// CODE SNIPPET
(C) Wired Luminaire Sections
JUMP TO FULL CODE CHAPTER
Wired luminaire sections are paired, with a ballast(s) or LED driver(s) supplying a light source or light sources in both. For interconnection between paired units, it shall be permissible to use metric designator 12 (trade size 3/8) flexible metal conduit in lengths not exceeding 7.5 m (25 ft), in conformance with Article 348. Luminaire wire operating at line voltage, supplying only the ballast(s) or LED driver(s) of one of the paired luminaires, shall be permitted in the same raceway as the light source supply wires of the paired luminaires where the voltage rating of the light source supply wires is greater than the line voltage.
Related Code Sections
(C) Equipment for General Use, Wired Luminaire Sections
Wired luminaire sections are paired, with a ballast(s) or LED driver(s) supplying a light source or light sources in both. For interconnection ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.137 Equipment Not Integral With Luminaire > (C) Wired Luminaire Sections
(A) Wiring Methods and Materials, Minimum
manufactured wiring systems as permitted in 604.100(A) In hoistways as permitted in 620.21(A)(1) As part of a listed assembly to connect wired luminaire ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 348 Flexible Metal Conduit: Type FMC > 348.20 Size > (A) Minimum
(B) Wiring and Protection, Branch-Circuit Overcurrent Device
of this section, a luminaire may be either portable or permanent ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.5 Protection of Flexible Cords, Flexible Cables, and Fixture Wires > (B) Branch-Circuit Overcurrent Device