// CODE SNIPPET
P-805.1 Water Service Protection
JUMP TO FULL CODE CHAPTER
When underground water service piping or water distribution piping and sewer or drain piping are laid in the same trench, the water service pipe or the water distribution pipe shall be laid on a bench or solidly tamped backfill at a level at least 12 inches above the top of the drainage pipe and at least 12 inches horizontally from the center line of the drainage pipe, and shall conform to Sections P-809 and P-904.4.
Related Code Sections
P-805.1 Water Supply and Distribution, Water Service Protection
When underground water service piping or water distribution piping and sewer or drain piping are laid in the same trench, the water service pipe ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-805 Underground Water Pipe > P-805.1 Water Service Protection
608.5 Water Supply and Distribution, Water Service Piping
Water service piping shall be protected in accordance with Sections 603.2 and 603.2.1 ...
Plumbing Code 2018 of Philadelphia > 6 Water Supply and Distribution > 608 Protection of Potable Water Supply > 608.5 Water Service Piping
507.1 Fire Service Features, Required Water Supply
An approved water supply capable of supplying the required fire flow for fire protection shall be provided to premises on which facilities ...
2018 Philadelphia Fire Code > 5 Fire Service Features > 507 Fire Protection Water Supplies > 507.1 Required Water Supply
507.5.6 Fire Service Features, Physical Protection
Where fire hydrants are subject to impact by a motor vehicle, guard posts or other approved means shall comply with Section 312 ...
2018 Philadelphia Fire Code > 5 Fire Service Features > 507 Fire Protection Water Supplies > 507.5 Fire Hydrant Systems > 507.5.6 Physical Protection