|Adopt Entire Chapter|
|Adopt Entire Chapter as amended (amended sections listed below)||X|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19, Division 1]|
|Chapter / Section|
In addition to the requirements of Section 507.5.1 of the California Fire Code, fire hydrants shall be provided in accordance with this appendix for the protection of buildings, or portions of buildings, hereafter constructed or moved into the jurisdiction.
Exception: [SFM] Group B, S-2 and U occupancies having a floor area not exceeding 1,000 square feet, primarily constructed of noncombustible exterior walls with wood or steel roof framing, having a Class A roof assembly, with uses limited to the following or similar uses:
The number of fire hydrants available to a building shall be not less than the minimum specified in Table C102.1.
REQUIRED NUMBER AND SPACING OF FIRE HYDRANTS
|FIRE-FLOW REQUIREMENT (gpm)||MINIMUM NUMBER OF HYDRANTS||AVERAGE SPACING BETWEEN HYDRANTSa, b, c, f, g (feet)||MAXIMUM DISTANCE FROM ANY POINT ON STREET OR ROAD FRONTAGE TO A HYDRANTd, f, g|
|1,750 or less||1||500||250|
|7,500 or more||8 or moree||200||120|
For SI: 1 foot = 304.8 mm, 1 gallon per minute = 3.785 L/m.
- Reduce by 100 feet for dead-end streets or roads.
- Where streets are provided with median dividers that cannot be crossed by fire fighters pulling hose lines, or where arterial streets are provided with four or more traffic lanes and have a traffic count of more than 30,000 vehicles per day, hydrant spacing shall average 500 feet on each side of the street and be arranged on an alternating basis.
- Where new water mains are extended along streets where hydrants are not needed for protection of structures or similar fire problems, fire hydrants shall be provided at spacing not to exceed 1,000 feet to provide for transportation hazards.
- Reduce by 50 feet for dead-end streets or roads.
- One hydrant for each 1,000 gallons per minute or fraction thereof.
- A 50-percent spacing increase shall be permitted where the building is equipped throughout with an approved automatic sprinkler system in accordance with Section 903.3.1.1 of the California Fire Code.
- A 25-percent spacing increase shall be permitted where the building is equipped throughout with an approved automatic sprinkler system in accordance with Section 903.3.1.2 or 903.3.1.3 of the California Fire Code or Section P2904 of the California Residential Code.