// CODE SNIPPET
3311.4 Water Supply
JUMP TO FULL CODE CHAPTER
Water supply for fire protection, either temporary or permanent, shall be made available as soon as combustible material accumulates.
Related Code Sections
11.1.5 Design Approaches, Water Supplies
The minimum water supply shall be available for the minimum duration specified in Chapter 11 ...
Standard for the Installation of Sprinkler Systems 2013 of Alabama > 11 Design Approaches > 11.1 General > 11.1.5 Water Supplies
220.127.116.11.1 Design Approaches, Water Supply
The water supply requirement for sprinklers only shall be calculated from the density/area curves of Figure 18.104.22.168.1 or from Chapter 22 where ...
Standard for the Installation of Sprinkler Systems 2013 of Alabama > 11 Design Approaches > 11.2 Occupancy Hazard Fire Control Approach for Spray Sprinklers > 11.2.3 Water Demand Requirements — Hydraulic Calculation Methods > 22.214.171.124 Density/Area Method > 126.96.36.199.1 Water Supply
18.3 Protection of Rubber Tire Storage, Water Supplies
Total water supplies shall be in accordance with the following options: A minimum of not less than 750 gpm (2835 L/min) for hose streams ...
Standard for the Installation of Sprinkler Systems 2013 of Alabama > 18 Protection of Rubber Tire Storage > 18.3 Water Supplies
188.8.131.52 Special Occupancy Requirements, Water Supplies
that the piping and water supply will supply the hose and automatic sprinkler demands simultaneously. [ 122: 6.2.3 ...
Standard for the Installation of Sprinkler Systems 2013 of Alabama > 22 Special Occupancy Requirements > 22.36 Metal/Nonmetal Mining and Metal Mineral Processing Facilities > 22.36.1 Design Requirements > 184.108.40.206 Water Supplies