|Adopt Entire Chapter|
|Adopt Entire Chapter as amended (amended sections listed below)||X|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19,Division 1]||X|
|Chapter / Section|
|[T-19 §3.05 (a)]||X|
|[T-19 §3.05 (b)]||X|
- The fire code official is authorized to increase the dimension of 150 feet (45 720 mm) where any of the following conditions occur:
- 1.1. The building is equipped throughout with an approved automatic sprinkler system installed in accordance with Section 903.3.1.1, 903.3.1.2 or 903.3.1.3.
- 1.2. Fire apparatus access roads cannot be installed because of location on property, topography, waterways, nonnegotiable grades or other similar conditions, and an approved alternative means of fire protection is provided.
- 1.3. There are not more than two Group R-3 or Group U occupancies.
- Where approved by the fire code official, fire apparatus access roads shall be permitted to be exempted or modified for solar photovoltaic power generation facilities.
- Roads. Required access roads from every building to a public street shall be all-weather hard-surfaced (suitable for use by fire apparatus) right-of-way not less than 20 feet in width. Such right-of-way shall be unobstructed and maintained only as access to the public street.Exception: The enforcing agency may waive or modify this requirement if in his opinion such all-weather hard-surfaced condition is not necessary in the interest of public safety and welfare.
- The key box shall be compatible with an existing rapid entry key box system in use in the jurisdiction and approved by the fire code official.
- The front cover shall be permanently labeled with the words "Fire Department Use Only—Elevator Keys."
- The key box shall be mounted at each elevator bank at the lobby nearest to the lowest level of fire department access.
- The key box shall be mounted 5 feet 6 inches (1676 mm) above the finished floor to the right side of the elevator bank.
- Contents of the key box are limited to fire service elevator keys. Additional elevator access tools, keys and information pertinent to emergency planning or elevator access shall be permitted where authorized by the fire code official.
- In buildings with two or more elevator banks, a single key box shall be permitted to be used where such elevator banks are separated by not more than 30 feet (9144 mm). Additional key boxes shall be provided for each individual elevator or elevator bank separated by more than 30 feet (9144 mm).
- The emergency voice/alarm communication system control unit.
- The fire department communications system.
- Fire alarm system zoning annunciator panel required by Section 907.6.4.3.
- Annunciator unit visually indicating the location of the elevators and whether they are operational.
- Status indicators and controls for air distribution systems.
- The fire fighter's control panel required by Section 909.16 for smoke control systems installed in the building.
- Controls for unlocking interior exit stairway doors simultaneously.
- Sprinkler valve and water-flow detector display panels.
- Emergency and standby power status indicators.
- A telephone for fire department use with controlled access to the public telephone system.
- Fire pump status indicators.
- Schematic building plans indicating the typical floor plan and detailing the building core, means of egress, fire protection systems, fire-fighter air-replenishment systems, fire-fighting equipment and fire department access, and the location of fire walls, fire barriers, fire partitions, smoke barriers and smoke partitions.
- An approved Building Information Card that includes, but is not limited to, all of the following information:
- 13.1. General building information that includes: property name, address, the number of floors in the building above and below grade, use and occupancy classification (for mixed uses, identify the different types of occupancies on each floor) and the estimated building population during the day, night and weekend;
- 13.2. Building emergency contact information that includes: a list of the building's emergency contacts including but not limited to building manager, building engineer and their respective work phone number, cell phone number and e-mail address;
- 13.3. Building construction information that includes: the type of building construction including but not limited to floors, walls, columns and roof assembly;
- 13.4. Exit access stairway and exit stairway information that includes: number of exit access stairways and exit stairways in building; each exit access stairway and exit stairway designation and floors served; location where each exit access stairway and exit stairway discharges, interior exit stairways that are pressurized; exit stairways provided with emergency lighting; each exit stairway that allows reentry; exit stairways providing roof access; elevator information that includes: number of elevator banks, elevator bank designation, elevator car numbers and respective floors that they serve; location of elevator machine rooms, control rooms and control spaces; location of sky lobby; and location of freight elevator banks;
- 13.5. Building services and system information that includes: location of mechanical rooms, location of building management system, location and capacity of all fuel oil tanks, location of emergency generator and location of natural gas service;
- 13.6. Fire protection system information that includes: location of standpipes, location of fire pump room, location of fire department connections, floors protected by automatic sprinklers and location of different types of automatic sprinkler systems installed including but not limited to dry, wet and pre-action;
- 13.7. Hazardous material information that includes: location and quantity of hazardous material.
- Work table.
- Generator supervision devices, manual start and transfer features.
- Public address system, where specifically required by other sections of this code.
- Elevator fire recall switch in accordance with California Code of Regulations, Title 8, Division 1, Chapter 4, Subchapter 6, Elevator Safety Orders.
- Elevator emergency or standby power selector switch(es), where emergency or standby power is provided.
- A master switch for unlocking elevator lobby doors permitted by Section 1010.1.9.10.
- Where approved by the building official and the fire code official, a wired communication system in accordance with Section 907.2.13.2 shall be permitted to be installed or maintained instead of an approved radio coverage system.
- Where it is determined by the fire code official that the radio coverage system is not needed.
- In facilities where emergency responder radio coverage is required and such systems, components or equipment required could have a negative impact on the normal operations of that facility, the fire code official shall have the authority to accept an automatically activated emergency responder radio coverage system.
- All signal booster components shall be contained in a National Electrical Manufacturer's Association (NEMA) 4-type waterproof cabinet.
- Battery systems used for the emergency power source shall be contained in a NEMA 4-type waterproof cabinet.
- The signal booster system and battery system shall be electrically supervised and monitored by a supervisory service, or when approved by the fire code official, shall sound an audible signal at a constantly attended location
- Equipment shall have FCC certification prior to installation.
- A valid FCC-issued general radio operators license.
- Certification of in-building system training issued by a nationally recognized organization, school or a certificate issued by the manufacturer of the equipment being installed.
- Each floor of the building shall be divided into a grid of 20 approximately equal test areas.
- The test shall be conducted using a calibrated portable radio of the latest brand and model used by the agency talking through the agency's radio communications system.
- Failure of not more than two nonadjacent test areas shall not result in failure of the test.
- In the event that three of the test areas fail the test, in order to be more statistically accurate, the floor shall be permitted to be divided into 40 equal test areas. Failure of not more than four nonadjacent test areas shall not result in failure of the test. If the system fails the 40-area test, the system shall be altered to meet the 90-percent coverage requirement.
- A test location approximately in the center of each test area shall be selected for the test, with the radio enabled to verify two-way communications to and from the outside of the building through the public agency's radio communications system. Once the test location has been selected, that location shall represent the entire test area. Failure in the selected test location shall be considered failure of that test area. Additional test locations shall not be permitted.
- The gain values of all amplifiers shall be measured and the test measurement results shall be kept on file with the building owner so that the measurements can be verified during annual tests. In the event that the measurement results become lost, the building owner shall be required to rerun the acceptance test to reestablish the gain values.
- As part of the installation a spectrum analyzer or other suitable test equipment shall be utilized to ensure spurious oscillations are not being generated by the subject signal booster. This test shall be conducted at the time of installation and subsequent annual inspections.
- In-building coverage test as described in Section 510.5.3.
- Signal boosters shall be tested to verify that the gain is the same as it was upon initial installation and acceptance.
- Backup batteries and power supplies shall be tested under load of a period of 1 hour to verify that they will properly operate during an actual power outage. If within the 1-hour test period the battery exhibits symptoms of failure, the test shall be extended for additional 1-hour periods until the integrity of the battery can be determined.
- Other active components shall be checked to verify operation within the manufacturer's specifications.
- At the conclusion of the testing, a report, which shall verify compliance with Section 510.5.3, shall be submitted to the fire code official.