1. Not be directly connected to the drainage system.<p> 2. Discharge through an air gap</i> located in the same room as the water heater. <p> 3. Not be smaller than the diameter of the outlet of the valve served and shall discharge full size to the air gap</i>. p>
4. Serve a single relief device and shall not connect to piping serving any other relief device or equipment.
6. Discharge in a manner that does not cause personal injury or structural damage.
7. Discharge to a termination point that is readily observable by the building occupants.
8. Not be trapped.
9. Be installed so as to flow by gravity.
10. Not terminate more than 6 inches (152 mm) above the floor or waste receptor.
11. Not have a threaded connection at the end of such piping.
12. Not have valves or tee fittings.
13. Be constructed of those materials listed in Section 605.4 or materials tested, rated and approved for such use in accordance with ASME A112.4.1.