Where rubbish containers with a capacity exceeding 5.33 cubic feet (40 gallons) (0.15 m3) are used for temporary storage of combustible debris, rubbish and waste material, they shall have tight-fitting or self-closing lids. Such rubbish containers shall be constructed entirely of materials that comply with either of the following:
- Noncombustible materials.
- Materials that meet a peak rate of heat release not exceeding 300 kW/m2 when tested in accordance with ASTM E1354 at an incident heat flux of 50 kW/m2 in the horizontal orientation.
The cleaning and purging of flammable gas piping systems, including cleaning new or existing piping systems, purging piping systems into service and purging piping systems out of service, shall comply with NFPA 56.
Required means of egress shall be maintained during construction and demolition, remodeling or alterations and additions to any building.
Exception: Approved temporary means of egress systems and facilities.
Structures under construction, alteration or demolition shall be provided with not less than one approved portable fire extinguisher in accordance with Section 906 and sized for not less than ordinary hazard as follows:
- At each stairway on all floor levels where combustible materials have accumulated.
- In every storage and construction shed.
- Additional portable fire extinguishers shall be provided where special hazards exist including, but not limited to, the storage and use of flammable and combustible liquids.
Internal-combustion-powered construction equipment shall be used in accordance with all of the following conditions:
- Equipment shall be located so that exhausts do not discharge against combustible material.
- Exhausts shall be piped to the outside of the building.
- Equipment shall not be refueled while in operation.
- Fuel for equipment shall be stored in an approved area outside of the building.