Required occupancy separations of more than one hour may be reduced to one-hour fire-resistive construction with all openings protected by not less than three-fourths-hour fire-resistive assemblies of the self-closing or automatic-closing type when the building is provided with an automatic sprinkler system throughout the entire building in accordance with Section 8-410.2. Doors equipped with automatic-closing devices shall be of a type which will function upon activation of a device which responds to products of combustion other than heat.
Required occupancy separations of one hour may be omitted when the building is provided with an automatic sprinkler system throughout.
Regardless of the use or character of occupancy, the area of a one-story qualified historical building or property may have, but shall not exceed, a floor area of 15,000 square feet (1393.5 m2) unless such an increase is otherwise permitted in regular code. Multistory qualified historical buildings (including basements and cellars) shall be in accordance with regular code requirements.
Exception: Historical buildings may be unlimited in floor area without fire-resistive area separation walls:
- When provided with an automatic sprinkler, or
- Residential occupancies of two stories or less when provided with a complete fire alarm and annunciation system and where the exiting system conforms to regular code.
Occupancies B, F-1, F-2 or S in high-rise buildings with floors located more than 75 feet above the lowest floor level having building access may be permitted with only the stories over 75 feet provided with an automatic fire sprinkler system if:
- The building construction type and the exits conform to regular code, and
- A complete building fire alarm and annunciation system is installed, and
- A fire barrier is provided between the sprinklered and nonsprinklered floors.
The alteration and repair of qualified historical buildings or properties may permit the replacement, retention and extension of original materials and the continued use of original methods of construction, provided a life-safety hazard is not created or continued. Alterations and repairs shall be consistent with the CHBC.
The amount of alterations and repairs is not limited, provided there is no nonhistorical increase in floor area, volume or size of the building or property.