C403.2.4.4 Zone Isolation
HVAC systems serving zones that are over 25,000 square feet (2323 m2) in floor area or that span more than one floor and are designed to operate or be occupied nonsimultaneously shall be divided into isolation areas. Each isolation area shall be equipped with isolation devices and controls configured to automatically shut off the supply of conditioned air and outdoor air to and exhaust air from the isolation area. Each isolation area shall be controlled independently by a device meeting the requirements of Section C403.2.4.2.2. Central systems and plants shall be provided with controls and devices that will allow system and equipment operation for any length of time while serving only the smallest isolation area served by the system or plant.
- Exhaust air and outdoor air connections to isolation areas where the fan system to which they connect is not greater than 5,000 cfm (2360 L/s).
- Exhaust airflow from a single isolation area of less than 10 percent of the design airflow of the exhaust system to which it connects.
- Isolation areas intended to operate continuously or intended to be inoperative only when all other isolation areas in a zone are inoperative.