Heads up: There are no amended sections in this chapter.
|Adopt Entire Chapter||X|
|Adopt Entire Chapter as amended (amended sections listed below)|
|Adopt only those sections that are listed below|
|[California Code of Regulations, Title 19, Division 1]|
|Chapter / Section|
* The California Code of Regulations (CCR), Title 19, Division 1 provisions that are found in the California Fire Code are a reprint from the current CCR, Title 19, Division 1 text for the code user's convenience only. The scope, applicability and appeals procedures of CCR, Title 19, Division I remain the same.
The equipment, processes and operations involving dust explosion hazards shall comply with the provisions of this chapter.
Accumulation of combustible dust shall be kept to a minimum in the interior of buildings. Accumulated combustible dust shall be collected by vacuum cleaning or other means that will not place combustible dust into suspension in air. Forced air or similar methods shall not be used to remove dust from surfaces.
EXPLOSION PROTECTION STANDARDS
|NFPA 61||Agricultural and Food Products|
|NFPA 69||Explosion Prevention|
|NFPA 70||National Electrical Code|
|NFPA 85||Boiler and Combustion System Hazards|
|NFPA 120||Coal Preparation Plants|
|NFPA 484||Combustible Metals|
|NFPA 654||Manufacturing, Processing and Handling of Combustible Particulate Solids|
|NFPA 655||Prevention of Sulfur Fires and Explosions|
|NFPA 664||Prevention of Fires and Explosions in Wood Processing and Woodworking Facilities|