// CODE SNIPPET
(A) Where GFCI Protection Is Required
JUMP TO FULL CODE CHAPTER
In addition to the requirements of 210.8(B), GFCI protection for personnel shall be provided for the following:
- All 125-volt, single-phase, 15- and 20-ampere non-locking-type receptacles used for disassembly and reassembly or readily accessible to the general public
- Equipment that is readily accessible to the general public and supplied from a 125-volt, single-phase, 15- or 20-ampere branch circuit
The GFCI shall be permitted to be an integral part of the attachment plug or located in the power-supply cord within 300 mm (12 in.) of the attachment plug. Listed cord sets incorporating GFCI for personnel shall be permitted.
Related Code Sections
(A) Special Occupancies, Where GFCI Protection Is Required
In addition to the requirements of 210.8(B), GFCI protection for personnel shall be provided for the following: All 125-volt, single-phase, 15 ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 525 Carnivals, Circuses, Fairs, and Similar Events > 525.23 Ground-Fault Circuit-Interrupter (GFCI) Protection > (A) Where GFCI Protection Is Required
(F) Special Occupancies, GFCI Protection
Ground-fault circuit-interrupter protection shall be provided as required in 210.8(B). GFCI protection shall not be required for other than 125-volt ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 551 Recreational Vehicles and Recreational Vehicle Parks > 551.71 Type Receptacles Provided > (F) GFCI Protection
(5) Equipment for General Use, GFCI Protection
In addition to the requirements in 210.8, branch circuits supplying the heating panel or heating panel sets shall have ground-fault circuit ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 424 Fixed Electric Space-Heating Equipment > 424.99 Installation Under Floor Covering > (B) Installation > (5) GFCI Protection
(C) Special Equipment, GFCI Protection
with Class A ground-fault circuit-interrupter protection. Exception: Listed low-voltage motors not requiring grounding, with ratings not exceeding ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.21 Motors > (C) GFCI Protection