would be the same as found for Type B double-wall connectors.