|Adopt Entire Chapter||X|
|Adopt Entire Chapter as amended (amended sections listed below)|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19, Division 1]|
|Chapter / Section|
Indoor storage of organic peroxides in amounts exceeding the maximum allowable quantity per control area indicated in Table 5003.1.1(1) shall be in accordance with Sections 5001, 5003, 5004 and this chapter.
Indoor storage of unclassified detonable organic peroxides that are capable of detonation in their normal shipping containers under conditions of fire exposure shall be stored in accordance with Chapter 56.
In addition to the requirements of the California Building Code, detached storage buildings for Class I, II, III, IV and V organic peroxides shall be located in accordance with Table 6204.1.2. Detached buildings containing quantities of unclassified detonable organic peroxides in excess of those set forth in Table 5003.8.2 shall be located in accordance with Table 5604.5.2(1).
ORGANIC PEROXIDES—DISTANCE TO EXPOSURES FROM DETACHED STORAGE BUILDINGS OR OUTDOOR STORAGE AREAS
|ORGANIC PEROXIDE CLASS||MAXIMUM STORAGE QUANTITY (POUNDS) AT MINIMUM SEPARATION DISTANCE|
|Distance to buildings, lot lines, public streets, public alleys, public ways or means of egress||Distance between individual detached storage buildings or individual outdoor storage areas|
|50 feet||100 feet||150 feet||20 feet||75 feet||100 feet|
|II||100,000||200,000||No Limit||100,000a||No Limit||No Limit|
|III||200,000||No Limit||No Limit||200,000a||No Limit||No Limit|
|IV||No Limit||No Limit||No Limit||No Limit||No Limit||No Limit|
|V||No Limit||No Limit||No Limit||No Limit||No Limit||No Limit|
For SI: 1 foot = 304.8 mm, 1 pound = 0.454 kg.
- Where the amount of organic peroxide stored exceeds this amount, the minimum separation shall be 50 feet.
An approved supervised smoke detection system in accordance with Section 907 shall be provided in rooms or areas where Class I, II or III organic peroxides are stored. Activation of the smoke detection system shall sound a local alarm.
- Containers and packages in storage areas shall be closed.
- Bulk storage shall not be in piles or bins.
- A minimum 2-foot (610 mm) clear space shall be maintained between storage and uninsulated metal walls.
- Fifty-five-gallon (208 L) drums shall not be stored more than one drum high.
STORAGE OF ORGANIC PEROXIDES
|ORGANIC PEROXIDE CLASS||PILE CONFIGURATION||MAXIMUM QUANTITY PER BUILDING|
|Maximum width (feet)||Maximum height (feet)||Minimum distance to next pile (feet)||Minimum distance to walls (feet)|
|IV||16||10||3a, d||4b||No Requirement|
|V||No Requirement||No Requirement||No Requirement||No Requirement||No Requirement|