For the purpose of Section 446, certain terms are defined as follows:
- TYPE 1 WINERY CAVES are natural or manmade caves used solely for storage and/or processing of wine at a winery facility. Type 1 winery caves are not accessible to the public.
- TYPE 2 WINERY CAVES are natural or manmade caves used for the storage and/or processing of wine at a winery facility. Type 2 winery caves are accessible to the public on guided tours only.
- TYPE 3 WINERY CAVES are natural or manmade caves used for the storage and/or processing of wine at a winery facility. Type 3 winery caves are accessible to the public on guided tours and contain assembly use areas.
Tours for the public shall be continuously guided by staff knowledgeable in the location of exits and the use of emergency notification devices.
Per the California Fire Code,Section 2404.20, when, in the opinion of the fire chief, it is essential for public safety, the owner, agent or lessee shall employ one or more qualified persons, as required and approved by the chief, to be on duty at such place. Such individuals shall be in uniform or otherwise easily identifiable.
Standby personnel shall be subject to the fire chief’s orders at all times when so employed and shall remain on duty during the times such places are open to the public or when such activity is being conducted.
Before the start of any activity requiring standby personnel, such individuals shall:
- Inspect the required fire appliances to ensure they are in the proper place and in good working order.
- Inspect all exits to verify accessibility and proper operation.
While on duty, such individuals shall not be required or permitted to perform any duties other than those specified by the fire chief.
The use of candles and other open-flame devices shall be in accordance with California Fire Code Section 308.1.7.
Portable fire extinguishers shall be located to be readily accessible. Its type, location and spacing throughout the facility shall be in accordance with the provisions of Title 19, Chapter 3 and California Fire Code Section 906.1. Other fire appliances shall be maintained at the site as required by the fire chief.
Exits shall be located remotely from each other and arranged to minimize any possibility that more than one may be blocked off by any one fire or other emergency condition.
The power supply for exit illumination may be provided by the premises’ wiring system. In the event of its failure, illumination shall be automatically provided from an emergency system in Types 2 and 3 winery caves. Emergency systems shall be supplied from storage batteries or an on-site generator set, and the system shall be installed in accordance with the requirements of the California Electrical Code.