// CODE SNIPPET
(6) Wire Harness and Exposed Cable Arc-Fault Protection
Related Code Sections
(6) Special Conditions, Wire Harness and Exposed Cable Arc-Fault Protection
A utility-interactive inverter(s) that has a wire harness or cable output circuit rated 240 V, 30 amperes, or less, that is not installed within ...
National Electrical Code 2014 of Alabama > 7 Special Conditions > 705 Interconnected Electric Power Production Sources > 705.12 Point of Connection > (D) Utility-Interactive Inverters > (6) Wire Harness and Exposed Cable Arc-Fault Protection
210.12 Wiring and Protection, Arc-Fault Circuit-Interrupter Protection
Arc-fault circuit-interrupter protection shall be provided as required in 210.12(A) (B), and (C). The arc-fault circuit interrupter shall ...
National Electrical Code 2014 of Alabama > 2 Wiring and Protection > 210 Branch Circuits > 210.12 Arc-Fault Circuit-Interrupter Protection
E3902.16 Power and Lighting Distribution, Arc-Fault Circuit-Interrupter Protection
of the following: [210.12(A)] A listed combination-type arc-fault circuit interrupter, installed to provide protection of the entire branch circuit ...
Residential Code 2015 of Alabama > 39 Power and Lighting Distribution > E3902 Ground-Fault and Arc-Fault Circuit-Interrupter Protection > E3902.16 Arc-Fault Circuit-Interrupter Protection
(B) Special Occupancies, Temporary Wiring
590. Flexible cables and cords approved for hard or extra-hard usage shall be permitted to be laid on floors where protected from contact by the general ...
National Electrical Code 2014 of Alabama > 5 Special Occupancies > 518 Assembly Occupancies > 518.3 Other Articles > (B) Temporary Wiring
E3802.3 Wiring Methods, Exposed Cable
In exposed work, except as provided for in Sections E3802.2 and E3802.4, cable assemblies shall be installed as specified in Sections E3802.3.1 ...
Residential Code 2015 of Alabama > 38 Wiring Methods > E3802 Above-Ground Installation Requirements > E3802.3 Exposed Cable