// CODE SNIPPET
P-1107.1.1 Yoke Venting Offsets
JUMP TO FULL CODE CHAPTER
Such offsets shall be provided with a yoke vent equal to one-half the diameter of the vent stack or soil stack but not less than 1-1/2 inches. The lower end of the yoke vent shall connect to the soil or waste stack through a wye below the offset and above the next lower horizontal branch, and the upper end shall connect to the stack vent or the vent stack not less than 6 inches above the highest fixture.
Related Code Sections
P-1107.1.1 Vents and Venting, Yoke Venting Offsets
Such offsets shall be provided with a yoke vent equal to one-half the diameter of the vent stack or soil stack but not less than 1-1/2 inches. The ...
Philadelphia Plumbing Code > 11 Vents and Venting > P-1107 Venting of Offsets > P-1107.1 Stack Offsets > P-1107.1.1 Yoke Venting Offsets
907.3 Vents, Lower Section
The lower section of the drainage stack shall be vented by a yoke vent connecting between the offset and the next lower horizontal branch . The ...
503.6.10.2 Chimneys and Vents, Vent Offsets
Type B and L vents sized in accordance with Item 2 or 3 of Section 503.6.10.1 shall extend in a generally vertical direction with offsets ...
2018 Philadelphia Fuel Gas Code > 5 Chimneys and Vents > 503 (IFGS) Venting of Appliances > 503.6 Gas Vents > 503.6.10 Size of Gas Vents > 503.6.10.2 Vent Offsets
504.2.3 Chimneys and Vents, Vent Offsets
Where multiple offsets occur in a vent, the total lateral length of all offsets combined shall not exceed that specified in Tables 504.2(1) through 504.2 ...
2018 Philadelphia Fuel Gas Code > 5 Chimneys and Vents > 504 (IFGS) Sizing of Category I Appliance Venting Systems > 504.2 Application of Single-Appliance Vent Tables 504.2(1) Through 504.2(6) > 504.2.3 Vent Offsets