// CODE SNIPPET
319.6.2 Yard Hydrant System
JUMP TO FULL CODE CHAPTER
Fire apparatus-accessible locations as required by FC319.7.1 shall be within 250 feet (76 200 mm) of a fire hydrant or other approved water supply, and shall be situated such that a hose stream from 250 feet (76 200 mm) of hose line stretched from such location will reach all portions of the premises.
Related Code Sections
§27-933 Fire Alarm, Detection and Extinguishing Equipment, Yard Hydrant Systems Required
exists. (d) Standpipes and sprinkler systems may be connected to a yard hydrant system in accordance with the requirements of this subchapter. (e ...
NYC 1968 Code (Vol I) > 17 Fire Alarm, Detection and Extinguishing Equipment > 3 Standpipe Requirements > §27-933 Yard Hydrant Systems Required
Article 17 Standpipe Systems [PDF] (page 15)
hundred seventy-five pounds per square inch. Sub-Article 9. Yard Hydrant Systems (16.9). §C26-1428.0 Yard Hydrant Systems.a. Shipyards, oil storage plants ...
Article 17 Standpipe Systems [PDF] (page 1)
ARTICLE 17. STANDPIPE SYSTEMS Sub-Article 1. General Provisions Governing Standpipe Systems (16.1.1). §C26-1381.0 Standpipe and Yard Hydrant Systems ...
901.4 Fire Protection Systems, Threads
Threads provided for Fire Department connections to sprinkler systems, standpipes, yard hydrants or any other fire hose connection shall ...