CALIFORNIA FIRE CODE — MATRIX ADOPTION TABLE
CHAPTER 30 — INDUSTRIAL OVENS
|Adopt Entire Chapter||X|
|Adopt Entire Chapter as |
amended (amendedsections listed below)
|Adopt only those |
sections that arelisted below
|[California Code of |
Regulations, Title 19,Division 1]
|Chapter / Section|
* The California Code of Regulations (CCR), Title 19, Division 1 provisions that are found in the California Fire Code are a reprint from the current CCR, Title 19, Division 1 text for the code user's convenience only. The scope, applicability and appeals procedures of CCR, Title 19, Division I remain the same.
Valves for fuel supply lines shall be located within 6 feet (1829 mm) of the appliance served.
Exception: Where approved and the valve is located in the same general area as the appliance served.
Safety data for Class A solvent atmosphere ovens shall be furnished on the manufacturer's nameplate. The nameplate shall provide the following design data:
- The solvent used.
- The number of gallons (L) used per batch or per hour of solvent entering the oven.
- The required purge time.
- The oven operating temperature.
- The exhaust blower rating for the number of gallons (L) of solvent per hour or batch at the maximum operating temperature.
Exception: For low-oxygen ovens, the maximum allowable oxygen concentration shall be included in place of the exhaust blower ratings.