// CODE SNIPPET
Section P2720 Whirlpool Bathtubs
JUMP TO FULL CODE CHAPTER
Access shall be provided to circulation pumps in accordance with the fixture or pump manufacturer's installation instructions. Where the manufacturer's instructions do not specify the location and minimum size of field-fabricated access openings, an opening of not less than 12 inches by 12 inches (305 mm by 305 mm) shall be installed for access to the circulation pump. Where pumps are located more than 2 feet (610 mm) from the access opening, an opening of not less than 18 inches by 18 inches (457 mm by 457 mm) shall be installed. A door or panel shall be permitted to close the opening. The access opening shall be unobstructed and be of the size necessary to permit the removal and replacement of the circulation pump.
Leak testing and pump operation shall be performed in accordance with the manufacturer's instructions.
The product shall be installed in accordance with the manufacturer's instructions.