See Figure F 101.1(1) through Figure F 101.1(14).

Table 803.1.2(1) is used where sizing a Type B double-wall gas vent connected directly to the appliance.

Table 803.1.2(2) is used where sizing a single-wall metal vent connector attached to a Type B double-wall gas vent.

Table 803.1.2(3) is used where sizing a Type B double-wall gas vent connector attached to a tile-lined masonry chimney.

Table 803.1.2(4) is used where sizing a single-wall vent connector attached to a tile-lined masonry chimney.

Asbestos cement Type B or single-wall metal vent serving a single draft hood-equipped appliance. [See Table 803.1.2(5)]

Table 803.2(1) is used where sizing Type B double-wall gas vent connectors attached to a Type B double-wall common vent.

Table 803.2(2) is used where sizing single-wall vent connectors attached to a Type B double-wall common vent.

Table 803.2(3) is used where sizing Type B double-wall vent connectors attached to a tile-lined masonry chimney.

Table 803.2(4) is used where sizing single-wall metal vent connectors attached to a tile-lined masonry chimney.

Asbestos cement Type B or single-wall metal pipe vent serving two or more draft hood-equipped appliances. [See Table 803.2(5)]

Example: Manifolded common vent connector

Example: Offset common vent

Table 803.1.2(1) is used where sizing a Type B double-wall gas vent connected directly to the appliance.

**Note:**The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 803.1.2(2) is used where sizing a single-wall metal vent connector attached to a Type B double-wall gas vent.

**Note:**The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 803.1.2(3) is used where sizing a Type B double-wall gas vent connector attached to a tile-lined masonry chimney.

**Notes:***A*is the equivalent cross-sectional area of the tile liner.- The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 803.1.2(4) is used where sizing a single-wall vent connector attached to a tile-lined masonry chimney.

**Notes:***A*is the equivalent cross-sectional area of the tile liner.- The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal vent serving a single draft hood-equipped appliance. [See Table 803.1.2(5)]

Table 803.2(1) is used where sizing Type B double-wall gas vent connectors attached to a Type B double-wall common vent.

**Note:**Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 803.2(2) is used where sizing single-wall vent connectors attached to a Type B double-wall common vent.

**Note:**Each appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.Table 803.2(3) is used where sizing Type B double-wall vent connectors attached to a tile-lined masonry chimney.

**Notes:***A*is the equivalent cross-sectional area of the tile liner.- The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Table 803.2(4) is used where sizing single-wall metal vent connectors attached to a tile-lined masonry chimney.

**Notes:***A*is the equivalent cross-sectional area of the tile liner.- The appliance is permitted to be either Category I draft hood-equipped or fan-assisted type.

Asbestos cement Type B or single-wall metal pipe vent serving two or more draft hood-equipped appliances. [See Table 803.2(5)]

Example: Manifolded common vent connector

*L*shall not exceed 18 times the common vent connector manifold inside diameter; that is, a 4 inch (102 mm) inside diameter common vent connector manifold shall not exceed 72 inches (1829 mm) in length._{M}**Note:**This is an illustration of a typical manifolded vent connector. Different appliance, vent connector, or common vent types are possible.Example: Offset common vent

**Note:**This is an illustration of a typical offset vent. Different appliance, vent connector, or vent types are possible.An installer has a 120000 British thermal units per hour (Btu/h) (35 kW) input appliance with a 5 inch (127 mm)
diameter draft hood outlet that needs to be vented into a 10
foot (3048 mm) high Type B vent system. What size vent
should be used assuming: (1) a 5 foot (1524 mm) lateral
single-wall metal vent connector is used with two 90 degree
(1.57 rad) elbows or (2) a 5 foot (1524 mm) lateral single-wall
metal vent connector is used with three 90 degree (1.57
rad) elbows in the vent system? (See Figure F 101.1)

Solution:

Table 803.1.2(2) shall be used to solve this problem because single-wall metal vent connectors are being used with a Type B vent, as follows:

Solution:

Table 803.1.2(2) shall be used to solve this problem because single-wall metal vent connectors are being used with a Type B vent, as follows:

- Read down the first column in Table 803.1.2(2) until the row associated with a 10 foot (3048 mm) height and foot (1524 mm) lateral is found. Read across this row until a vent capacity exceeding 120000 Btu/h (35 kW) is located in the shaded columns labeled NAT Max for draft hood-equipped appliances. In this case, a 5 inch (127 mm) diameter vent has a capacity of 122000 Btu/h (35.7 kW) and shall be permitted to be used for this application.
- Where three 90 degree (1.57 rad) elbows are used in the
vent system, the maximum vent capacity listed in the tables shall be reduced by 10 percent This implies that the
5 inch (127 mm) diameter vent has an adjusted capacity of
only 110000 Btu/h (32 kW). In this case, the vent system
shall be increased to 6 inches (152 mm) in diameter. See
the following calculations:

122000 Btu/h (35.7 kW) x 0.90 = 110000 Btu/h (32 kW) for 5 inch (127 mm) vent

From Table 803.1.2(2), select 6 inch (152 mm) vent. 186000 Btu/h (54.5 kW)x 0.90 = 167000 Btu/h(49 kW)

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

An installer has an 80000 Btu/h (23.4 kW) input fan-assisted appliance that shall be installed using 10 feet (3048 mm) of lateral connector attached to a 30 foot (9144 mm) high Type B vent. Two 90 degree (1.57 rad) elbows are needed for the installation. Is a single-wall metal vent connector permitted to be used for this application? (See Figure F 101.2)

Solution:

Table 803.1.2(2) refers to the use of single-wall metal vent connectors with Type B vent. In the first column find the row associated with a 30 foot (9144 mm) height and a 10 foot (3048 mm) lateral. Read across this row, looking at the FAN Min and FAN Max columns, to find that a 3 inch (76 mm) diameter single-wall metal vent connector is not recommended. Moving to the next larger size single-wall connector [4 inch (102 mm)] we find that a 4 inch (102 mm) diameter single-wall metal connector has a recommended maximum vent capacity of 144000 Btu/h (42 kW). The 80000 Btu/h (23.4 kW) fan-assisted appliance is outside this range, so the conclusion is that a single-wall metal connector shall not be used to vent the appliance. Table 803.1.2(2) shows the acceptable range of vent capacities for a 4 inch (102 mm) vent with 5 feet (1524 mm) of lateral to be between 72000 Btu/h (21.1 kW) and 157000 Btu/h (46 kW).

Where the appliance cannot be moved closer to the vertical vent, then a Type B vent shall be used as the connector material. In this case, Table 803.1.2(1) shows that, for a 30 foot (9144 mm) high vent with 10 feet (3048 mm) of lateral, the acceptable range of vent capacities for a 4 inch (102 mm) diameter vent attached to a fan-assisted appliance is between 37000 Btu/h (10.8 kW) and 150000 Btu/h (44 kW).

Solution:

Table 803.1.2(2) refers to the use of single-wall metal vent connectors with Type B vent. In the first column find the row associated with a 30 foot (9144 mm) height and a 10 foot (3048 mm) lateral. Read across this row, looking at the FAN Min and FAN Max columns, to find that a 3 inch (76 mm) diameter single-wall metal vent connector is not recommended. Moving to the next larger size single-wall connector [4 inch (102 mm)] we find that a 4 inch (102 mm) diameter single-wall metal connector has a recommended maximum vent capacity of 144000 Btu/h (42 kW). The 80000 Btu/h (23.4 kW) fan-assisted appliance is outside this range, so the conclusion is that a single-wall metal connector shall not be used to vent the appliance. Table 803.1.2(2) shows the acceptable range of vent capacities for a 4 inch (102 mm) vent with 5 feet (1524 mm) of lateral to be between 72000 Btu/h (21.1 kW) and 157000 Btu/h (46 kW).

Where the appliance cannot be moved closer to the vertical vent, then a Type B vent shall be used as the connector material. In this case, Table 803.1.2(1) shows that, for a 30 foot (9144 mm) high vent with 10 feet (3048 mm) of lateral, the acceptable range of vent capacities for a 4 inch (102 mm) diameter vent attached to a fan-assisted appliance is between 37000 Btu/h (10.8 kW) and 150000 Btu/h (44 kW).

An installer has an 80000 Btu/h (23.4 kW) input appliance
with a 4 inch (102 mm) diameter draft hood outlet that needs
to be vented into a 12 foot (3658 mm) high Type B vent. The
vent connector has a 5 foot (1524 mm) lateral length and is
also Type B vent. Is this appliance permitted to be vented
using a 4 inch (102 mm) diameter vent?

Solution:

Table 803.1.2(1) is used in the case of an all Type B Vent system. However, since there is no entry in Table 803.1.2(1) tor a height of 12 feet (3658 mm), interpolation shall be used. Read down the 4 inch (102 mm) diameter NAT Max colunm to the row associated with a 10 foot (3048 mm) height and 5 foot (1524 mm) lateral to find the capacity value of 77000 Btu/h (22.6 kW). Read further down to the 15 foot (4572 mm) height, 5 foot (1524 mm) lateral row to find the capacity value of 87000 Btu/h (25.5 kW). The difference between the 15 foot (4572 mm) height capacity value and the 10 foot (3048 mm) height capacity value is 10000 Btu/h (3 kW). The capacity for a vent system with a 12 foot (3658 mm) height is equal to the capacity for a 10 foot (3048 mm) height plus two-fifths of the difference between the 10 foot (3048 mm) and 15 foot (4572 mm) height values, or 77000 Btulh (22.6 kW) +

Solution:

Table 803.1.2(1) is used in the case of an all Type B Vent system. However, since there is no entry in Table 803.1.2(1) tor a height of 12 feet (3658 mm), interpolation shall be used. Read down the 4 inch (102 mm) diameter NAT Max colunm to the row associated with a 10 foot (3048 mm) height and 5 foot (1524 mm) lateral to find the capacity value of 77000 Btu/h (22.6 kW). Read further down to the 15 foot (4572 mm) height, 5 foot (1524 mm) lateral row to find the capacity value of 87000 Btu/h (25.5 kW). The difference between the 15 foot (4572 mm) height capacity value and the 10 foot (3048 mm) height capacity value is 10000 Btu/h (3 kW). The capacity for a vent system with a 12 foot (3658 mm) height is equal to the capacity for a 10 foot (3048 mm) height plus two-fifths of the difference between the 10 foot (3048 mm) and 15 foot (4572 mm) height values, or 77000 Btulh (22.6 kW) +

^{2}/_{5}x 10000 Btu/h (3 kW) = 81000 Btu/h (23.7 kW). Therefore, a 4 inch (102 mm) diameter vent shall be used in the installation.A 35000 Btu/h (10.3 kW) water heater is to be common vented with a 150000 Btu/h (44 kW) furnace, using a common vent with a total height of 30 feet (9144 mm). The connector rise is 2 feet (610 mm) for the
water heater with a horizontal length of 4 feet (1219 mm).
The connector rise for the furnace is 3 feet (914 mm) with a
horizontal length of 8 feet (2438 mm). Assume single-wall
metal connectors will be used with Type B vent. What size
connectors and combined vent should be used in this installation?
(See Figure F 102.1)

Solution:

Table 803.2(2) shall be used to size single-wall metal vent connectors attached to Type B vertical vents. In the vent connector capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height. For a 2 foot (610 mm) rise on the vent connector for the water heater, read the shaded columns for draft hood-equipped appliances to find that a 3 inch (76 mm) diameter vent connector has a capacity of 37000 Btu/h (10.8 kW). Therefore, a 3 inch (76 mm) single-wall metal vent connector shall be used with the water heater, for a draft hood-equipped furnace with a 3 foot (914 mm) rise, read across the row to find that a 5 inch (127 mm) diameter vent connector has a maximum capacity of 120000 Btu/h (35 kW) (which is too small for the furnace), and a 6 inch (152 mm) diameter vent connector has a maximum vent capacity of 172000 Btu/h (50 kW). Therefore, a 6 inch (152 mm) diameter vent connector shall be used with the 150000 Btu/h (44 kW) furnace. Since both vent connector horizontal lengths are less than the maximum lengths listed in Section 803.2.1, the table values shall be used without adjustments.

In the common vent capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height and read over to the NAT + NAT portion of the 6 inch (152 mm) diameter column to find a maximum combined capacity of 257000 Btu/h (75 kW). Since the two appliances total 185000 Btu/h (54 kW), a 6 inch (152 mm) common vent shall be used.

Solution:

Table 803.2(2) shall be used to size single-wall metal vent connectors attached to Type B vertical vents. In the vent connector capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height. For a 2 foot (610 mm) rise on the vent connector for the water heater, read the shaded columns for draft hood-equipped appliances to find that a 3 inch (76 mm) diameter vent connector has a capacity of 37000 Btu/h (10.8 kW). Therefore, a 3 inch (76 mm) single-wall metal vent connector shall be used with the water heater, for a draft hood-equipped furnace with a 3 foot (914 mm) rise, read across the row to find that a 5 inch (127 mm) diameter vent connector has a maximum capacity of 120000 Btu/h (35 kW) (which is too small for the furnace), and a 6 inch (152 mm) diameter vent connector has a maximum vent capacity of 172000 Btu/h (50 kW). Therefore, a 6 inch (152 mm) diameter vent connector shall be used with the 150000 Btu/h (44 kW) furnace. Since both vent connector horizontal lengths are less than the maximum lengths listed in Section 803.2.1, the table values shall be used without adjustments.

In the common vent capacity portion of Table 803.2(2), find the row associated with a 30 foot (9144 mm) vent height and read over to the NAT + NAT portion of the 6 inch (152 mm) diameter column to find a maximum combined capacity of 257000 Btu/h (75 kW). Since the two appliances total 185000 Btu/h (54 kW), a 6 inch (152 mm) common vent shall be used.

For SI units: 1 foot = 304.8 mm, 1000 British thermal units per hour = 0.293 kW

In this case, a 35000 Btu/h (10.3 kW) input
draft hood-equipped water heater with a 4 inch (102 mm)
diameter draft hood outlet, 2 feet (610 mm) of connector rise.
and 4 feet (1219 mm) of horizontal length is to be common
vented with a 100000 Btu/h (29 kW) fan-assisted furnace
with a 4 inch (102 mm) diameter flue collar, 3 feet (914 mm)
of connector rise, and 6 feet (1829 mm) of horizontal length.
The common vent consists of a 30 foot (9144 mm) height of
Type B vent. What are the recommended vent diameters for
each connector and the common vent? The installer would
like to use a single-wall metal vent connector. (See Figure F 102.2)

Solution:

Water Heater Vent Connector Diameter. Since the water heater vent connector horizontal length of 4 feet (1219 mm) is less than the maximum value listed in Table 803.2(2), the venting table values shall be used without adjustment. Using the Vent Connector Capacity portion of Table 803.2(2), read down the Total Vent Height (

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 803.2(2), read down the Total Vent Height (

The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted. Since the furnace vent connector horizontal length of 6 feet (1829 mm) is less than the maximum value listed in Section 803.2.1, the venting table values shall be used without adjustment. Where the furnace had an input rating of 80000 Btu/h (23.4 kW), then a Type B vent connector shall be needed in order to meet the minimum capacity limit.

Common Vent Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 803.2(2), read down the Vent Height (

Summary: In this example, the installer shall use a 4 inch (102 mm) diameter, single-wall metal vent connector for the water heater and a 4 inch (102 mm) diameter, single-wall metal vent connector for the furnace. The common vent shall be a 5 inch (127 mm) diameter Type B vent.

Solution:

Water Heater Vent Connector Diameter. Since the water heater vent connector horizontal length of 4 feet (1219 mm) is less than the maximum value listed in Table 803.2(2), the venting table values shall be used without adjustment. Using the Vent Connector Capacity portion of Table 803.2(2), read down the Total Vent Height (

*H*) column to 30 feet (9144 mm) and read across the 2 feet (610 mm) Connector Rise (*R*) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input rating of 37000 Btu/h (10.8 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 803.2.17. A 4 inch (102 mm) vent connector has a maximum input rating of 67000 Btu/h (19.6 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected. Since the water heater is equipped with a draft hood, there are no minimum input rating restrictions.Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 803.2(2), read down the Total Vent Height (

*H*) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (*R*) row. Since the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 119000 Btu/h (34.9 kW) and a minimum input rating of 85000 Btu/h (24.9 kW).The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted. Since the furnace vent connector horizontal length of 6 feet (1829 mm) is less than the maximum value listed in Section 803.2.1, the venting table values shall be used without adjustment. Where the furnace had an input rating of 80000 Btu/h (23.4 kW), then a Type B vent connector shall be needed in order to meet the minimum capacity limit.

Common Vent Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 803.2(2), read down the Vent Height (

*H*) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating equal to or exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 132000 Btu/h (39 kW) and the 5 inch (127 mm) common vent has a capacity of 202000 Btu/h (59 kW). Therefore, the 5 inch (127 mm) common vent shall be used in this example.Summary: In this example, the installer shall use a 4 inch (102 mm) diameter, single-wall metal vent connector for the water heater and a 4 inch (102 mm) diameter, single-wall metal vent connector for the furnace. The common vent shall be a 5 inch (127 mm) diameter Type B vent.

In this case, the water heater and fan-assisted furnace of Example 5(a) are to be common-vented
into a clay-tile-lined masonry chimney with a 30 foot (9144 mm) height. The chimney is not exposed to the outdoors below
the roof line. The internal dimensions of the clay tile liner are
nominally 8 inches (203 mm) by 12 inches (305 mm).
Assuming the same vent connector heights, laterals, and materials
found in Example 5(a), what are the recommended vent
connector diameters, and is this an acceptable installation?

Solution:

Table 803.2(4) is used to size common venting installations involving single-wall connectors into masonry chimneys.

Water Heater Vent Connector Diameter. Using Table 803.2(4), Vent Connector Capacity, read down the Vent Height (

Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 803.2(4), read down the total Vent Height (

Masonry Chimney. From Table F 102.3, the equivalent area for a nominal liner size of 8 inches (203 mm) by 12 inches (305 mm) is 63.6 of a square inches (0.041 m

Section 803.2.16 requires the common vent area to not exceed seven times the smallest listed appliance categorized vent area, flue collar area, or draft hood outlet area. Both appliances in this installation have 4 inch (102 mm) diameter outlets. From Table F 102.3, the equivalent area for an inside diameter of 4 inches (102 mm) is 12.2 of a square inches (0.008 m

Solution:

Table 803.2(4) is used to size common venting installations involving single-wall connectors into masonry chimneys.

Water Heater Vent Connector Diameter. Using Table 803.2(4), Vent Connector Capacity, read down the Vent Height (

*H*) column to 30 feet (9144 mm), and read across the 2 feet (610 mm) Connector Rise (*R*) row to the first Btu/h rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum input of 31000 Btu/h (9 kW), while a 4 inch (102 mm) vent connector has a maximum input of 57000 Btu/h (16.7 kW). A 4 inch (102 mm) vent connector shall be used.Furnace Vent Connector Diameter. Using the Vent Connector Capacity portion of Table 803.2(4), read down the total Vent Height (

*H*) column to 30 feet (9144 mm) and across the 3 feet (914 mm) Connector Rise (*R*) row. Because the furnace has a fan-assisted combustion system, find the first FAN Max column with a Btu/h rating exceeding the furnace input rating. The 4 inch (102 mm) vent connector has a maximum input rating of 127000 Btu/h (37 kW) and an input rating of not less than 95000 Btu/h (27.8 kW). The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted.Masonry Chimney. From Table F 102.3, the equivalent area for a nominal liner size of 8 inches (203 mm) by 12 inches (305 mm) is 63.6 of a square inches (0.041 m

^{2}). Using Table 803.2(4), Common Vent Capacity, read down the FAN + NAT column under the Minimum Internal Area of Chimney value of 63 to the row for 30 foot (9144 mm) height to find a capacity value of 739000 Btu/h (217 kW). The combined input rating of the furnace and water heater, 135000 Btu/h (40 kW), is less than the table value so this is an acceptable installation.Section 803.2.16 requires the common vent area to not exceed seven times the smallest listed appliance categorized vent area, flue collar area, or draft hood outlet area. Both appliances in this installation have 4 inch (102 mm) diameter outlets. From Table F 102.3, the equivalent area for an inside diameter of 4 inches (102 mm) is 12.2 of a square inches (0.008 m

^{2}). Seven times 12.2 equals 85.4, which is exceeding 63.6, so this configuration is acceptable.For SI units, 1 inch. = 25.4 mm, 1 square inch = 0.000645 m

^{2}^{*}Where liner sizes differ dimensionally from those shown in this table, equivalent diameters shall be permitted to be determined from published tables for square and rectangular ducts of equivalent carrying capacity or by other engineering methods.

In this case, the water heater and
fan-assisted furnace of Examples 5(a) and 5(b) are to be common-vented into an exterior masonry chimney. The
chimney height, clay-tile-liner dimensions, and vent connector
heights and laterals are the same as in Example 5(b). This
system is being installed in Charlotte, North Carolina. Does
this exterior masonry chimney need to be relined? Where so,
what corrugated metallic liner size is recommended? What
vent connector diameters are recommended? [see Table F 102.3 and Figure 803.1.2(6)]

Solution:

According to Section 803.2.19, Type B vent connectors are required to be used with exterior masonry chimneys. Use Table 803.2(8) and Table 803.2(9) to size FAN+NAT common venting installations involving Type-B double-wall connectors into exterior masonry chimneys.

The local 99 percent winter design temperature needed to use Table 803.2(8) and Table 803.2(9) shall be found in the ASHRAE Handbook - Fundamentals. For Charlotte, North Carolina, this design temperature is 19°F (-7.2°C).

Chimney Liner Requirement. As in Example 5(b), use the 63 square inch (0.04 m

According to Section 803.2.18, Table 803.2(1) or Table 803.2(2) are used for sizing corrugated metallic liners in masonry chimneys, with the maximum common vent capacities reduced by 20 percent. This example will be continued assuming Type B vent connectors.

Water Heater Vent Connector Diameter. Using Table 803.2(1) Connector Capacity, read down the total Vent Height (

Furnace Vent Connector Diameter. Using Table 803.2(1), Vent Connector Capacity, read down the total Vent Height (

Chimney Liner Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 803.2(1), read down the total Vent Height (

Single Wall Connectors. Once it has been established that relining the chimney is necessary, Type B double-wall vent connectors are not specifically required. This example shall be permitted to be redone using Table 803.2(2) for single-wall vent connectors. For this case, the vent connector and liner diameters would be the same as found for Type B double-wall connectors.

Solution:

According to Section 803.2.19, Type B vent connectors are required to be used with exterior masonry chimneys. Use Table 803.2(8) and Table 803.2(9) to size FAN+NAT common venting installations involving Type-B double-wall connectors into exterior masonry chimneys.

The local 99 percent winter design temperature needed to use Table 803.2(8) and Table 803.2(9) shall be found in the ASHRAE Handbook - Fundamentals. For Charlotte, North Carolina, this design temperature is 19°F (-7.2°C).

Chimney Liner Requirement. As in Example 5(b), use the 63 square inch (0.04 m

^{2}) column of Table 803.2(8) to the 30 foot (9144 mm) height row to find that the combined appliance maximum input is 747000 Btu/h (218.9 kW). The combined input rating of the appliance in this installation, 135000 Btu/h (40 kW), is less than the maximum value, so this criterion is satisfied. Table 803.2(9), at a 19°F (-7.2°C) design temperature, and at the same vent height and internal area used earlier, shows that the minimum allowable input rating of a space-heating appliance is 470000 Btu/h (137.7 kW). The furnace input rating of 100000 Btu/h (29 kW) is less than this minimum value. So this criterion is not satisfied, and an alternative venting design shall be used, such as a Type B vent shown in Example Sea) or a listed chimney liner system shown in the rest of the example.According to Section 803.2.18, Table 803.2(1) or Table 803.2(2) are used for sizing corrugated metallic liners in masonry chimneys, with the maximum common vent capacities reduced by 20 percent. This example will be continued assuming Type B vent connectors.

Water Heater Vent Connector Diameter. Using Table 803.2(1) Connector Capacity, read down the total Vent Height (

*H*) column to 30 feet (9144 mm), and read across the 2 feet (610 mm Connector Rise (*R*) row to the first Btu/hour rating in the NAT Max column that is equal to or exceeding the water heater input rating. The table shows that a 3 inch (76 mm) vent connector has a maximum capacity of 39000 Btu/h (11.4 kW). Although this rating is exceeding the water heater input rating, a 3 inch (76 mm) vent connector is prohibited by Section 803.2.19. A 4 inch (102 mm) vent connector has a maximum input rating of 70000 Btu/h (20.5 kW) and is equal to the draft hood outlet diameter. A 4 inch (102 mm) vent connector is selected.Furnace Vent Connector Diameter. Using Table 803.2(1), Vent Connector Capacity, read down the total Vent Height (

*H*) column to 30 feet (9144 mm), and read across the 3 feet (914 mm) Connector Rise (*R*) row to the first Btu/h rating in the FAN MAX column that is equal to or exceeding the furnace input rating. The 100000 Btu/h (29 kW) furnace in this example falls within this range, so a 4 inch (102 mm) connector shall be permitted.Chimney Liner Diameter. The total input to the common vent is 135000 Btu/h (40 kW). Using the Common Vent Capacity portion of Table 803.2(1), read down the total Vent Height (

*H*) column to 30 feet (9144 mm) and across this row to find the smallest vent diameter in the FAN + NAT column that has a Btu/h rating exceeding 135000 Btu/h (40 kW). The 4 inch (102 mm) common vent has a capacity of 138000 Btu/h (40.4 kW). Reducing the maximum capacity by 20 percent results in a maximum capacity for a 4 inch (102 mm) corrugated liner of 110000 Btu/h (32 kW), less than the total input of 135000 Btu/h (40 kW). So a larger liner is needed. The 5 inch (127 mm) common vent capacity listed in Table 803.2(1) is 210000 Btu/h (62 kW), and after reducing by 20 percent is 168000 Btu/h (49.2 kW). Therefore, a 5 inch (127 mm) corrugated metal liner shall be used in this example.Single Wall Connectors. Once it has been established that relining the chimney is necessary, Type B double-wall vent connectors are not specifically required. This example shall be permitted to be redone using Table 803.2(2) for single-wall vent connectors. For this case, the vent connector and liner diameters would be the same as found for Type B double-wall connectors.

Determine the required combination
of indoor and outdoor combustion air opening sizes for
the following appliance installation example.

Example Installation: A fan-assisted furnace and a draft hood-equipped water heater with the following inputs are located in a 15 foot by 30 foot (4572 mm by 9144 mm) basement with an 8 foot (2438 mm) ceiling. No additional indoor spaces shall be used to help meet the appliance combustion air needs.

Fan-Assisted Furnace Input: 100000 Btu/h (29 kW) Draft Hood-Equipped Water Heater Input: 40000 Btu/h (11.7 kW)

Solution:

For SI units: 1000 British thermal units per hour = 0.293 kW, 1 cubic foot =
0.0283 m

Example Installation: A fan-assisted furnace and a draft hood-equipped water heater with the following inputs are located in a 15 foot by 30 foot (4572 mm by 9144 mm) basement with an 8 foot (2438 mm) ceiling. No additional indoor spaces shall be used to help meet the appliance combustion air needs.

Fan-Assisted Furnace Input: 100000 Btu/h (29 kW) Draft Hood-Equipped Water Heater Input: 40000 Btu/h (11.7 kW)

Solution:

- Determine the total available room volume.

Appliance room volume.

15 feet by 30 feet (4572 mm by 9144 mm) with an 8 foot (2438 mm) ceiling = 3600 cubic feet (101.94 m^{3}) - Determine the total required volume.

The standard method to determine combustion air shall be used to calculate the required volume.

The combined input for the appliances located in the basement is calculated as follows:

100000 Btu/h (29 kW) + 40000 Btu/h (11.7 kW) = 140000 Btu/h (41 kW)

The standard method requires that the required volume be determined based on 50 cubic feet per 1000 Btu/h (4.83 m^{3}/kW).

Using Table F 103.0 the required volume for a 140000 Btu/h (41 kW) water heater is 7000 cubic feet (198.22 m^{3}).

Conclusion:

Indoor volume is insufficient to supply combustion air since the total of 3600 cubic feet (10 1.94 m^{3}) does not meet the required volume of 7000 cubic feet (198.22 m^{3}). Therefore, additional combustion air shall be provided from the outdoors. - Determine ratio of the available volume to the required volume.
- Detern1ine the reduction factor to be used to reduce the
full outdoor air opening size to the minimum required
based on ratio of indoor spaces.

1.0 -0.51 (from Step 3) = 0.49 - Determine the single outdoor combustion air opening size as if combustion air is to come from outdoors. In this example, the combustion air opening directly communicates with the outdoors.
- Determine the minimum outdoor combustion air opening area. Section 701.7.3(3) requires the minimum dimension of the air opening shall be not less than 3 inches (76 mm).

APPLIANCE INPUT(Btu/h) |
REQUIRED VOLUME(cubic feet) |

5000 | 250 |

10000 | 500 |

15000 | 750 |

20000 | 1000 |

25000 | 1250 |

30000 | 1500 |

35000 | 1750 |

40000 | 2000 |

45000 | 2250 |

50000 | 2500 |

55000 | 2750 |

60000 | 3000 |

65000 | 3250 |

70000 | 3500 |

75000 | 3750 |

80000 | 4000 |

85000 | 4250 |

90000 | 4500 |

95000 | 4750 |

100000 | 5000 |

105000 | 5250 |

110000 | 5500 |

115000 | 5750 |

120000 | 6000 |

125000 | 6250 |

130000 | 6500 |

135000 | 6750 |

140000 | 7000 |

145000 | 7250 |

150000 | 7500 |

160000 | 8000 |

170000 | 8500 |

180000 | 9000 |

190000 | 9500 |

200000 | 10000 |

210000 | 10500 |

220000 | 11000 |

230000 | 11500 |

240000 | 12000 |

250000 | 12500 |

260000 | 13000 |

270000 | 13500 |

280000 | 14000 |

290000 | 14500 |

300000 | 15000 |

^{3}