// CODE SNIPPET
802.1 Wheelchair Spaces
Go To Full Code Chapter
802.1.1 Floor or Ground Surface
Where a wheelchair space can be entered from the front or rear, the wheelchair space shall be 48 inches (1220 mm) deep minimum. Where a wheelchair space can be entered only from the side, the wheelchair space shall be 60 inches (1525 mm) deep minimum.
Wheelchair spaces shall adjoin accessible routes. Accessible routes shall not overlap wheelchair spaces.
Wheelchair spaces shall not overlap circulation paths.
Advisory 802.1.5 Overlap. The term "circulation paths" used in Section 802.1.5 means aisle width required by applicable building or life safety codes for the specific assembly occupancy. Where the circulation path provided is wider than the required aisle width, the wheelchair space may intrude into that portion of the circulation path that is provided in excess of the required aisle width.
Related Code Sections
206.7.2 Scoping Requirements, Wheelchair Spaces
Platform lifts shall be permitted to provide an accessible route to comply with the wheelchair space dispersion and line-of-sight requirements of 221 ...
221.2 Scoping Requirements, Wheelchair Spaces
Wheelchair spaces complying with 221.2 shall be provided in assembly areas with fixed seating ...
802.1 Special Rooms, Spaces, and Elements, Wheelchair Spaces
Wheelchair spaces shall comply with 802.1. The ...
1002.4 Recreation Facilities, Wheelchair Spaces in Amusement Rides
Wheelchair spaces in amusement rides shall comply with 1002.4 ...
802.1.5 Special Rooms, Spaces, and Elements, Overlap
Wheelchair spaces shall not overlap circulation paths. Advisory 802.1.5 Overlap. The term "circulation paths" used in Section 802.1.5 means ...