// CODE SNIPPET
[F] 904.5 Wet-Chemical Systems
Related Code Sections
904.5 Fire Protection and Life Safety Systems, Wet-Chemical Systems
Wet-chemical extinguishing systems shall be installed, maintained, periodically inspected and tested in accordance with NFPA 17A and their listing ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 904 Alternative Automatic Fire-Extinguishing Systems > 904.5 Wet-Chemical Systems
803.2.4 Alterations—Level 2, Supervision
dioxide extinguishing systems. Dry- and wet-chemical extinguishing systems. Automatic sprinkler systems installed in accordance with NFPA 13R where ...
Existing Building Code 2018 of Illinois > 8 Alterations—Level 2 > 803 Fire Protection > 803.2 Automatic Sprinkler Systems > 803.2.4 Supervision
(D) Wiring Methods and Materials, Indoor Wet Locations
In portions of dairy processing facilities, laundries, canneries, and other indoor wet locations, and in locations where walls are frequently washed ...
National Electrical Code 2017 of Illinois > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.6 Protection Against Corrosion and Deterioration > (D) Indoor Wet Locations
1009.4 Change of Occupancy, Chemical Wastes
, the waste shall be neutralized prior to entering the drainage system, or the piping shall be changed to a compatible material. Chemical waste shall ...
Existing Building Code 2018 of Illinois > 10 Change of Occupancy > 1009 Plumbing > 1009.4 Chemical Wastes
(D) Wiring Methods and Materials, Wet Locations
PVC conduit shall be permitted in portions of dairies, laundries, canneries, or other wet locations, and in locations where walls are frequently ...
National Electrical Code 2017 of Illinois > 3 Wiring Methods and Materials > 352 Rigid Polyvinyl Chloride Conduit: Type PVC > 352.10 Uses Permitted > (D) Wet Locations