Heads up: There are no suggested sections in this chapter.
Heads up: There are no amended sections in this chapter.
Flammable solids stored in quantities greater than 1,000 cubic feet (28 m3) shall be separated into piles each not larger than 1,000 cubic feet (28 m3).
Aisle widths between piles shall not be less than the height of the piles or 4 feet (1219 mm), whichever is greater.
Outdoor storage of flammable solids shall not be located within 20 feet (6096 mm) of a building, lot line, public street, public alley, public way or means of egress. A 2-hour fire barrier without openings or penetrations and extending 30 inches (762 mm) above and to the sides of the storage area is allowed in lieu of such distance. The wall shall either be an independent structure, or the exterior wall of the building adjacent to the storage area.
Magnesium storage in quantities greater than 1,000 cubic feet (28 m3) shall be separated into piles not larger than 1,000 cubic feet (28 m3) each. Piles shall be separated by aisles with a minimum width of not less than the pile height. Such storage shall not be located in nonsprinklered buildings of Type III, IV or V construction, as defined in the International Building Code.
Outdoor storage of magnesium pigs, ingots and billets shall be in piles not exceeding 1,000,000 pounds (453.6 metric tons) each. Piles shall be separated by aisles with a minimum width of not less than one-half the pile height. Piles shall be separated from combustible materials or buildings on the same or adjoining property by a distance of not less than the height of the nearest pile.
Storage of fine magnesium scrap in quantities greater than 50 cubic feet (1.4 m3) [six 55-gallon (208 L) steel drums] shall be separated from other occupancies by an open space of at least 50 feet (15 240 mm) or by a fire barrier constructed in accordance with Section 707 of the International Building Code.
Floors under and around melting pots shall be of noncombustible construction.
Approved means shall be provided for control of magnesium fires in heat-treating ovens.
Magnesium grinding, buffing and wire-brushing operations, other than rough finishing of castings, shall be provided with approved hoods or enclosures for dust collection which are connected to a liquid-precipitation type of separator that converts dust to sludge without contact (in a dry state) with any high-speed moving parts.
Connecting ducts or suction tubes shall be completely grounded, as short as possible, and without bends. Ducts shall be fabricated and assembled with a smooth interior, with internal lap joints pointing in the direction of airflow and without unused capped side outlets, pockets or other dead-end spaces which allow an accumulation of dust.
Each machine shall be equipped with an individual dust-separating unit.
- One separator is allowed to serve two dust-producing units on multiunit machines.
- One separator is allowed to serve not more than four portable dust-producing units in a single enclosure or stand.
Electric wiring, fixtures and equipment in the immediate vicinity of and attached to dust-producing machines, including those used in connection with separator equipment, shall be of approved types and shall be approved for use in Class II, Division 1 hazardous locations in accordance with NFPA 70.
Equipment shall be securely grounded by permanent ground wires in accordance with NFPA 70.
Fire-extinguishing materials shall be provided for every operator performing machining, grinding or other processing operation on magnesium as follows:
- Within 30 feet (9144 mm), a supply of extinguishing materials in an approved container with a hand scoop or shovel for applying the material; or
- Within 75 feet (22 860 mm), a portable fire extinguisher complying with Section 906.
All extinguishing materials shall be approved for use on magnesium fires. Where extinguishing materials are stored in cabinets or other enclosed areas, the enclosures shall be openable without the use of a key or special knowledge.