|Adopt entire chapter|
|Adopt entire chapter as amended (amended sections listed below)||X|
|Adopt only those sections that are listed below|
|Chapter / Section|
The Office of the State Fire Marshal’s adoption of this chapter or individual sections is applicable to structures regulated by other state agencies pursuant to Section 1.11.
- The net free area of the spark arrestor shall be not less than four times the net free area of the outlet of the chimney.
- The spark arrestor screen shall have heat and corrosion resistance equivalent to 19-gage galvanized steel or 24-gage stainless steel.
- Openings shall not permit the passage of spheres having a diameter larger than 1/2 inch (12.7 mm) nor block the passage of spheres having a diameter of less than 3/8 inch (9.5 mm).
- The spark arrestor shall be accessible for cleaning and the screen or chimney cap shall be removable to allow for cleaning of the chimney flue.